Question? Just ask us!
Free Encyclopedia of Building & Environmental Inspection, Testing, Diagnosis, Repair
InspectAPedia ® Home
AIR CONDITIONING & HEAT PUMP SYSTEMS
A/C - HEAT PUMP CONTROLS & SWITCHES
AIR CONDITIONER COMPONENT PARTS
AIR CONDITIONER TYPES, ENERGY SOURCES
AIR FILTER EFFICIENCY
AIR FILTERS, FIBERGLASS PARTICLES
AIR FLOW MEASUREMENT CFM
APPLIANCE EFFICIENCY RATINGS
BLOWER DOORS & AIR INFILTRATION
BLOWER FAN CONTINUOUS OPERATION
BLOWER FAN OPERATION & TESTING
BOOKSTORE - Air Conditioning "How To" Books
CAPACITORS for HARD STARTING MOTORS
CLEANING & Legionella BACTERIA
CHINESE DRYWALL HAZARDS
CONDENSATION or SWEATING PIPES, TANKS
DEFINITION of Heating & Cooling Terms
DEW POINT CALCULATION for WALLS
DEW POINT TABLE - CONDENSATION POINT GUIDE
DIAGNOSTIC GUIDES A/C / HEAT PUMP
DIAGNOSE & FIX HEATING PROBLEMS-BOILER
DIAGNOSE & FIX HEATING PROBLEMS-FURNACE
DUCTS - Asbestos
DUCT INSULATION, Asbestos Paper
DUCT INSULATION for SOUNDPROOFING
DUCT SYSTEM & DUCT DEFECTS
DUCT SYSTEM NOISES
DUCTS, Asbestos Transite Pipe
DUST, HVAC CONTAMINATION STUDY
ELECTRIC MOTOR OVERLOAD RESET SWITCH
EVAPORATIVE COOLING SYSTEMS
FAN LIMIT SWITCH
GAS EXPOSURE EFFECTS, TOXIC
GAS DETECTION INSTRUMENTS
HEAT LOSS (or GAIN) in buildings
HEAT LOSS (or GAIN) INDICATORS
HEAT LOSS R U & K VALUE CALCULATION
HEATING SMALL LOADS
INSPECTION CHECKLIST - OUTDOOR UNIT
INSPECTION LIMITATIONS, A/C SYSTEMS
LEED GREEN BUILDING CERTIFICATION
LOST COOLING CAPACITY
LOW VOLTAGE TRANSFORMER TEST
MOTOR OVERLOAD RESET SWITCH
MOLD in AIR HANDLERS & DUCT WORK
OPERATING COST, AIR CONDITIONER
OPERATING DEFECTS, AIR CONDITIONING
REPAIR GUIDES A/C / HEAT PUMP
REPAIR & DIAGNOSTIC FAQs for A/C
THERMOSTATS, HEATING / COOLING
THERMOSTATIC EXPANSION VALVES
WATER COOLED AIR CONDITIONERS
WINDOW / WALL AIR CONDITIONERS
WINDOW / WALL A/C SUPPORTS
Air conditioner condensate pump guide: this air conditioning repair article discusses the inspection of air conditioning condensate pumps & condensate pump control systems, including their proper installation. This is part of our installation, inspection, & troubleshooting guide for condensate piping, traps, drains, condensate pumps, and the detection and hazards of air conditioning system condensate leaks in buildings.
Green links show where you are. © Copyright 2013 InspectAPedia.com, All Rights Reserved.
Air conditioner condensate pumps are a convenient way to collect and dispose of the condensate produced by an air conditioning system when the air handler/cooling coil are located in a building location where the cooling condensate cannot be drained away by gravity. The most common situation is the need to dispose of air conditioner condensate produced by an air handler which is installed in a building basement or crawl space.
