Question? Just ask us!
Free Encyclopedia of Building & Environmental Inspection, Testing, Diagnosis, Repair
InspectAPedia ® Home
AIR CONDITIONING & HEAT PUMP SYSTEMS
A/C - HEAT PUMP CONTROLS & SWITCHES
AIR CONDITIONER COMPONENT PARTS
AIR CONDITIONER TYPES, ENERGY SOURCES
AIR FILTER EFFICIENCY
AIR FILTERS, FIBERGLASS PARTICLES
AIR FLOW MEASUREMENT CFM
APPLIANCE EFFICIENCY RATINGS
BLOWER DOORS & AIR INFILTRATION
BLOWER FAN CONTINUOUS OPERATION
BLOWER FAN OPERATION & TESTING
BOOKSTORE - Air Conditioning "How To" Books
CAPACITORS for HARD STARTING MOTORS
CLEANING & Legionella BACTERIA
CHINESE DRYWALL HAZARDS
CONDENSATION or SWEATING PIPES, TANKS
DEFINITION of Heating & Cooling Terms
DEW POINT CALCULATION for WALLS
DEW POINT TABLE - CONDENSATION POINT GUIDE
DIAGNOSTIC GUIDES A/C / HEAT PUMP
DIAGNOSE & FIX HEATING PROBLEMS-BOILER
DIAGNOSE & FIX HEATING PROBLEMS-FURNACE
DUCTS - Asbestos
DUCT INSULATION, Asbestos Paper
DUCT INSULATION for SOUNDPROOFING
DUCT SYSTEM & DUCT DEFECTS
DUCT SYSTEM NOISES
DUCTS, Asbestos Transite Pipe
DUST, HVAC CONTAMINATION STUDY
ELECTRIC MOTOR OVERLOAD RESET SWITCH
EVAPORATIVE COOLING SYSTEMS
FAN LIMIT SWITCH
GAS EXPOSURE EFFECTS, TOXIC
GAS DETECTION INSTRUMENTS
HEAT LOSS (or GAIN) in buildings
HEAT LOSS (or GAIN) INDICATORS
HEAT LOSS R U & K VALUE CALCULATION
HEATING SMALL LOADS
INSPECTION CHECKLIST - OUTDOOR UNIT
INSPECTION LIMITATIONS, A/C SYSTEMS
LEED GREEN BUILDING CERTIFICATION
LOST COOLING CAPACITY
LOW VOLTAGE TRANSFORMER TEST
MOTOR OVERLOAD RESET SWITCH
MOLD in AIR HANDLERS & DUCT WORK
OPERATING COST, AIR CONDITIONER
OPERATING DEFECTS, AIR CONDITIONING
REPAIR GUIDES A/C / HEAT PUMP
REPAIR & DIAGNOSTIC FAQs for A/C
THERMOSTATS, HEATING / COOLING
THERMOSTATIC EXPANSION VALVES
WATER COOLED AIR CONDITIONERS
WINDOW / WALL AIR CONDITIONERS
WINDOW / WALL A/C SUPPORTS
Retrofit or add-on air conditioning specifications: this air conditioning repair article discusses the Sizing of Retrofit Conditioning Air Handlers: How to Add Air Conditioning to Hot Air Heating Systems. We describe the central air conditioner operating problems that occur if an add-on air conditioning component (to an existing hot air heating system) is not properly sized for the building or if it is not properly matched to the pre-existing blower or air handler system that was used for central heating. There may also be a need for an air handler blower fan capable of operating at different speeds for heating versus cooling. Contact us to suggest text changes and additions and, if you wish, to receive online listing and credit for that contribution.
Green links show where you are. © Copyright 2013 InspectAPedia.com, All Rights Reserved.
ADDING A/C: RETROFIT SIZING - Air Conditioning Retrofit Errors When Adding Air Conditioning to an Existing Hot Air Heating System: Improper Air Conditioning Cooling Coil Size
We discuss the air conditioning system sizing problem at AIR CONDITIONER BTU CHART and while details are found at DEHUMIDIFICATION PROBLEMS, we also introduce the oversized air conditioner problem at LOST COOLING CAPACITY. Also see COOLING RULES OF THUMB to guesstimate how many tons or BTUs of cooling a building needs and see RATED COOLING CAPACITY to determine the cooling capacity of existing air conditioning equipment.
The typical indoor half of an air conditioning system is comprised of a blower fan which moves building air (through return ducts) across an evaporator coil (which cools and dehumidifies the building air) and then through supply ducts to various building rooms. Liquid refrigerant is metered into the evaporator coil where it evaporates or changes state from a liquid to a gas.
This state change from liquid to gas absorbs heat and thus cools the evaporator coil. As air is cooled by moving across the evaporator coil, moisture is removed from the air (cool air holds less moisture than warm air). The condensate is moved to an acceptable disposal point, perhaps by a condensate pump to a building drain.
But a larger evaporator coil does not necessarily mean we'll see an equivalent improvement in the cooling capacity of the air conditioning system. In fact if the cooling coil is too large for the air handler or "blower unit" the air conditioning system will not work properly.
The photo shows that an evaporator coil has been added atop an existing heating furnace. Using the existing blower and duct work and simply adding an evaporator coil atop the unit is a common way to add air conditioning to an existing furnace and duct system, and such air conditioning retrofits can work quite well by taking advantage of an existing duct system and air handler.
But to work properly the evaporator coil (or cooling coil) should not be too large for the air movement capacity of the existing air handling system. Otherwise the air handler won't be able to move enough air across the evaporator coil to prevent freeze-ups and the net result may be less cooling capacity rather than more. In other words, when the new evaporator coil for an add-on air conditioning system is too large, the blower will not move enough air across the coil, probably leading to the evaporator coil becoming blocked by ice.
Similarly, the air movement capability of the blower assembly, including the speed of the fan of an existing furnace needs to be matched to the evaporator coil's needs. The speed of air flow through ductwork and its delivery into a building are different for heating than for cooling a building. Some contemporary combination units which provide both heating and cooling air to a building make use of a dual speed or variable speed fan.
If when inspecting a "retrofit" air conditioning system (like the one in this photograph) you see that the evaporator coil is much larger than the furnace blower atop which it sits, the system is probably not properly designed and it may not work correctly. An expert air conditioning service technician or design specialist should evaluate the system when you see this condition.
Frequently Asked Questions (FAQs)
No FAQs have been posted for this page. Try the search box below or CONTACT US by email if you cannot find the answer you need at InspectApedia.
Questions & answers or comments about how to properly size & install retrofit or add-on air conditioning to an existing warm air furnace.
Ask a Question or Enter Search Terms in the InspectApedia search box just below.
Technical Reviewers & References
Related Topics, found near the top of this page suggest articles closely related to this one.