Question? Just ask us!
Free Encyclopedia of Building & Environmental Inspection, Testing, Diagnosis, Repair
InspectAPedia ® Home
SOLAR ENERGY SYSTEMS
AIR CONDITIONING & HEAT PUMP SYSTEMS
AIR LEAK MINIMIZATION
AIR LEAK SEALING PROCEDURE
AIR SEALING STRATEGIES
BIOGAS PRODUCTION & USE
EVAPORATIVE COOLING SYSTEMS
FLOOR FRAMING & SUBFLOOR for TILE
FLOOR POURED FINISH ON CONCRETE SLABS
FLOOR RADIANT HEAT Mistakes to Avoid
FLOOR TYPES & DEFECTS
FRAMING DETAILS for BETTER INSULATION
FRAMING DETAILS for DOUBLE WALL HOUSES
FRAMING METAL STUD PERFORMANCE
FREEZE-PROOF A BUILDING
FROST HEAVES, FOUNDATION, SLAB
GREEN BUILDING CONSTRUCTION CODES GUIDES
GREENHOUSE DESIGN for SOLAR HEATING
GREENHOUSE / SUNSPACE GLARE
HEAT LOSS in BUILDINGS
HEAT LOSS DETECTION TOOLS
HEAT LOSS INDICATORS
HEAT LOSS PREVENTION PRIORITIES
HEAT LOSS R U & K VALUE CALCULATION
HEAT LOSS RATE CALCULATIONS
HEATING SMALL LOADS
HOUSEWRAP INSTALLATION DETAILS
HUMIDITY LEVEL TARGET
INSULATION IDENTIFICATION GUIDE
INSULATION LOCATION - WHERE TO PUT IT
LEED GREEN BUILDING CERTIFICATION
LEED Building Designation & IAQ
MOISTURE CONTROL in BUILDINGS
NOISE / SOUND DIAGNOSIS & CURE
ODORS GASES SMELLS, DIAGNOSIS & CURE
PLUMBING SYSTEM INSPECT DIAGNOSE REPAIR
RADIANT SLAB FLOORING CHOICES
RADIANT SLAB TUBING & FLUID CHOICES
ROOFING INSPECTION & REPAIR
ROOF VENTILATION SPECIFICATIONS
ROOF ICE DAM LEAKS
SHEATHING, FOIL FACED - VENTS
STRUCTURAL INSPECTIONS & DEFECTS
SUMP PUMPS GUIDE
SWEATING (CONDENSATION) on PIPES, TANKS
Thermal Expansion Cracking of Brick
THERMAL EXPANSION of HOT WATER
THERMAL EXPANSION of MATERIALS
THERMAL IMAGING, THERMOGRAPHY
THERMAL IMAGING MOLD SCANS
THERMAL MASS in BUILDINGS
THERMAL TRACKING & HEAT LOSS
VAPOR BARRIERS & AIR SEALING at BAND JOISTS
VAPOR BARRIERS & CONDENSATION in BUILDINGS
VAPOR BARRIERS & HOUSEWRAP
VAPOR CONDENSATION & BUILDING SHEATHING
VENTILATION in BUILDINGS
WATER SOFTENERS & CONDITIONERS
WIND ENERGY SYSTEMS
WIND TURBINES & LIGHTNING
WINDOWS & DOORS
WINTERIZE A BUILDING
WOOD Burning Heaters Fireplaces Stoves
This article discusses the Five Key Elements of Passive Solar Design and links to additional passive solar design as well as solar design evaluation questions and answers.
Green links show where you are. © Copyright 2014 InspectApedia.com, All Rights Reserved.
Our page top photo shows windows admitting morning solar gain in a nearly-balanced-energy passive solar home in San Miguel de Allende, Guanajuato, Mexico. The windows in this east-facing room receive morning sunlight (when the home and air are cool, and is shaded in the afternoon. This is a direct gain of passive solar energy. The concrete and adobe walls form a significant thermal mass. Although the building has no central heating, temperatures remain comfortable year round, with only modest use of a small electric heater during the chilly months of December and January.
