Question? Just ask us!
Free Encyclopedia of Building & Environmental Inspection, Testing, Diagnosis, Repair
InspectAPedia ® Home
ENVIRONMENTAL HAZARDS - INSPECT, TEST, REMEDY
AIR CLEANER PURIFIER TYPES
AIR FILTER EFFICIENCY
AIR FILTERS for HVAC SYSTEMS
AIR HANDLER / BLOWER UNITS
AIR LEAK DETECTION TOOLS
AIR LEAK SEALING PROCEDURE
AIR POLLUTANTS, COMMON INDOOR
AIR QUALITY IMPROVEMENT STRATEGIES
AIR SEALING STRATEGIES
ALLERGEN TESTS for BUILDINGS
ALLERGY TESTS for PEOPLE
ANIMAL ALLERGENS / PET DANDER
ANIMAL or URINE ODOR SOURCE DETECTION
ASBESTOS-FREE INSULATION MATERIALS
ASBESTOS IDENTIFICATION IN BUILDINGS
ATTORNEYS and EXPERT WITNESSES
BIBLIOGAPHY ENVIRONMENTAL HEALTH, MOLD, IAQ
BLOWER DOORS & AIR INFILTRATION
BLOWER FAN OPERATION & TESTING
BOOKSTORE - ENVIRONMENTAL
CAR MOLD CONTAMINATION
CARPET DUST IDENTIFICATION
CARPET MOLD CONTAMINATION
CARPETING & INDOOR AIR QUALITY
CAT DANDER in BUILDINGS
CHIMNEY INSPECTION DIAGNOSIS REPAIR
COMBUSTION GASES & PARTICLE HAZARDS
CONDENSATION or SWEATING PIPES, TANKS
CPSC Indoor Air Pollution Book Online Copy
DUCT SYSTEM & DUCT DEFECTS
EMF RF FIELD & FREQUENCY DEFINITIONS
EMERGENCY RESPONSE, IAQ, GAS, MOLD
EMF ELECTROMAGNETIC FIELDS & HUMAN EXPOSURE
FIBERBOARD INSULATION SHEATHING MOLD
FIBERGLASS DUCT, RIGID CONSTRUCTION
FIBERGLASS INSULATION IDENTIFICATION
FIREPLACES & WOODSTOVES CONTAMINANTS
FLOOD DAMAGE ASSESSMENT, SAFETY & CLEANUP
FLOODS in BUILDINGS, MOLD PREVENTION
FLOORING MATERIALS, Age, Types
FORMALDEHYDE GAS HAZARD REDUCTION
GAS DETECTION INSTRUMENTS
GAS EXPOSURE EFFECTS, TOXIC
HOME HEATING SAFETY
HUMIDITY CONTROL & TARGETS INDOORS
HOUSE DUST ANALYSIS
HOUSE DUST COMPONENTS
INDOOR AIR QUALITY & HOUSE TIGHTNESS
INDOOR AIR QUALITY IMPROVEMENT GUIDE
ASBESTOS INSULATION on PIPES
INSULATION AIR & HEAT LEAKS
INSULATION FACT SHEET- DOE
INSULATION IDENTIFICATION GUIDE
INSULATION INSPECTION & IMPROVEMENT
INSULATION MOLD TEST
INSULATION MOLD RESISTANCE of FOAM
INSULATION, UFFI UREA FORMALDEHYDE FOAM
LIGHT, GUIDE to FORENSIC USE
LEED Building Designation & IAQ
MILDEW REMOVAL & PREVENTION
MOISTURE CONTROL in BUILDINGS
MOLD ACTION GUIDE - WHAT TO DO ABOUT MOLD
MOLD APPEARANCE - WHAT MOLD LOOKS LIKE
MOLD APPEARANCE - STUFF THAT IS NOT MOLD
MOLD CLEANUP GUIDE- HOW TO GET RID OF MOLD
MOLD or INDOOR AIR EMERGENCY RESPONSE
MOLD / ENVIRONMENTAL EXPERT, HIRE ?
