Question? Just ask us!
Free Encyclopedia of Building & Environmental Inspection, Testing, Diagnosis, Repair
InspectAPedia ® Home
AIR CONDITIONING & HEAT PUMP SYSTEMS
A/C - HEAT PUMP CONTROLS & SWITCHES
AIR CONDITIONER COMPONENT PARTS
AIR CONDITIONER TYPES, ENERGY SOURCES
AIR FILTER EFFICIENCY
AIR FILTERS, FIBERGLASS PARTICLES
AIR FLOW MEASUREMENT CFM
APPLIANCE DIAGNOSIS & REPAIR
APPLIANCE EFFICIENCY RATINGS
BLOWER DOORS & AIR INFILTRATION
BLOWER FAN CONTINUOUS OPERATION
BLOWER FAN OPERATION & TESTING
BOOKSTORE - Air Conditioning "How To" Books
CAPACITORS for HARD STARTING MOTORS
CLEANING & Legionella BACTERIA
CHINESE DRYWALL HAZARDS
CONDENSATION or SWEATING PIPES, TANKS
DEFINITION of HEATING & COOLING TERMS
DEW POINT CALCULATION for WALLS
DEW POINT TABLE - CONDENSATION POINT GUIDE
DIAGNOSTIC GUIDES A/C / HEAT PUMP
DIAGNOSE & FIX HEATING PROBLEMS-BOILER
DIAGNOSE & FIX HEATING PROBLEMS-FURNACE
DUCTS - Asbestos
DUCT INSULATION, Asbestos Paper
DUCT INSULATION for SOUNDPROOFING
DUCT SYSTEM & DUCT DEFECTS
DUCT SYSTEM NOISES
DUCTS, Asbestos Transite Pipe
DUST, HVAC CONTAMINATION STUDY
ELECTRIC MOTOR OVERLOAD RESET SWITCH
EVAPORATIVE COOLING SYSTEMS
FAN LIMIT SWITCH
GAS EXPOSURE EFFECTS, TOXIC
GAS DETECTION INSTRUMENTS
HEAT LOSS (or GAIN) in buildings
HEAT LOSS (or GAIN) INDICATORS
HEAT LOSS R U & K VALUE CALCULATION
HEATING SMALL LOADS
INSPECTION CHECKLIST - OUTDOOR UNIT
INSPECTION LIMITATIONS, A/C SYSTEMS
LEED GREEN BUILDING CERTIFICATION
LOST COOLING CAPACITY
LOW VOLTAGE TRANSFORMER TEST
MOTOR OVERLOAD RESET SWITCH
MOLD in AIR HANDLERS & DUCT WORK
OPERATING COST, AIR CONDITIONER
OPERATING DEFECTS, AIR CONDITIONING
REPAIR GUIDES A/C / HEAT PUMP
REPAIR & DIAGNOSTIC FAQs for A/C
THERMOSTATS, HEATING / COOLING
THERMOSTATIC EXPANSION VALVES
WATER COOLED AIR CONDITIONERS
WINDOW / WALL AIR CONDITIONERS
WINDOW / WALL A/C SUPPORTS
Air conditioner or heat pump noise diagnosis & cure: this air conditioning repair article discusses the diagnosis and repair of air conditioning compressor noises which range in importance from normal (if annoying squeaks and squeals, to rattling loose bolts and hardware, to costly compressor damage indicating air conditioning compressor or A/C compressors at or near end of their life.
Green links show where you are. © Copyright 2014 InspectApedia.com, All Rights Reserved.
The following HVAC noise descriptions are a continuation from the article beginning at NOISES, HVAC SOUND DESCRIPTIONS with a description of BANGING A/C or heat pump
Hissing sound and humming from my AC - It was the capacitor! Thanks! - Bingo
Question: Hissing Compressor noises, ice on the suction line, hissing ssssss sounds from air conditioner
sir i check my out door unit i see the compressor is getting cold and after few minutes the amperes will going up start in 17 up to 20amp.,and it comes sound like noise, yes that was my compressor also, din after few minutes suck line becomes ice and noise coming like ssssssssssssssssssssssssssssssssssssssssss..... - Danny Carumba
Watch out: Danny: Because SOME A/C compressor hissing noises can be due to dangerous internal over-pressure conditions, I'd ask a service technician to check the air conditioner promptly. Please see our catalog of sources of hissing sounds in air conditioners and heat pumps, described at SCREAMING A/C compressor/condenser unit sounds. Such equipment should be shut off immediately.