The U.S. DOE illustration (left) identifies the five elements of passive solar design:
The following five elements constitute a complete passive solar home design. Each performs a separate function, but all five must work together for the design to be successful. -- U.S. Department of Energy
The large glass (window) area through which sunlight enters the building. Typically, the aperture(s) should face within 30 degrees of true south and should not be shaded by other buildings or trees from 9 a.m. to 3 p.m. each day during the heating season. For a low-cost passive solar home using lots of glass see PASSIVE SOLAR HOME, LOW COST.
The hard, darkened surface of the storage element. This surface—which could be that of a masonry wall, floor, or partition (phase change material), or that of a water container—sits in the direct path of sunlight. Sunlight hits the surface and is absorbed as heat. For an example see our articles at THERMAL MASS in buildings and see PASSIVE SOLAR FLOOR TILES, PHASE CHANGE.
The materials that retain or store the heat produced by sunlight. The difference between the absorber and thermal mass, although they often form the same wall or floor, is that the absorber is an exposed surface whereas thermal mass is the material below or behind that surface. For an example, see BLOCKBED RADIANT FLOORS - SOLAR DESIGN. Also see SLAB INSULATION, PASSIVE SOLAR. Also see Trombe Wall.
The method by which solar heat circulates from the collection and storage points to different areas of the house. A strictly passive design will use the three natural heat transfer modes — conduction, convection, and radiation—exclusively. In some applications, however, fans, ducts, and blowers may help with the distribution of heat through the house. See BLOCKBED RADIANT FLOORS - SOLAR DESIGN.
Roof overhangs can be used to shade the aperture area during summer months. Other elements that control under- and/or overheating include electronic sensing devices, such as a differential thermostat that signals a fan to turn on; operable vents and dampers that allow or restrict heat flow; low-emissivity blinds ; and awnings. For examples see SOLAR SHADES & SUNSCREENS and SUNGAIN, FILMS, LOW-E GLASS.
To understand how a passive solar home design works, you need to understand how heat moves and how it can be stored. (Photo at left, U.S. DOE, & Donald Aitken)
As a fundamental law, heat moves from warmer materials to cooler ones until there is no longer a temperature difference between the two. To distribute heat throughout the living space, a passive solar home design makes use of this law through the following heat-movement and heat-storage mechanisms:
Direct gain is the simplest passive solar home design technique. Sunlight enters the house through the aperture (collector)—usually south-facing windows with a glazing material made of transparent or translucent glass. The sunlight then strikes masonry floors and/or walls, which absorb and store the solar heat. The surfaces of these masonry floors and walls are typically a dark color because dark colors usually absorb more heat than light colors. At night, as the room cools, the heat stored in the thermal mass convects and radiates into the room.
[Another example of direct solar gain is at our page top photo.- DF]
Some builders and homeowners have used water-filled containers located inside the living space to absorb and store solar heat. Water stores twice as much heat as masonry materials per cubic foot of volume. Unlike masonry, water doesn't support itself. Water thermal storage, therefore, requires carefully designed structural support. Also, water tanks require some minimal maintenance, including periodic (yearly) water treatment to prevent microbial growth.
The amount of passive solar (sometimes called the passive solar fraction) depends on the area of glazing and the amount of thermal mass. The glazing area determines how much solar heat can be collected. And the amount of thermal mass determines how much of that heat can be stored. It is possible to undersize the thermal mass, which results in the house overheating. There is a diminishing return on over sizing thermal mass, but excess mass will not hurt the performance. The ideal ratio of thermal mass to glazing varies by climate.
[Our photo (left) shows a small area designed by D. Friedman & J. Church for both direct solar gain and a brick on concrete floor providing thermal mass at a home in Poughkeepsie, NY - DF]
Another important thing to remember is that the thermal mass must be insulated from the outside temperature. If the thermal mass is not insulated, the collected solar heat can drain away rapidly. Loss of heat is especially likely when the thermal mass is directly connected to the ground or is in contact with outside air at a lower temperature than the desired temperature of the mass.
Even if you simply have a conventional home with south-facing windows without thermal mass, you probably still have some passive solar heating potential (this is often called solar-tempering). To use it to your best advantage, keep windows clean and install window treatments that enhance passive solar heating, reduce nighttime heat loss, and prevent summer overheating.
An indirect-gain passive solar home has its thermal storage between the south-facing windows and the living spaces.
Illustration of a Trombe wall (left) U.S. DOE.
