Question? Just ask us!
Free Encyclopedia of Building & Environmental Inspection, Testing, Diagnosis, Repair
InspectAPedia ® Home
VENTILATION in BUILDINGS
AIR BYPASS LEAKS
AIR LEAK DETECTION TOOLS
AIR LEAK SEALING PROCEDURE
AIR POLLUTANTS, COMMON INDOOR
AIR SEALING STRATEGIES
ATTIC LEAKS, CONDENSATION & MOLD
BASEMENT CEILING VAPOR BARRIER
BASEMENT HEAT LOSS
BASEMENT LEAKS, INSPECT FOR
BLOWER DOORS & AIR INFILTRATION
BRICK WALL DRAINAGE WEEP HOLES
CATHEDRAL CEILING VENTILATION
CEILINGS, DROP or SUSPENDED PANEL
COMBUSTION AIR for TIGHT buildings
COOLING LOAD REDUCTION by ROOF VENTS
CONDENSATION on WINDOWS & SKYLIGHTS
DEW POINT CALCULATION for WALLS
FIREPLACES & HEARTHS
FLAT ROOF MOISTURE & CONDENSATION
GREEN BUILDING CONSTRUCTION
HEAT LOSS in BUILDINGS
HEAT LOSS DETECTION TOOLS
HOT ROOF DESIGNS: Un-Vented Roof Solutions
HOUSEWRAP AIR & VAPOR BARRIERS
HOUSE DOCTOR, how-to be
HUMIDITY LEVEL TARGET
ICE DAM PREVENTION
INDOOR AIR HAZARDS TABLE
INDOOR AIR QUALITY & HOUSE TIGHTNESS
INDOOR AIR QUALITY IMPROVEMENT GUIDE
INSULATION CHOICES & PROPERTIES
Insulation Air & Heat Leaks
INSULATION INSPECTION & IMPROVEMENT
INSULATION R-Values & Properties
LOG HOME GUIDE
MOISTURE CONTROL in BUILDINGS
ODORS GASES SMELLS, DIAGNOSIS & CURE
ROOF VENTILATION SPECIFICATIONS
SHEATHING, FOIL FACED - VENTS
STAIN DIAGNOSIS on BUILDING INTERIORS
STUCCO WALL METHODS & INSTALLATION
SWEATING (CONDENSATION) on PIPES, TANKS
THERMAL MASS in buildings
THERMAL TRACKING Indicates Heat Loss
VAPOR BARRIERS & AIR SEALING at BAND JOISTS
VAPOR BARRIERS & HOUSEWRAP
VAPOR CONDENSATION & BUILDING SHEATHING
VENTILATION in BUILDINGS
WIND WASHING INSULATION At EAVES
WINDOWS & DOORS
This article discusses saving energy by roof framing options and construction details that permit optimum roof ventilation to also conserve energy, reducing cooling & heating costs. Sketch at page top and accompanying text are reprinted/adapted/excerpted with permission from Solar Age Magazine - editor Steven Bliss.
Green links show where you are. © Copyright 2014 InspectApedia.com, All Rights Reserved.
This roof ventilation design details article from Steven Bliss's "Building it Right" column in Solar Age Magazine and available in the three links just above, describes a few adjustments for insulated roofs that will assure good ventilation without wasting building heating or cooling energy.
The author explains the basics of ice dams and ice dam leaks on buildings, the need for a 1- to 2-inch air space over the outer wall top plate, and the importance of continuing the air ventilation pathway up under the roof to the ridge outlet. At the same time, good roof ventilation design prevents leaks from wind, rain, insects, and rodents.
Good attic or under-roof ventilation and insulation design is described for truss roofs as well as framing tips to save time and construction costs. The "raised-heel" or Arkansas truss design is explained - a method for obtaining additional insulation over the top plate for buildings constructed in cold climates.
For cathedral ceilings the author recommends flat trusses to provide adequate ceiling depth to permit both good insulation and good air ventilation in the structure.
Use Roof Vents and Roof Eaves Baffles to Assure Air Inflow for Roof Ventilation
The writer explains the use of vertical blocking or baffles to provide airflow passage between each pair of rafters or roof trusses. Where blown-in insulation is to be installed, the baffles need to continue all of the way up to the ridge outlet vent. Baffles may be site constructed using hardboard or manufactured rigid roof baffle products. Raised heel or flat truss design roofs include a vertical baffle flush with the side wall sheathing, or building wall sheathing can be continued vertically to form the baffle.
Additional Roof Venting & Gutter Details to Prevent Leaks and Rot at Roof Eaves
The writer, an advocate of the fully-vented cold-roof building design (to prevent ice dams, attic or roof condensation, and related rot or mold problems as well as providing a cooler building in hot weather) reviews gutter hanging details to assure that leaks do not occur at the vented roof eaves such as using strap hangers to keep gutters away from the fascia board, and placing the gutters low enough in snow-regions that the gutters won't be knocked off of the building by sliding snow and ice.
Options to provide intake venting at the overhang or soffit at the roof eaves include locating a continuous vent strip at the outermost edge of the overhang to minimize wind-blown rain entering the soffit from below.
The author cites model building codes on the amount of net free roof vent area in the attic: 1/300 of the ceiling area if the ceiling has a vapor barrier, and 1/150 of the ceiling area if no vapor barrier is installed.
We agree with the article's conclusion that these code specifications were written long ago when houses were more drafty, and when the prime concern was winter condensation risks.
Because of the increased use of air conditioning in buildings even in northern climates, summer energy costs have become a concern also suggesting that more ventilation than these minimums is recommended today.
Finally, if a whole house fan is to be installed blowing into the roof space or attic, still larger ventilation areas will be needed for the fan to work effectively (and to avoid a fire risk).
"Detailing for Roof Ventilation, the insulated roof requires a few adjustments in detailing - all the changes for the better" - links to the original article in PDF form immediately below are preceded by an expanded/updated online version of this article.
Here we include solar energy, solar heating, solar hot water, and related building energy efficiency improvement articles reprinted/adapted/excerpted with permission from Solar Age Magazine - editor Steven Bliss.
Green link shows where you are in this article series.
Frequently Asked Questions (FAQs)
No FAQs have been posted for this page. Try the search box below or CONTACT US by email if you cannot find the answer you need at InspectApedia.
Try the search box just below or if you prefer, post a question or a comment in the Comments box below and we will respond promptly.
Search the InspectApedia website
HTML Comment Box is loading comments...
Technical Reviewers & References
Related Topics, found near the top of this page suggest articles closely related to this one.