Question? Just ask us!
Free Encyclopedia of Building & Environmental Inspection, Testing, Diagnosis, Repair
InspectAPedia ® Home
INSULATION INSPECTION & IMPROVEMENT
ACOUSTICAL SEALANT CHOICES
AIR BYPASS LEAKS
AIR SEALING STRATEGIES\
CATHEDRAL CEILING INSULATION
DEW POINT CALCULATION for WALLS
FRAMING DETAILS for BETTER INSULATION
FREEZE-PROOF A BUILDING
GREENHOUSE DESIGN for SOLAR HEATING
HEAT LOSS in BUILDINGS
HEAT LOSS CALCULATIONS
HEAT LOSS DETECTION TOOLS
HEAT LOSS PREVENTION PRIORITIES
HUMIDITY LEVEL TARGET
Insulation Air & Heat Leaks
INSULATION for GREENHOUSE or SOLARIUM
INSULATION INSPECTION & IMPROVEMENT
INSULATION R-Values & Properties
LEED GREEN BUILDING CERTIFICATION
MOISTURE CONTROL in BUILDINGS
THERMAL MASS in buildings
VAPOR BARRIERS & CONDENSATION in buildings
VENTILATION in BUILDINGS
WALL CONSTRUCTION BARRIER vs CAVITY
WINTERIZE A BUILDING
This article describes how to ventilate a greenhouse used for solar heating, and how to connect the greenhouse to the house for effective heating. We discuss insulating the greenhouse against night time heat losses, and also we describe how to get warm air or heat from the greenhouse into the rest of the building. We give suggestions for ventilating greenhouses or sunspaces in hot summer weather, and we describe where to watch out for leaks in greenhouse or sunspace or solarium roofs & walls.
Green links show where you are. © Copyright 2013 InspectAPedia.com, All Rights Reserved.
The table of insulation properties at page top and accompanying text are reprinted/adapted/excerpted with permission from Solar Age Magazine - editor Steven Bliss. Readers should also see INSULATION R-Values & Properties for a more extensive table describing the properties of different insulating materials.
Readers should also see INSULATION for GREENHOUSE or SOLARIUM. Contact us to suggest text changes and additions and, if you wish, to receive online listing and credit for that contribution.
Question about how to best insulate a greenhouse (sunspace) against night time heat losses:
I plan to convert a carport to a greenhouse / dining room. The brick wall between the carport and the house contains a door to the kitchen and a window to the living room.
How should the greenhouse be ventilated and how should the greenhouse be connected to the house for effective solar heating? - Michael Moran, Clemson SC
Sunspace or Greenhouse Trombe Wall Retrofit Advice for Solar Heating
The brick wall between house and the new greenhouse has the makings of a Trombe wall, with one minor hitch - if it does not receive direct sunlight, its value as a thermal mass that absorbs, stores, and later returns heat is greatly reduced.
Cutting skylights into the carport roof would help the thermal mass wall work better by allowing sunlight to strike it directly.
Our photo (left) shows a large sunspace constructed atop a converted factory building in Poughkeepsie, NY.
Sunspace or Greenhouse Air Movement Advice for Solar Heat Design - Getting Warm Air into the Building
To get proper air circulation from the sunspace to the house you will need two vents - one high and one low.
The doorway and window should provide this ventilation, though a high vent can be added if required.
Since natural air convection is relatively week in a one-story building, a thermostatically controlled fan in the wall would give greater control and move even more heated air from the greenhouse sunspace into the rest of the house.
Another greenhouse solution combines awning windows along the front with operable skylights for roof vents. For accurate sizing for venting and heating of a sunspace, see "The Last Word in Sunspace Design," Solar Age 6/84, and also see INSULATION for GREENHOUSE or SOLARIUM.
Our greenhouse photo (left) was taken in the Barri Gotic in Barcelona, Spain.
Here we include solar energy, solar heating, solar hot water, and related building energy efficiency improvement articles reprinted/adapted/excerpted with permission from Solar Age Magazine - editor Steven Bliss.
As Carson Dunlop Associates point out in their sketch (left), greenhouses and solariums can be leaky, especially where an add-on solarium abuts the original structure.
Often we can spot these leaks as stains down the building wall below the points of contact between the solarium roof and the building walls.
Watch Out: a solarium or greenhouse leak that enters the wall cavity may not show up immediately as a stain on the building interior, but it can lead to rot, insect damage, or a mold problem
Original article in PDF form:
Frequently Asked Questions (FAQs)
No FAQs have been posted for this page. Try the search box below or CONTACT US by email if you cannot find the answer you need at InspectApedia.
Questions & answers or comments about trombe wall designs, solar heating, & greenhouses or sunspaces.
Ask a Question or Enter Search Terms in the InspectApedia search box just below.
Technical Reviewers & References
Related Topics, found near the top of this page suggest articles closely related to this one.