Using a Trombe wall is the most common indirect-gain approach. The wall consists of an 8–16 inch-thick masonry wall on the south side of a house. A single or double layer of glass is mounted about 1 inch or less in front of the wall's surface. Solar heat is absorbed by the wall's dark-colored outside surface and stored in the wall's mass, where it radiates into the living space.
The Trombe wall distributes or releases heat into the home over a period of several hours. Solar heat migrates through the wall, reaching its rear surface in the late afternoon or early evening. When the indoor temperature falls below that of the wall's surface, heat begins to radiate and transfer into the room. For example, heat travels through a masonry wall at an average rate of 1 hour per inch. Therefore, the heat absorbed on the outside of an 8-inch-thick concrete wall at noon will enter the interior living space around 8 p.m.
The most common isolated-gain passive solar home design is a sunspace. A sunspace—also known as a solar room or solarium—can be built as part of a new home or as an addition to an existing one.
The simplest and most reliable sunspace design is to install vertical windows with no overhead glazing. Sunspaces may experience high heat gain and high heat loss through their abundance of glazing. The temperature variations caused by the heat losses and gains can be moderated by thermal mass and low-emissivity windows. For more information, see sunspace orientation and glazing angles.
The thermal masses that can be used include a masonry floor, a masonry wall bordering the house, or water containers. The distribution of heat to the house can be accomplished through ceiling and floor level vents, windows, doors, or fans. Most homeowners and builders also separate the sunspace from the home with doors and/or windows so that home comfort isn't overly affected by the sunspace's temperature variations. For more information, see [at U.S.DOE or below] sunspace heat distribution and control.
Sunspaces may often be called and look a lot like "greenhouses." However, a greenhouse is designed to grow plants while a sunspace is designed to provide heat and aesthetics to a home.
Many elements of a greenhouse design that are optimized for growing plants, such as overhead and sloped glazing, are counterproductive to an efficient sunspace.
Moisture-related mold and mildew, insects, and dust inherent to gardening in a greenhouse are not especially compatible with a comfortable and healthy living space. [See HUMIDITY LEVEL TARGET and see INDOOR AIR QUALITY IMPROVEMENT GUIDE -DF]
Also, it is difficult to shade sloped glass to avoid overheating, while vertical glass can be shaded by a properly sized overhang.
Photo-Example of A Sunspace for a Cold Climate
[Our photos (above and at left) show a sunspace constructed by the website author (D Friedman) & J Church, in Poughkeepsie, New York. This addition includes continuous operable awning-type windows around three sides of the structure (North, East, South). In order to maximize solar gain during winter months in this northern climate (Mid Hudson Valley, New York).
The roof was designed with only a minimal overhang. The West side of the addition is its point of attachment to the original building.
This sunspace was well insulated in its roof and lower walls below the windows, and the space can be opened to share air and heat with the rest of the building (lifting out a sliding glass door).
As this sunspace was built by modifying an existing screened porch, we did not construct a thermal-mass floor: the space was constructed over a crawl area, but the floor has been insulated below using two-inch solid-foam board insulation placed between the floor joists, immediately below the wood flooring. Even with heat turned off into this room, it reaches the high 50's, low 60's in cold winter months. Roof overhang design for passive solar homes is discussed below. -DF]
Passive Solar Home Design for Summer Comfort
It makes little sense to save money on winter heating just to spend it on summer cooling. So in most climates, a passive solar home design must provide summer comfort as well. The solar heat in the summer must be blocked by an overhang or other devices, such as awnings, shutters, and trellises.
The physical dimensions of an overhang are an important element because overheating will occur unless the overhang provides enough shade.
[The solar overhang shown in our photo (above-right) is located on a home in Mexico and is discussed in more detail at PASSIVE SOLAR HEAT PERFORMANCE. The addition of these small overhangs above windows on the East and West facing sides of this studio made the difference between having a comfortable space and having a space that was just too warm to occupy late in the afternoons. For a contrasting example, another home in the same area that has no roof overhangs to control solar gain is discussed at PASSIVE SOLAR HOME, LOW COST. -- DF]
Many variables—including latitude, climate, solar radiation transmittance, il luminance levels, and window size and type—need to be considered for properly sizing an overhang in a specific locale. Therefore, it's best to have an experienced solar designer or builder calculate the proper overhang dimensions. For more information, see roof overhangs [below] for shading building elements.
In passive solar home design, exterior roof overhangs provide a practical method for shading building elements such as windows, doors, and walls.