Question: Hissing in "surround sound" after installing a new high efficiency A/C and Heating System
I have a very high pitch hissing sound "surround sound" throughout the whole condo. We did install a new /better/efficient AC/heating system...some original duct and tubing is still in place. The problem is, we can't sleep with this noise! And cannot pinpoint where its's coming from: wall.
I need a professional with GOOD hearing to hear this. We will be putting some sound proofing on the garage back wall that abuts, unfortunately the condo (6 units attached) doghouse. We have had all items on the wall of the doghouse shut off and can STILL hear this high pitch hissing? Any suggestions to what we can do and WHO to contact? Have had 2 electricians, and audiologist, etc. check this but their hearing is not like mine and I do not have tinnitis, because when out and about I hear fine and not the hissing. HELP please. I really don't want to move. - El
Reply: Track down sound source before installing soundproofing around an A/C or heat pump system
El, before installing soundproofing it makes sense to track down the source of the annoying noise - especially since the noise, if abnormal, could indicate failing or even unsafe equipment that needs repair.
We discussed hissing at the compressor condenser unit at SCREAMING A/C and warned about this problem in the article above. But not all hissing is due to extreme pressure. An A/C or heat pump compressor (of the reciprocating or piston and cylinder design) that continues to run with damaged internal refrigerant valves may make a hissing noise too. In this case the motor will continue to run, it may not even overheat, but it's wasting electricity and running more than it should. An HVAC tech may diagnose bad A/C compressor valves by noticing that the high and low side pressures equalize very quickly when the motor stops.
Hi Dan ...thank you for responding to my question ....I cannot track down the source...it's Surround sound....everywhere....not emanating from one spot unfortunately! I do live in a condo setting, had the Condo president shut off all electrical items in the doghouse: housing of the electrical, pumps, phone, etc ...shutdown could still hear the noise! It seems no one can hear this ...except my family and none of us are in a business to locate the source.
We do have all underground lights, no poles ....I have tried earplugs even, I don't have tinnitis, because when I am not inside the condo...no problem. Electricians and even PSNH don't seem to hear the very high pitch noise. If I could locate the source: one spot ...I would gladly put a hole there. I think until everyone else's' stuff starts breaking down so we can get a 5 for 1 deal this won't be fixed...and I know at this point the original builder is probably past the taking to court stage. Contractors who worked on these? To pass code IMO ...barely. Any sources or websites you can suggest I'd appreciate. Thank you. EL
I would also like to mention that a Large PSNH box sits at the end of our driveway....they opened it up and changes a plug of sorts (???) not sure what, but also, a lot of underground cables under our particular front yard:PSNH, cable ...etc. it would cost a lot know it would cost a lot , but don't feel we should have to pay since it (source)unknown still ....is the cause. We also, have to contact Dig Safe prior to planting..
.I would think that the cable's, etc. would be way under , at least 4 or so feet...does anyone know building codes on cable depth necessary to pass codes in NH? If so please post here and info. as to contacts:web page , phone numbers, etc...it seems to have increased as far as sound over the past 4-5yrs. We have also had a PSNH person come out to our condo to check our meter and it says with limits of Section PUC 304.02 by NHP Utilities (NHPUC), Chapter PUC 300, rules and reg's for electric utilities .....really ...I feel like I've exhausted my resources and I am not in this field...any thoughts to help? - El.
El, beginning at NOISE / SOUND DIAGNOSIS & CURE we organize some approaches to trying to track down odd sounds. To get anywhere with public officials or electricians they will of course need to either hear the sound themselves or confirm it with instruments.
Question: Hissing sound traced to a bad capacitor?
Hissing sound and humming from my AC - It was the capacitor! Thanks! - Bingo
Question: Hissing at compressor/condenser unit in hot weather, heavy load or after 5 minutes
I have a carrier 2000, don't know how many tons it is but here's the problem; I had a few hot days above 100 with abnormally high humidity. I turned on the AC in the early morning when it was relatively cool. It ran for 3 days straight with no issues. Then I noticed the air wasn't cool at all. Just warm and humid. I went outside to investigate... The condenser was making an obnoxious humming and it sounded like the compressor had a blow of valve. It was hissing like it had a leak with a large amount of pressure behind it. I waited a couple days to turn it back on. It started fine the condenser sounded good and the fan started like it should and it was finally pumping out cold air. 5 minutes go by. I hear the loud humming again and the hissing. So here is my question: Is my compressor shot or am I low on freon. Because it will over heat and shut down. Thanks for your help.
