Question? Just ask us!
Free Encyclopedia of Building & Environmental Inspection, Testing, Diagnosis, Repair
InspectAPedia ® Home
AIR CONDITIONING & HEAT PUMP SYSTEMS
A/C - HEAT PUMP CONTROLS & SWITCHES
AIR CONDITIONER COMPONENT PARTS
AIR CONDITIONER TYPES, ENERGY SOURCES
AIR FILTER EFFICIENCY
AIR FILTERS, FIBERGLASS PARTICLES
AIR FLOW MEASUREMENT CFM
APPLIANCE EFFICIENCY RATINGS
BLOWER DOORS & AIR INFILTRATION
BLOWER FAN CONTINUOUS OPERATION
BLOWER FAN OPERATION & TESTING
BOOKSTORE - Air Conditioning "How To" Books
CAPACITORS for HARD STARTING MOTORS
CLEANING & Legionella BACTERIA
CHINESE DRYWALL HAZARDS
CONDENSATION or SWEATING PIPES, TANKS
DEFINITION of Heating & Cooling Terms
DEW POINT CALCULATION for WALLS
DEW POINT TABLE - CONDENSATION POINT GUIDE
DIAGNOSE & FIX AIR CONDITIONER / HEAT PUMP
DIAGNOSE & FIX HEATING PROBLEMS-BOILER
DIAGNOSE & FIX HEATING PROBLEMS-FURNACE
DUCTS - Asbestos
DUCT INSULATION, Asbestos Paper
DUCT INSULATION for SOUNDPROOFING
DUCT SYSTEM NOISES
DUCTS, Asbestos Transite Pipe
DUST, HVAC CONTAMINATION STUDY
ELECTRIC MOTOR OVERLOAD RESET SWITCH
EVAPORATIVE COOLING SYSTEMS
FAN LIMIT SWITCH
GAS EXPOSURE EFFECTS, TOXIC
GAS DETECTION INSTRUMENTS
HEAT LOSS (or GAIN) in buildings
HEAT LOSS (or GAIN) INDICATORS
HEAT LOSS R U & K VALUE CALCULATION
HEATING SMALL LOADS
INSPECTION CHECKLIST - OUTDOOR UNIT
INSPECTION LIMITATIONS, A/C SYSTEMS
LEED GREEN BUILDING CERTIFICATION
LOST COOLING CAPACITY
LOW VOLTAGE TRANSFORMER TEST
MOTOR OVERLOAD RESET SWITCH
MOLD in AIR HANDLERS & DUCT WORK
OPERATING COST, AIR CONDITIONER
OPERATING DEFECTS, AIR CONDITIONING
REPAIR GUIDE, AIR CONDITIONERS / HEAT PUMPS
REPAIR & DIAGNOSTIC FAQs for A/C
THERMOSTATS, HEATING / COOLING
THERMOSTATIC EXPANSION VALVES
WATER COOLED AIR CONDITIONERS
WINDOW / WALL AIR CONDITIONERS
WINDOW / WALL A/C SUPPORTS
The cost & trouble caused by missing or leaky air filters on HVAC systems: this article explains the effects of operating a heating or air conditioning system without proper air filters in place. This article series answers almost any question you might ask about air filters for heating or air conditioning systems. We explain how an air conditioning service technician will diagnose certain common air conditioning system failures or defects. We include photographs to assist readers in recognizing cooling system defects.
Green links show where you are. © Copyright 2013 InspectAPedia.com, All Rights Reserved. Author Daniel Friedman.
Leaky HVAC system air filters mean increased system operating costs, energy wastage, and ultimately increased service and repair costs.
Bending over the end of an air conditioner or heating air handler filter such as shown in the photo at left above is a bad idea. If the filter does not fit there will be bypass leakage past the filter, soiling the blower fan, slowing air flow, and leading to more costly cleaning and service later.
Furthermore when you bend the filter as this owner did, you interrupt the structural integrity of the filter's frame, risking filter collapse. A collapsed air filter can be drawn right into the blower fan, causing damage to the fan motor or even leading to a fire!
The photo at right shows how a college HVAC maintenance crew kept the A/C system running when the school did not have the proper filter size in stock. This filter installation also will have severe bypass leakage around the filter where the pleated section contacts the edges of the filter slot.
Installing a filter that is the wrong size for the heating or air conditioning air handler defeats the purpose of air filters because of leakage and it may be unsafe. Install a properly-sized filter in locations like this as soon as possible and watch out for unsafe filter collapsing.
How to Construct or Obtain Large or Special-dimension HVAC System Air Filters
Air filter suppliers and manufacturers have no trouble providing air filters of special dimensions. Furthermore if the filter is built by a manufacturer it's more likely that they'll understand the structural and strength requirements of the filter as well as the required airflow characteristics and filtering ability. We list some suppliers of air filters at SOURCES FOR AIR FILTERS
Incidentally, except unusual cases with special requirements, wouldn't it have made sense for the HVAC or duct system designer to have specified a filter that is one of the many standard sizes?
Lost or missing HVAC system air filters mean increased system operating costs, energy wastage, and ultimately increased service and repair costs.
Should we Filter or Clean Air Before it Enters the Air Handler Unit?
If we clean the air before it enters the air handling unit will that reduce the workload and hence the electric consumption of the air handling unit fan , and if so by how much ? In addition I would like to ask where else can there be savings in electricity. Is there a study made by ASHRAE or someone else that I can buy ? - Ziad I. Ghandour
Reply: Proper Air Filtration Saves Energy and Reduces HVAC System Operating & Service Costs
Cleaning the air before it enters the air handler, if you mean by using an air filter upstream of the air handler unit (AHU) is good practice. In the short run, airborne dust and debris don't have much impact on the blower assembly itself. But over time the following problems occur:
Dust collects on the squirrel cage blower assembly, filling in fan blade curvature and significantly reducing the air output of the system
Dust collects on the evaporator coil, ultimately blocking it, reducing air flow, and often causing coil icing
Those conditions increase the operating cost of the system and can eventually lead to costly service calls These are practical HVAC maintenance conditions, not something for which we have seen a peer-reviewed ASHRAE study.
Frequently Asked Questions (FAQs)
No FAQs have beenn posted for this topic. Try the search box below or CONTACT US by email if you cannot find the answer you need at InspectApedia.
Questions & answers or comments about air filter mistakes: wrong size, wrong fit, leaks, bad air filtration, dirty ducts, extra expense.
Ask a Question or Enter Search Terms in the InspectApedia search box just below.
Technical Reviewers & References
Related Topics, found near the top of this page suggest articles closely related to this one.