MOLD GROWTH on SURFACES, TABLE OF
MOLD GROWTH in/on BUILDING INSULATION
MOLD TESTING METHOD VALIDITY
MOLD TESTING SERVICES
MSDS MATERIAL SAFETY DATA SHEETS
MVOCs & MOLDY MUSTY ODORS
MYCOPHOBIA, STAINS MISTAKEN for MOLD
MYCOTOXIN EFFECTS of MOLD EXPOSURE
Museum Artifact Preservation
NOISE / SOUND DIAGNOSIS & CURE
ODORS GASES SMELLS, DIAGNOSIS & CURE
OIL TANKS INSPECT LEAK TEST ABANDON REGS
OZONE MOLD / ODOR TREATMENT WARNINGS
PARTICLE SIZES & IAQ
Particulates & Allergens Indoors
RADON HAZARD TESTS & MITIGATION
SAFETY HAZARDS GUIDE
SICK HOUSE IAQ QUESTIONNAIRE
SMELL PATCH TEST to FIND ODOR SOURCE
SOUND CONTROL in BUILDINGS
STAIN DIAGNOSIS on BUILDING EXTERIORS
STAIN DIAGNOSIS on BUILDING INTERIORS
THERMAL TRACKING & HEAT LOSS
UFFI UREA FORMALDEHYDE FOAM INSULATION
URETHANE FOAM Deterioration, Outgassing
VAPOR BARRIERS & AIR SEALING at BAND JOISTS
VAPOR BARRIERS & CONDENSATION in BUILDINGS
VAPOR BARRIERS & HOUSEWRAP
VAPOR CONDENSATION & BUILDING SHEATHING
VENTILATION in BUILDINGS
VINYL SIDING or WINDOW PLASTIC ODORS
VOCs VOLATILE ORGANIC COMPOUNDS
WATER ODORS, CAUSE CURE
WATER TESTS, CONTAMINANTS, TREATMENT
WORLD TRADE CENTER 9-11 DUST PHOTOS
Fiberglass insulation mold contamination test details:
This document discusses choices of test methods to screen for toxic or allergenic mold contamination in fiberglass building insulation in residential and light-commercial buildings.
Mold is often found in basement fiberglass insulation, crawl space fiberglass insulation, fiberglass wall insulation, heating or cooling duct fiberglass insulation, and attic or roof insulation in buildings which have either been wet or have been exposed to high levels of mold from other sources.
Green links show where you are. © Copyright 2015 InspectApedia.com, All Rights Reserved.
This article explains how to find or test for moldy insulation in buildings, the probable cause of mold contamination in building insulation, and how to recognize conditions that make that problem likely in a particular case.
Our page top photo shows a Burkard personal air sampler that with clever manipulation can be used to test fiberglass building insulation for contaminating particles including mold, insect fragments, pollen, or other debris.
This website discusses health hazards associated with moldy fiberglass in buildings, with focus on fiberglass insulation, fiberglass fragments, fiberglass in heating and air conditioning duct work, and invisible but toxic mold growth in fiberglass which has been wet, exposed to high humidity, or exposed to other moldy conditions.
Watch out: Our photo of clean-looking insulation in a basement ceiling (at below left left) does not provide evidence that insulation testing was necessary for that building.
But a case history of occupant complaints, a wet basement, and previous storage of moldy materials in the basement that had been removed at the time of our inspection led us to test and confirm that this insulation was severely contaminated with Penicillium sp. mold.
Reader Question: How should we sample fiberglass insulation for mold when investigating a building?
I believe that there is mold that is not visible to the eye, but how do you confirm that it is there? Send a piece of the insulation to a lab for analysis? I’m a mold inspector in Minneapolis, Minnesota and we have a lot of damp insulation in basements here.
Sometimes I see spots on the insulation and know that there is obvious mold, but I have long suspected (based on smell and moisture readings) that some mold might not be visible to the eye. Is it just that it is in early growth stage so the colonies are too small to see?
And again, how do you verify that this is the case – by samples submitted to the lab? I was on the site searching for information on mold in insulated ducts. - Vickie Swenson, CRMI Minnesota Mold Inspection (612) 508-2742
Answer: Detailed Description of Methods for Testing Building Insulation for Mold
You are quite right that it can be impossible to see mold in some materials including fiberglass insulation. Sometimes fiberglass looks very very clean to the naked eye, but is chock full of Aspergillus or Penicillium.
There are several similar ways to test insulation that does not already give visual evidence of a mold problem.
We use an air sampling cassette such as an Air-o-Cel or Allergenco unit with a vacuum pump set to move air at the proper flow rate for the cassette (typically 10 lpm). The sampler is held 1-4 inches away from the insulation and then with the pump running we poke or agitate the suspect insulation to stir a particle release.
The sample interval needs to be short - often just 5-20 seconds in duration since otherwise you risk overloading the cassette with fiberglass particles.