Aaron: "The condenser was making an obnoxious humming and it sounded like the compressor had a blow of valve. It was hissing like it had a leak with a large amount of pressure behind it." suggests an overpressure at the compressor, perhaps a blocked condensing coil or dryer. Your system needs service, but the compressor is not necessarily shot - let us know what your tech says.
Dan: Thanks for the tip. By doing some research (and I am no HVAC guy by any means) I found that the compressor would indeed over heat because of too much pressure. I looked at the a coil in the furnace itself and it looked fine. I don't however understand " the dryer" factor. I did wash the outside of the unit before i started it and the air filter is spotless.
Aaron: if there is an overpressure at the compressor, a cause is usually a blockage somewhere. I don't know all possible causes, but some examples are
or wa-wa-wa sounds or wow wow wow sounds or Huffing & Puffing Sounds: examples, diagnosis, repair advice
Question: Thanks for posting this -- it's been helpful to read! My question: The fan runs fine on our AC unit, but the compressor makes a slow, thrummy, WuwWuwWuw sound about every 30 seconds, as if it's trying to start up but can't, and there's no cold air coming out of our vents. I'm not sure if this is the same as the "humming" described above. Is it possible that this is caused by a loose connection or faulty capacitor? Or should I assume that it's something more serious? - Tiny
Question: Ours has a different sound outside: a sort of huffing and puffing. We only hear it after the unit has been running for a long time. Any ideas? - Herbert Lewis
Question: I saw the q&a about the wow-wow-wow sound but no answer other than tell us what you found. I have had it since it was installed but the heat pump tech said it was normal. I know it was not but gave up. Now it's bothering me more. Any new/better answers? The wow cycle period is about one second - in radar search antennas we used to call it "hunting." (for the right speed). There it had to do with control feedback settings, but somehow that doesn't translate to a heat pump unless it means too much coolant. Could that be it? - Dick, 3/11/2012
Reply: Huffing Puffing wawa or wowwow A/C Units - still and open question, how to investigate
Herbert: huffing and puffing is a new one to me: an air conditioner compressor making this noise might be reaching an overpressure condition due to a control failure or blockage - let us know what your HVAC tech diagnoses - it will surely help other readers
Sometimes the wowwow sound is from a compressor that is hard-starting. In that case you are hearing the electric motor trying to start against head pressure (or against a binding internal part), perhaps cycling on and off.
Dick, thanks for the question. We're very serious about developing a dictionary of sounds and their diagnosis and cure; but sometimes, especially by text, I just don't quite know what a sound is or even quite what it sounds like. The wowwow is one of those I'm unsure about in that there are several causes and several sounds that people describe as wowwow wawa. But in this FAQ (just above and continued below) we include some possible explanations and will add others as they crop up.
An on-site an expert might observe something cycling (as you describe) that helps track down the problem. For example, if you used a mechanic's stethoscope and tracked the sound to a specific part that is emitting the sound (probably a compressor or maybe a thermostatic expansion valve, on occasion a fan motor or bearing) then once we know where the sound is coming from, we can dig into what might cause that part to do that. For example a part on a system may be making a sound not because that part is itself defective but due to another control.
The sound is LOUD and must be from the compressor itself and passed along via the tubing.. The compressor is outside on the ground level and it is distracting on the floor above (beach house on stilts).
Here are some added steps to take to track down a sound to its exact source - a first step in diagnosing sounds
Pick up a mechanic's stethoscope (at your local auto supply store).
Go to the piece of equipment, air handler indoors, compressor/condenser unit outdoors, and listen to be sure you're in the right area.
Use the rod in the stethoscope to track the sound to a specific part that is emitting the sound (probably a compressor or maybe a thermostatic expansion valve, on occasion a fan motor or bearing.
Watch out: there are electrocution shock hazards and cut-off finger hazards or other injury hazards from moving parts and live electrical contacts. While the equipment has to be running if we're going to track down a sound to its emitting part, this process should be performed with great care and by someone with experience to avoid the chances of a serious injury.
Then once we know where the sound is coming from, we can dig into what might cause that part to do that. For example a part on a system may be making a sound not because that part is itself defective but due to another control.
Reply: Hard Starting A/C and Heat Pump Compressors May Make Groans, Wuw, and WaWa or Wah-Wah-Wah- Sounds
Tiny, it sounds as if your A/C compressor is indeed having trouble starting; It makes sense to be sure all wiring connections are secure (Watch out for electrocution shock hazards) but I suspect you need a hard-start/run capacitor kit. I would leave the system OFF until it is repaired. And keep in mind that a hard-starting compressor may be at/near end of its life.