How an Air Conditioner Condensate Pump Works
Sequence of Steps in the Operation of an Air Conditioner Condensate Pump
Proper and Improper Places to Route and Connect an Air Conditioner Condensate Pump Drain Line
Here is an excerpt from the Uniform Mechanical Code pertaining to the disposal of air conditioning condensate: "Section 310.0, 310.1 Condensate Disposal.
To clarify, an indirect waste pipe is something that is upstream of a trap. That means we cannot dump into anything downstream of a trap. That would include the main plumbing vent stack - a common error in disposing of air conditioner condensate in attic installations. -- [Thanks to Al Carson, Carson Dunlop Associates, Toronto]
Acceptable methods to dispose of air conditioning condensate from a condensate pump
Air conditioning condensate drain connections which are not recommended or are not best practice
What else goes wrong with air conditioning condensate pumps
Frequently Asked Questions (FAQs) About How to Install, Diagnose, & Repair an Air Conditioner or Heat Pump Condensate Drain Pump
No FAQs have been posted for this page. Try the search box below or CONTACT US by email if you cannot find the answer you need at InspectApedia.
Question: Requirement for a trap on condensate drain lines; leaks led to ceiling fan collapse
As a homeowner I installed a condensate pump for my attic-located air conditioner as described above.
When my A/C tech inspected he said a horizontal flow air handler does not have a trap on the condensate output so air is drawn in through the air gap at the pump collection tank. This air flow keeps the condensate from flowing out the drain until the air handler blower shuts off, creating a tidal wave of water which sloshes where its not supposed to including the emergency drain pan. (My ceiling has fallen in 3 times due to overflowing emergency pan which did not drain properly.) - Bob Farrell 06/09/11
Question: The GFCI Receptacle that powers the condensate pump keeps tripping off - is a GFI required?
Frequent tripping GFI receptacle to condensate pump - Larry B 8/7/11
Does a condensate pump need to have a a GFCI receptacle - Bill Hastings 8/22/11
Reply: how to fix nuisance tripping of a GFCI in a damp area, basement, crawl space, etc.
Larry if the GFCI receptacle powering your condensate pump keeps tripping
Bill, the requirement for a GFCI receptacle for a condensate pump would come from where the electrical receptacle is located. For example electrical codes want GFCI protection in garages and perhaps in basements and crawl areas.
Question: Bad condensate sensor switch shuts down the air conditioner system
I have to jumpered the a/c line (yellow) to the hot(24 volts-red) on the ignition board to get the system to come back on while shopping for a new switch or pump.
I set the condensate pump to "continuous run" as a temporary measure to prevent flooding, but risk burning out the motor to the condensate pump.
- Yaga 8/13/11
Yaga additional risks from condensate leaks into a building when you bypass or "hot wire" the condensate overflow tray sensor switch are condensate leak overflow, building damage, and mold damage
Question: what is the "overflow" box connected to my condensate pump reservoir?
Hi I have a reservoir with a condensate pump in it~ also there is another pvc pipe coming out of the other end of reservoir going up to a box that says overflow. For the first time water came out and on to the floor? any ideas? thanks! Archie 06/02/12
Archie, if that "box that says overflow" is under your A/C or heat pump unit it may be that the main condensate drain line is clogged so condensate is spilling into an overflow pan rather than being routed normally to the condensate pump.
breaker, fire o matic?, emergency switch all fine, but condensate pump outlet & ac unit will not work - Will 8/1/2012
Will, do you mean that the condensate pump outlet is wired off of air handler circuit or out of a service or utility receptacle that is powered by the air conditioner's own power circuit?
For detailed steps in diagnosing the reason why your air conditioner is not working, start at DIAGNOSTIC GUIDES A/C / HEAT PUMP.
Questions & answers or comments about the installation, inspection, troubleshooting & repair of air conditioner condensate pump systems used to remove HVACR condensate.
Ask a Question or Enter Search Terms in the InspectApedia search box just below.
Technical Reviewers & References
Related Topics, found near the top of this page suggest articles closely related to this one.