Question? Just ask us!
Free Encyclopedia of Building & Environmental Inspection, Testing, Diagnosis, Repair
InspectAPedia ® Home
AIR CONDITIONING & HEAT PUMP SYSTEMS
A/C - HEAT PUMP CONTROLS & SWITCHES
AIR CONDITIONER COMPONENT PARTS
AIR CONDITIONER TYPES, ENERGY SOURCES
AIR FILTER EFFICIENCY
AIR FILTERS, FIBERGLASS PARTICLES
AIR FLOW MEASUREMENT CFM
APPLIANCE EFFICIENCY RATINGS
BLOWER DOORS & AIR INFILTRATION
BLOWER FAN CONTINUOUS OPERATION
BLOWER FAN OPERATION & TESTING
BOOKSTORE - Air Conditioning "How To" Books
CAPACITORS for HARD STARTING MOTORS
CLEANING & Legionella BACTERIA
CHINESE DRYWALL HAZARDS
CONDENSATION or SWEATING PIPES, TANKS
DEFINITION of Heating & Cooling Terms
DEW POINT CALCULATION for WALLS
DEW POINT TABLE - CONDENSATION POINT GUIDE
DIAGNOSE & FIX AIR CONDITIONER / HEAT PUMP
DIAGNOSE & FIX HEATING PROBLEMS-BOILER
DIAGNOSE & FIX HEATING PROBLEMS-FURNACE
DUCTS - Asbestos
DUCT INSULATION, Asbestos Paper
DUCT INSULATION for SOUNDPROOFING
DUCT SYSTEM NOISES
DUCTS, Asbestos Transite Pipe
DUST, HVAC CONTAMINATION STUDY
ELECTRIC MOTOR OVERLOAD RESET SWITCH
EVAPORATIVE COOLING SYSTEMS
FAN LIMIT SWITCH
GAS EXPOSURE EFFECTS, TOXIC
GAS DETECTION INSTRUMENTS
HEAT LOSS (or GAIN) in buildings
HEAT LOSS (or GAIN) INDICATORS
HEAT LOSS R U & K VALUE CALCULATION
HEATING SMALL LOADS
INSPECTION CHECKLIST - OUTDOOR UNIT
INSPECTION LIMITATIONS, A/C SYSTEMS
LEED GREEN BUILDING CERTIFICATION
LOST COOLING CAPACITY
LOW VOLTAGE TRANSFORMER TEST
MOTOR OVERLOAD RESET SWITCH
MOLD in AIR HANDLERS & DUCT WORK
OPERATING COST, AIR CONDITIONER
OPERATING DEFECTS, AIR CONDITIONING
REPAIR GUIDE, AIR CONDITIONERS / HEAT PUMPS
REPAIR & DIAGNOSTIC FAQs for A/C
THERMOSTATS, HEATING / COOLING
THERMOSTATIC EXPANSION VALVES
WATER COOLED AIR CONDITIONERS
WINDOW / WALL AIR CONDITIONERS
WINDOW / WALL A/C SUPPORTS
Unsafe air ducts: this HVAC diagnosis & safety hazard article describes unsafe air conditioning or heating duct openings such as openings that may cause fatal production of carbon monoxide and move it into the occupied building space. We also discuss air or return duct openings that may pick up and distribute other gases, chemicals, mold or allergens throughout a building.
Green links show where you are. © Copyright 2013 InspectAPedia.com, All Rights Reserved. Author Daniel Friedman.
UNSAFE OPENINGS - Air Conditioning or Heating Duct System May Draw Dangerous Combustion Gases
Return air collected close to gas-fired appliance
Return Air Openings Near Heating Equipment
Flue gases from nearby heating or water heater appliances are easily drawn into the return air plenum and air handler. This would permit circulation of flue gases into the living area and can be a safety hazard which could deliver potentially fatal carbon monoxide to building occupants.
"Hidden" Duct or Air Handler Leaks
Here is an interesting case of a surprise air leak into the return air plenum at a gas-fired hot air furnace and air conditioning system. We removed the (not working) electrostatic air cleaner (first photo) to look into the return plenum where we saw a large gap between the return plenum and the blower compartment (second photo).
When the gas burner was operating along with the blower (in heating mode) this opening could certainly draw un-wanted gases into the duct system and might lead to CO production too. In cooling or air conditioning mode, the blower was pulling in air from the basement (where we had a mold concern).
Carbon Monoxide Production Caused by Improperly Located Return Air Ducts/Registers
Return air openings close to natural-draft fired appliances, again particularly gas, can also interfere with proper gas (and possibly oil) burner operation by competing for combustion air, thus causing carbon monoxide production when the burner is operating.
If openings are found in the duct system near fossil-fuel fired appliances it should be reported as an indication of a system operating problem (inadequate return air) and as a safety hazard (potentially fatal carbon monoxide poisoning). Review this potential hazard with a qualified service professional. For example, should a stack pipe fail and flue gas be dumped into the furnace room it would be picked up and distributed throughout the building.
Sample Air Conditioning Or Heating System Report Language for Unsafe Duct Openings
Sample inspection report language:
This item should be handled as soon as possible by an experienced and qualified heating professional - carbon monoxide poisoning is a potentially fatal safety concern.
Frequently Asked Questions (FAQs)
No FAQs have beenn posted for this topic. Try the search box below or CONTACT US by email if you cannot find the answer you need at InspectApedia.
Questions & answers or comments about HVAC air duct safety hazards.
Ask a Question or Enter Search Terms in the InspectApedia search box just below.
Technical Reviewers & References
Related Topics, found near the top of this page suggest articles closely related to this one.