Thanks so much for that input. I've been trying to decide whether it's worth having someone come out to check the capacitor, and it sounds like it might be. I'm not really prepared to pay to replace the compressor or the whole unit this summer, especially since I'm up in Canada, so the A/C is more like a luxury than a necessity. Thanks again! - Tiny
Reply: check for bad start capacitor;
I think it's worth checking for a bad start/run capacitor because if that's the problem it's an inexpensive part and avoids someone selling you a compressor condenser unit that you probably didn't need. Also a bad motor winding can cause similar complaints.
I have a 13 year old Armstrong AC, 4 ton, 10 S.E.E.R. in our house. For the past 5 years (ever since we got into the house), the outdoor compressor unit has been making loud humming sound. The sound does not sound like humming if I stand next to the compressor unit outside.
However, inside the house, the sound is of humming. The AC has worked fine - no leaks, cools properly etc. I have had it serviced but every time the service person chalks the noise to age and recommended a new AC w/o any investigation. It could be just age but I'd welcome suggestions things I can check for myself.
I followed the two lines (thin copper line and the larger/covered in black line) running between outdoor and indoor AC units. If I put my ear next to the larger line, I can clearly hear the humming sound along its length as I move from the outdoor AC unit to the indoor condenser unit. I can also feel vibrations/tremors on this larger line.
I have been hearing a humming when my air conditioner is running now for about a week but the air is cool and working o.k. but this is coming from the compressor outside and wondered what it could be??? - Joyce Ballard
There is a humming noise coming from the Heat Pump AC unit when the thermostat is in the cool setting, but the thermostat is set below room temperature (air conditioner not running). If I move the switch on the thermostat to the off position the humming stops in the unit. Do you have any idea what is wrong? Thanks, Don 6/3/12
Hi, I live on the second floor of a condo and hear a loud constant low pitched humming noise coming from inside the wall where the tubing enters the unit from the outside and travels up the wall and across the ceiling to the internal blower. The sound is not present when the heat is on. It is a deep harmonic mmmm sound and has a vibration component. The AC blows cold and otherwise seems to be working. The compressor is 10 years old. - Barbara Rich 4/9/12
Reply: Pinning down the exact humming noise source on HVAC equipment: refrigerant line noise transmission, loose component parts, low voltage transformers, and hard starting -electric motors
A humming noise that you are hearing at the larger refrigerant line (the suction or "low pressure" line) can help you trace the noise to its source: the indoor air handler or the outdoor compressor-condenser. Knowing the source can help track down a detail that may or may not be repairable, such as a loose part, loose compressor mount, or worn out compressor internal parts.
Watch out: a humming noise coming from an electric motor or A/C - Heat Pump compressor motor that is not actually starting and running is likely to indicate that the motor is unable to start, and is at risk of overheating or damage. Humming from a motor that can't start is sometimes repaired by replacing a bad start/run capacitor, but if the motor is actually failing and seizing, it will need replacement.
Humming sounds are also given out by a low voltage transformer that is headed for failure.
Question: Condenser not working, humming sounds
My a/c condenser is not working, the fan blades do not turn, when I lower the indoor thermostat and then go out doors to the condenser pad, I hear " a humming click" approximately every twenty seconds or so, as if the unit is trying to turn on.
Hilary it sounds as if you are describing a hard-starting or stuck compressor motor. The click you hear may be the the result of the system turning itself off (unable to start) followed by a cool-down interval, and then the system tries again. You need a diagnostic service call and if in luck it could be a a bad start capacitor. Out of luck, a shot compressor. Other problems can also cause the compressor to have trouble starting, such as a bad refrigerant control valve.
Continue Reading more Noise Descriptions at noise group 4 beginning with LOUD NOISE at STARTUP> from A/C or heat pump system
Green link shows where you are in this article series.
Noise group 1 of 5 is below
Noise group 2 of 5 is below
Noise group 3 of 5 is below
Noise group 4 of 5 is below
Noise group 5 of 5 is below
Frequently Asked Questions (FAQs)
No FAQs have been posted for this page. Try the search box below or CONTACT US by email if you cannot find the answer you need at InspectApedia.
Try the search box just below or if you prefer, post a question or a comment in the Comments box below and we will respond promptly.
Search the InspectApedia website
HTML Comment Box is loading comments...
Technical Reviewers & References
Related Topics, found near the top of this page suggest articles closely related to this one.