Question? Just ask us!
Free Encyclopedia of Building & Environmental Inspection, Testing, Diagnosis, Repair
InspectAPedia ® Home
AIR CONDITIONING & HEAT PUMP SYSTEMS
A/C - HEAT PUMP CONTROLS & SWITCHES
AIR CONDITIONER COMPONENT PARTS
AIR CONDITIONER TYPES, ENERGY SOURCES
AIR FILTER EFFICIENCY
AIR FILTERS, FIBERGLASS PARTICLES
AIR FLOW MEASUREMENT CFM
APPLIANCE EFFICIENCY RATINGS
BLOWER DOORS & AIR INFILTRATION
BLOWER FAN CONTINUOUS OPERATION
BLOWER FAN OPERATION & TESTING
BOOKSTORE - Air Conditioning "How To" Books
CAPACITORS for HARD STARTING MOTORS
CLEANING & Legionella BACTERIA
CHINESE DRYWALL HAZARDS
CONDENSATION or SWEATING PIPES, TANKS
DEFINITION of Heating & Cooling Terms
DEW POINT CALCULATION for WALLS
DEW POINT TABLE - CONDENSATION POINT GUIDE
DIAGNOSTIC GUIDES A/C / HEAT PUMP
DIAGNOSE & FIX HEATING PROBLEMS-BOILER
DIAGNOSE & FIX HEATING PROBLEMS-FURNACE
DUCTS - Asbestos
DUCT INSULATION, Asbestos Paper
DUCT INSULATION for SOUNDPROOFING
DUCT SYSTEM & DUCT DEFECTS
DUCT SYSTEM NOISES
DUCTS, Asbestos Transite Pipe
DUST, HVAC CONTAMINATION STUDY
ELECTRIC MOTOR OVERLOAD RESET SWITCH
EVAPORATIVE COOLING SYSTEMS
FAN LIMIT SWITCH
GAS EXPOSURE EFFECTS, TOXIC
GAS DETECTION INSTRUMENTS
HEAT LOSS (or GAIN) in buildings
HEAT LOSS (or GAIN) INDICATORS
HEAT LOSS R U & K VALUE CALCULATION
HEATING SMALL LOADS
INSPECTION CHECKLIST - OUTDOOR UNIT
INSPECTION LIMITATIONS, A/C SYSTEMS
LEED GREEN BUILDING CERTIFICATION
LOST COOLING CAPACITY
LOW VOLTAGE TRANSFORMER TEST
MOTOR OVERLOAD RESET SWITCH
MOLD in AIR HANDLERS & DUCT WORK
OPERATING COST, AIR CONDITIONER
OPERATING DEFECTS, AIR CONDITIONING
REPAIR GUIDES A/C / HEAT PUMP
REPAIR & DIAGNOSTIC FAQs for A/C
THERMOSTATS, HEATING / COOLING
THERMOSTATIC EXPANSION VALVES
WATER COOLED AIR CONDITIONERS
WINDOW / WALL AIR CONDITIONERS
WINDOW / WALL A/C SUPPORTS
Air conditioner or heat pump noise diagnosis & cure: this air conditioning repair article discusses the diagnosis and repair of air conditioning compressor noises which range in importance from normal (if annoying squeaks and squeals, to rattling loose bolts and hardware, to costly compressor damage indicating air conditioning compressor or A/C compressors at or near end of their life.
Green links show where you are. © Copyright 2013 InspectAPedia.com, All Rights Reserved.
The following HVAC noise descriptions are a continuation from the article beginning at NOISES, HVAC SOUND DESCRIPTIONS
A Hissing or Screaming A/C compressor, also described as "very loud screaming" by some sources , may be caused by excessive internal pressures - a dangerous condition. Compressors include a high pressure sensor that should shut the system down if internal pressures are approaching a dangerous level. But if the compressor continues to run and is screaming, turn it off immediately as the system is unsafe.
Sounds like a whining, singing or rumbling sound coming from the compressor/condenser unit fan motor may be due to a broken internal cooling fan motor part or a vibration set up between the fan blade and fan motor/shaft.
Reader Question: loud squealing, clanking compressor noise
Because I couldn't see clearly in the photo and there was some intermittent clanging, I first thought to check for a fan blade assembly that is hitting an obstruction, is loose on its drive shaft, wobbling, hitting the enclosure. But your note that the noise is intermitten argues against a loose part or assembly.
But ultimately, to me this sounds to me like a unit that is unable to start. I suspect a bad compressor motor or bearing. That cyclic sort of clanging-buzzing sound may be a motor or fan motor trying to start in response to a start relay; the continuous squealing though sounds like a bad motor.
I speculate that during the day the compressor is running continuously in hot weather, perhaps also making the motor itself quite hot. Then finally in the evening as temperatures fall, the compressor and centeral A/C gets ahead of the building cooling load enough to cycle off - but not for long. Trying then to re-start fairly quickly the motor may be unable to re-start against a remaining high refrigerant head-pressure.
Such troubles can be caused by a failing compressor motor, an improper refrigerant charge (less likely), a sticking refrigerant control valve (possible), or something else I haven't thought of.
It's time for a service call by an experienced HVAC tech.
Let us know what your service tech reports - what we learn will assist other readers.
Reader Question on squealing A/C outdoor compressor/condenser Unit
Our compressor started squealing intermittently the other night around 1:30am. Did it for about 2 hours but not consistently nor constantly. drove us and the dogs crazy. hasn't done it since. HVAC tech says it was the compressor bearings and can't fix it since its 20 year old unit. I think that's love. what do you say? - Secn
Normal vs abnormal squealing sounds at A/C compressors Secn: ... "that's love"... is that a new term for B. S. ?? Anyway, there are multiple possible sources of squealing, such as the compressor motor, or even a fan motor. If it's the compressor, it's dead or dying; because the units are hermetically sealed, they're not repairable.
Thanks Dan. yep, wonderful spell check changed from the word I had originally typed to "love". it was a clean word though but B. S. works just as well. hah aha. So, the tech also said it's drawing high amps along with the bad compressor. Would the cap fix this too? He said he can't service anything on it Cruz it is R22 freon and can't be obtained anymore. I know they are moving to the R410a but I still say B. S. - Secn
Sorry Secn but high amps draw means the motor is near end of life. The cap may keep it going a while but it sounds like it's bad news. Tech is also right about the refrigerant. You may be able to install a new compressor, evacuating and cleaning the system (better to do it BEFORE a compressor burnup as a burnup contaminates the piping and increases the later repair cost a bit), installing a new compressor and a substitute refrigerant, possibly having to make some other adjustments, but less costly than a wholesale replacement. Keep us posted. - DJF
Question: hard starting A/C compressor, squealing noises, high pressures: diagnosis & repair
Hello and thank you in advance for any assistance you can provide. My house central air conditioner began to make squealing nosies upon start up so we had a professional repair company come inspect it. It would still start, eventually, after turning itself off and on several timnes, and the cooling still worked great.
The first inspector said he checked coils (they were dirty and my husband cleaned them), capcity, contactor, etc. This person put on a hard start kit, and went away. Well, the problem was still there and in fact worse. We called again, and the company sent someone else who checked more areas and filled up the freon and went away.
Well, it was still starting very hard, with noises, and my husband removed the hard start. He began to check the voltage and wires and borrowed a pressure guage from a good friend who does this for a living. We thought is might be the high pressure shut off switch, but when we started it again last night with the guages on, the high pressue shot up for about a minute and then slowly came down and settled within its stated range. We sat by the outside unit watching it the entire time of course to shut it off at the switch outside if needed. Again, cooled just fine, but now we have seemed to eliminate the high pressure switch as being bad and we don't know what else to try. Our friend said he has never heard of a unti starting with such high pressure and then settling back down with no issues.
We are of course trying to avoid replacing this unit. It is a YORK, 12 years old, and installed by the builder when we bought this house new. It is a 5 ton unit as we have a dual zone system, which just means it has a damper in the attic unit that directs the flow from one side of the house to the other. Do you have any thoughts on what else to check, what to do, or do we just throw in the towel and buy a new unit? - T & L A, 7/11/2013
Some of this AC squealing and high pressure diagnosis you've gone thorugh is indeed a bit confusing; squealing compressor noise is not likely to be fixed by cleaning the coils - it's more like doing what one knows how to do regardless of the problem.
Typically a squeal means hard-starting which could be a bad compressor motor, bad start capacitor, or a compressor having trouble starting against a head pressure (try leaving the system off for 30 minutes and then re-starting). Similarly, just "adding freon" is not going to fix the problem - "to a carpenter every problem looks like a nail"
Watch out: I would NOT be messing with pressure checks even though you have a gauge; the problem is that without connecting the gauge set to a can of refrigerant and purging the gauge hoses and fittings you risk introducing air into the A/C sytem and messing up its charge or worse, introducing contaminants. You may be uncomfortable being candid, but you should certainly tell the HVAC tech what you've done so far, so that nobody rules out a messed-up or contaiminated refrigerant charge. Otherwise people could waste still more time and money by not guessing the complete history of the system.
Installing a hard start kit is the first line of attack many techs use as it's quick, easy, inexpensive. When that does not work, a more careful inspection and test of the unit controls, charge, voltage draw during startup, and similar steps are needed for an accurate diagnosis. I suggest calling your HVAC service company, talk calmly and without accusation (or they'll just go into defense mode) with the service manager, and ask him to send a senior, experienced technician out to test and diagnose your system. Also see the article beginning at the top of this page for some discussion about A/C noises and see http://inspectapedia.com/aircond/AC_Compressor_Hard_Start.htm on hard starting compressors.
Wow Wow WaWa or WuW sounds from an A/C or heat pump system
Please see Question Groaning Huffing - at Groaning, Huffing, wuwuwu sounds from A/C or heat pump system, diagnosis
Green link shows where you are in this article series.
Noise group 1 of 5 is below
Noise group 2 of 5 is below
Noise group 3 of 5 is below
Noise group 4 of 5 is below
Noise group 5 of 5 is below
Frequently Asked Questions (FAQs)
No FAQs have been posted for this page. Try the search box below or CONTACT US by email if you cannot find the answer you need at InspectApedia.
Use the search box below to ask a question or to search the InspectApedia.com website.
Ask a Question or Enter Search Terms in the InspectApedia search box just below.
Technical Reviewers & References
Related Topics, found near the top of this page suggest articles closely related to this one.