At ACCURACY OF VARIOUS MOLD TEST METHODS we include photos of particle traces on microscope slides that can help you recognize when a dust sample is overloaded and thus hard to analyze in the lab.
Our photo (above left) shows a more complicated version of this test about to start. In this case we were using two air sampling pumps and two different brands of sampling cassettes in order to compare their behavior during dust sampling. In the foreground you can just make out a special timer-switch that we used to turn on and off both pumps simultaneously.
If you are in doubt or inexperienced, try making three sample cassettes of 5, 10, and 20 second durations, agitating the insulation about the same degree in each case and keeping about the same distance.
The time and distance are not critical as long as we make clear that this is a qualitative test for the presence or absence of high levels of mold or other particles in the insulation, not a quantitative test.
A second method for testing fiberglass insulation that we have used with good results was to run a Burkard personal air sampler with a prepared collection slide mounted in the device for a 15-second interval, holding the sampler one to six inches away from the insulation during agitation of the insulation itself.
You can simply use a pencil to poke the insulation during sampling. As with the air sampling cassette approach above, make several test samples at different sampling durations to be sure you have a good sample that is not overloaded.
Alternative, low-cost Air Pumps for Building Insulation Mold Testing
While we prefer using a calibrated instrument for pulling particles from building insulation to screen for mold contamination, considering that a reasonable mold contamination test is qualitative and that precise mold counts are inappropriate (and would be misleading), as long as your air pump or vacuum device produces a flow-rate within the operating range of your sampling cassette or slide, you can use less costly devices such as the keyboard vacuum pump shown here.
Watch out: the airflow rate of portable battery operated pumps such as shown here varies widely from device to device as well as depending on battery condition.
For field use in testing insulation, we tested ten low-cost portable pumps in our forensic laboratory, selecting a subset that consistently delivered 10-15 LPM with fresh batteries .
In the laboratory, if we receive a bulk sample of suspect insulation, in addition to inspecting the insulation itself in the stereo microscope and high power transmitted light forensic microscope, we sometimes use a third sampling method that is most suitable for a variety of suspect, perhaps dirty and loose materials.
We construct a test chamber using a cardboard box lined with a new clean plastic garbage bag.
The bag lines the box, the sample is placed into the box, the box is sealed. We cut an opening sufficient to admit or affix our air sampling cassette, then we agitate the box for 30 seconds before pulling a vacuum sample from the box itself.
This method also can reduce overloading the sample with fiberglass particles.
It is possible to perform quantitative analysis of insulation or other fibrous materials or dust samples for mold contamination using a wash and filter method that collects most particles from the insulation sample into a liquid for further processing and particle counting.
We do not agree that the apparent accuracy of this method is real, and we suspect that except for controlled technical studies it is not appropriate.
Therefore a quantitative analysis of mold spores per cubic inch, meter or other volume of fiberglass insulation may be very precise (lots of decimal places) but inaccurate as an estimator of size of the problem mold reservoir.
Should All Building Insulation be Tested for Mold?
We do not recommend testing all insulation for mold. The decision to test insulation for mold needs to be made based on a careful building inspection and case history, including visual evidence of leaks or the presence of exposed fiberglass over an area known to be or have been subject to a large mold contamination problem or a mold remediation project.
See Attic Moisture or Mold Sources for a discussion of common sources of moisture in attics that can cause moldy insulation, and similarly,
see BASEMENT LEAKS, INSPECT FOR for the same problem in basements.
Readers ducting cool air through a crawl space should also see CRAWLSPACE MOLD ADVICE.
Continue reading at TEST PROCEDURE for MOLD in FIBERGLASS about just how fiberglass mold tests are conducted in the field or select a topic from the More Reading links shown below.
Suggested citation for this web page
Green link shows where you are in this article series.
Frequently Asked Questions (FAQs)
No FAQs have been posted for this page. Try the search box below or CONTACT US by email if you cannot find the answer you need at InspectApedia.
Questions & answers or comments about methods for testing for the presence of mold contaminants in fiberglass or other building insulation products.
Use the "Click to Show or Hide FAQs" link just above to see recently-posted questions, comments, replies, try the search box just below, or if you prefer, post a question or comment in the Comments box below and we will respond promptly.
Search the InspectApedia website
HTML Comment Box is loading comments...
Technical Reviewers & References
Fiberglass in buildings: hazards, testing, cleanup, prevention: references & products
For more information about fiberglass as an indoor air quality concern see: