Question? Just ask us!
Free Encyclopedia of Building & Environmental Inspection, Testing, Diagnosis, Repair
InspectAPedia ® Home
AIR CONDITIONING & HEAT PUMP SYSTEMS
A/C - HEAT PUMP CONTROLS & SWITCHES
A/C DATA TAGS
A/C DIAGNOSTIC FAQs
A/C TYPES, ENERGY SOURCES
AGE of AIR CONDITIONERS & HEAT PUMPS
AIR CONDITIONER BTU CHART
AIR CONDITIONER COMPONENT PARTS
AIR FILTERS for HVAC SYSTEMS
AIR FLOW MEASUREMENT CFM
AIR HANDLER / BLOWER UNITS
BACKUP HEAT for HEAT PUMPS
BLOWER FAN CONTINUOUS OPERATION
BLOWER FAN OPERATION & TESTING
BOOKSTORE - Air Conditioning "How To" Books
CAPACITORS for HARD STARTING MOTORS
CIRCUIT BREAKER SIZE for A/C or HEAT PUMP
CLEANING & Legionella BACTERIA
COMPRESSOR & CONDENSING COIL, A/C
CONDENSATE HANDLING, A/C
CONTROLS & SWITCHES, A/C - HEAT PUMP
COOL OFF HEAT Thermostat Switch
COOLING CAPACITY, RATED
COOLING COIL or EVAPORATOR COIL
DATA TAGS on AIR CONDITIONERS
DEFINITION of HEATING & COOLING TERMS
DIAGNOSTIC GUIDES A/C / HEAT PUMP
DUCT SYSTEM & DUCT DEFECTS
DUST, HVAC CONTAMINATION STUDY
EDUCATION, HVAC SCHOOLS
ELECTRIC MOTOR DIAGNOSTIC GUIDE
EVAPORATOR COIL or COOLING COIL
EVAPORATIVE COOLING SYSTEMS
EXPANSION VALVES, REFRIGERANT
FAN, AIR HANDLER BLOWER UNIT
FAN AUTO ON Thermostat Switch
FAN, COMPRESSOR/CONDENSER UNIT
FAN CONVECTOR HEATERS - HYDRONIC COILS
GAS DETECTION INSTRUMENTS
GAUGE, REFRIGERATION PRESSURE TEST
HEAT LOSS (or GAIN) in buildings
HEAT LOSS (or GAIN) INDICATORS
HEAT LOSS R U & K VALUE CALCULATION
HUMIDITY LEVEL TARGET
INSPECTION CHECKLIST - OUTDOOR UNIT
INSPECTION LIMITATIONS, A/C SYSTEMS
LOST COOLING CAPACITY
LOW VOLTAGE TRANSFORMER TEST
MANUALS & PARTS GUIDES - HVAC
MOTOR OVERLOAD RESET SWITCH
MOLD in AIR HANDLERS & DUCT WORK
NOISE AIR CONDITIONER / HEAT PUMP
ODORS in AIR HANDLERS & DUCT WORK
OPERATING COST, AIR CONDITIONER
OPERATING DEFECTS, AIR CONDITIONING
OPERATING TEMPERATURES, AIR CONDITIONER
PORTABLE ROOM AIR CONDITIONERS
PRESSURE READINGS, REFRIGERANT
REPAIR GUIDES A/C / HEAT PUMP
REPAIR & DIAGNOSTIC FAQs for A/C
REFRIGERANTS & PIPING
RETROFIT SIZING for A/C or HEAT PUMPS
SEER RATINGS & OTHER DEFINITIONS
SPLIT SYSTEM AIR CONDITIONERS & HEAT PUMPS
THERMOSTATS, HEATING / COOLING
THERMOSTATIC EXPANSION VALVES
WATER COOLED AIR CONDITIONERS
WINDOW / WALL AIR CONDITIONERS
WINDOW / WALL A/C SUPPORTS
Clearance distances for outdoor HVAC compressor/condenser units: this article describes the recommended minimum (and maximum) distances to separate an air conditioner or heat pump outdoor compressor/condenser unit from building walls, other equipment, fences, shrubs, etc. In our photoat page top these two compressor/condenser units are too close together as well as too close to the building walls.
Green links show where you are. © Copyright 2014 InspectApedia.com, All Rights Reserved.
Air Conditioning & Heat Pump Equipment Minimum Clearance Distances from Building Walls, Shrubs, Other Equipment
Blocking air flow through the outdoor A/C or heat pump compressor/condenser unit is a really bad idea that shortens equipment life (as the equipment runs hotter) and increases system operasting costs (for the same reason - hotter opeating temperature means lower efficiency during the cooling season).
Air conditioning or heat pump compressor/condenser units mounted too close to a wall, surrounded by shrubs, or multiple units located too closely together will probably not receive enough cool air flow to function properly.
