InspectAPedia tolerates no conflicts of interest. We have no relationship with advertisers, products, or services discussed at this website.
Solid conductor aluminum branch circuit wiring in Residential Properties: Hazards & Remedies
This page may be freely distributed in print or electronic form and may be copied to other websites. Do not alter the content of this page without first contacting us for permission. InspectAPedia.com privacy and content use policies can be viewed at Accuracy & Privacy Policies. InspectAPedia.com is an independent publisher of building, environmental, and forensic inspection, diagnosis, and repair information for the public - we have no business nor financial connection with any manufacturer or service provider discussed at our website.
Aluminum electrical wiring, used in some homes from the mid 1960's to the early 1970's, is a potential fire hazard. According to the U.S. Consumer Product Safety Commission, fires and even deaths have been reported to have been caused by this hazard. Problems due to expansion can cause overheating at connections between the wire and devices (switches and outlets) or at splices.
CPSC research shows that "homes wired with aluminum wire manufactured before 1972 are 55 times more likely to have one or more connections reach "Fire Hazard Conditions" than are homes wired with copper.
"Post 1972" aluminum wire is also a concern. Introduction of the aluminum wire "alloys" in 1972 time frame did not solve most of the connection failure problems. Aluminum wiring is still permitted and used for certain applications, including residential service entrance wiring and single-purpose higher amperage circuits such as 240V air conditioning or electric range circuits.
As of the current date of this page, only two remedies (1 - Discontinued Use and 2.1.- COPALUM, below) have been recommended by the CPSC.
The pigtail connection must be made using
COPY PERMISSION: Readers are welcome to copy and place this ALUMINUM WIRIING SUMMARY free to copy page at their website or to make printed copies to give to others at no charge as long as this document is not modified in any form.
02/10/2013 - 04/01/1988 - http://inspectapedia.com/aluminum/Aluminum_Wiring_Summary.html - © 2014 - 1988 Copyright Daniel Friedman All Rights Reserved - InspectAPedia® is a Registered U.S. Trademark - This page may be copied to other websites as long as it is not modified. This page may be freely printed and distributed as long as it is done so without charge and as long as it is not used to endorse or sell a particular product or service.