Overhangs are most effective for south facing elements (in the northern hemisphere) and at midday. If the building element bears more than about 30° off true south, the effectiveness of an overhang, as with any solar feature, begins to decrease significantly. Overhangs usually only affect the amount of direct solar radiation that strikes a surface. Diffuse sky and reflected radiation gains are not often directly affected by overhangs.
The higher overhead the sun is, the shorter the shadow a person will cast on the ground. However, the short brim of a baseball cap can create a long shadow across the body of a standing person. The same concept applies in designing overhangs for buildings.
The higher, or more vertical, the arc of the sun, the longer the shadow that the building overhang generates along the face of the wall. Summer shadows extend down walls the furthest, winter shadows the least. Sites closer to the equatorial path of the sun have deeper-extending wall shadows than ones farther from the equator, assuming the same overhang length.
Overhangs may be solid, louvered, vegetation-supporting, or a combination of all of these aspects. Some shutters, eaves, trellises, light shelves, and awnings serve the same purpose as an overhang.
Overhangs may also be fixed, operable, and/or removable. Examples include roof eaves, awnings, and Bahama shutters (top-hinged louvered shutters typically propped open with wooden dowels) respectively.
Fixed overhangs offer perceived longevity and low maintenance at the expense of flexibility or the ability to adjust to site-specific factors. Although adjustable devices allow the user to fine tune the amount of shade or direct sunlight, they require more maintenance. Removable fixtures generally provide flexibility and longevity plus some personal involvement with installation and removal.
Openings, such as windows, do not always require fixed overhangs. A fixed overhang designed for optimal shading on the autumnal equinox (September 21) casts the same shadow on the vernal equinox (March 21).
While northern-hemisphere shading may be welcome in September because of the heat, shading in March may be undesirable. Vegetation, on the other hand, can follow the climatic seasons. Vines that shed their leaves for winter usually leaf out about the time shading is needed. Movable shading devices, while adjustable, often become maintenance problems.
Unfortunately, there is as yet no universally simple formula for sizing overhangs. While one overhang methodology works well for some locations, it can be completely inappropriate for others.
For example, there are a limited number of overhang-sizing guidelines acceptable for buildings located in southern states, particularly hot-humid climates. Guidelines acceptable for the high plains of Montana are unlikely to work for a site in Florida.
Due to the varying microclimate conditions encountered across the United States, the methods presented here are general in scope. Anyone seeking a more specialized analysis should seek professional advice from an architect trained in passive solar design.
Every climate requires special design attention. The following general guidelines may be useful in determining a suitable overhang design. The guidelines are listed by climate type, for solar noon, when the sun reaches its maximum altitude for a given day. Solar noon is very rarely the same as noon in local standard time.
*(HDD and CDD data is available from local weather services.)
Overhangs may be inappropriate for sites with restrictive regulatory guidelines. For example, your calculations indicate your house needs a three foot (~1 meter[m]) overhang on the front. The local zoning ordinance restricts eave extension to two feet (0.61 m) beyond the front yard setback.
If your house will be or is located precisely on the setback, you must do one of the following:
List of Passive Solar Design Key Reference Books including Online Texts
The first three passive solar design handbook links below are to free, online documents.
Here we include solar energy, solar heating, solar hot water, and related building energy efficiency improvement articles reprinted/adapted/excerpted with permission from Solar Age Magazine - editor Steven Bliss.
Readers wanting more detail about passive solar design should see SOLAR ENERGY SYSTEMS. Readers concerned with accurate calculation of the "percent solar" and similar energy savings assessments should see PASSIVE SOLAR HEAT PERFORMANCE. Readers should also see SOLAR HOUSE EVALUATION. Contact us to suggest text changes and additions and, if you wish, to receive online listing and credit for that contribution.
Green link shows where you are in this article series.
Frequently Asked Questions (FAQs)
No FAQs have been posted for this page. Try the search box below or CONTACT US by email if you cannot find the answer you need at InspectApedia.
Solar design handbook questions and answers .
Check the FAQs just above, try the search box just below, or if you prefer, post a question or comment in the Comments box below and we will respond promptly.
Search the InspectApedia website
HTML Comment Box is loading comments...
Technical Reviewers & References
Related Topics, found near the top of this page suggest articles closely related to this one.