And even worse, compressor/condenser units that are too close together not only have to fight for their incoming cooling air, but they may veed hot exhaust air to one another, increasing their operating temperatures still further.
The final authority on proper HVAC equipment clearance distances is the manufacturer's installation instruction manual. But here are some general rules of thumb for air conditioner or heat pump clearances that we will cite here.
In our photo at left the A./C compressor units are too close together and also suffer from airflow blocked by shrubbery.
This collection of air conditioning compressors are too many too close together - they will be fighting for cooling air around the condenser unit, increasing operating cost and shortening air conditioner compressor life.
Rule of Thumb Lateral or Horizontal A/C / Heat Pump clearance distances
If there are multiple air conditioner or heat pumps installed in the same area, and following the sense of the rule above, I'd keep the units at least 4 ft. apart from one another as well.
In our photo (left) from a home in New York, the compressor/condenser unit actually leaning against the house wall (its support pad tipped). About 1/3 of the air flow from this unit is completely blocked by the building wall.
At least the wall kept the unit from tipping over, though.
Closest recommended clearances for A/C or Heat Pump Compressors
If you do not have manufacturer's installation instructions at hand we recommend following the "rules of thumb" for A/C or heat pump clearance distances given above.
But of course the final authority is the equipment manufacturer. Here is an adapted (reformatted) quote of clearance requirements from a Carrier 24ANA Infinitiy Series Air Conditioner of 2-5 nominal ton size A/C equipment installation manual:
What about other building mechanical systems that would interfere with the heat pump or air conditioner compressor-condenser unit?
In our photo at left, from a Minneapolis MN home, these two compressor/condenser units are just about three feet apart - a little close, and that right-most larger compressor/condenser unit is too close to building walls, a clothes dryer vent, and shrubbery.
We also see that direct-vented heating appliance white PVC piping is blowing exhaust close to these units. The installation is nice-looking and neat though.
These four air conditioner compressors were found jammed into a wall niche along a street in Queretero, Mexico.
These units may have a short life before needing replacement.
Where there simply is not adequate space to provide proper air circulation around an air conditioning compressor or multiple compressors, it may be a good idea to let the building owner know that the units won't have a long life.
Rule of Thumb Vertical A/C / Heat Pump clearance distances
So obstructing airflow out at the unit top will also reduce air flow across the condensing coils, shortening equipment life and cutting its efficiency.
A rule of thumb is to assure that there is at least 4 ft. above the A./C compressor/condenser unit.
For example, installing an A./C or heat pump compressor under an outdoor deck might block its airflow (not to mention the noise aggravation).
In fact typical A/C or heat pump installation insturctions recommend that you locate the unit away from windows, patios, decks, etc., where unit operation sound may disturb the customer.
Possible A/C or heat pump Clearance Distance Exceptions
The most important clearance distances to respect around an outdoor air conditioner or heat pump compressor/condenser unit are with respect to those sides of the equipment through which air is intended to flow - either "in" to the unit our "out" of the unit.
Some outdoor units use a top mounted fan that blows "up" out of the unit, drawing cooling air through the condensing coils at one or more sides of the equipment. For these units both side clearance and top clearance must be respected.
But often the condensing coil does not extend through all four sides of the unit. If this is the case, the distance clearance from the side of a unit through which no air is expected to flow is probably less critical - though you should still be careful that multiple units placed too close together are not competing for the same air.
In our photo above, air moves into this compressor/condenser through three of its sides, but its "back side" (facing the building wall) is not one thorugh which air moves.
Moving an air conditioner compressor to a distance of about 40 feet from a building won't prevent it from working, but the installer might need to adjust the diameter of the refrigerant lines to be sure that the equipment is working at 100% of its capacity.
it's not that the air conditioner won't work at all if the compressor/condenser is located at an unusual distance from the air handler/evaporator coil, it's more that it may lose some capacity and have to work harder - meaning higher electrical bills and in extreme cases, shorter equipment life.
Some air conditioner manufacturers such as McQuay provide a refrigeration piping guide that gives complete, detailed guidance and charts on refrigerant line sizing (diameter) as a function of length of run.
Details about refrigerant piping diameters, distances, and effects on equipment operation are at REFRIGERANT PIPING & DISTANCES.
Green link shows where you are in this article series.
Frequently Asked Questions (FAQs)
No FAQs have been posted for this page. Try the search box below or CONTACT US by email if you cannot find the answer you need at InspectApedia.
Try the search box just below or if you prefer, post a question or a comment in the Comments box below and we will respond promptly.
Search the InspectApedia website
HTML Comment Box is loading comments...
Technical Reviewers & References
Related Topics, found near the top of this page suggest articles closely related to this one.