Question? Just ask us!
Free Encyclopedia of Building & Environmental Inspection, Testing, Diagnosis, Repair
InspectAPedia ® Home
ELECTRICAL INSPECTION, DIAGNOSIS, REPAIR
AFCIs ARC FAULT CIRCUIT INTERRUPTERS
ALUMINUM WIRING HAZARDS & REPAIRS
AMPS VOLTS DETERMINATION
AMPERAGE MEASUREMENT METHODS
APPLIANCE EFFICIENCY RATINGS
BACKUP ELECTRICAL GENERATORS
BACK-WIRED ELECTRICAL DEVICES
BOOKSTORE - ELECTRICAL
Cadet & Encore Heater Recall
CIRCUIT BREAKER SIZE for A/C or HEAT PUMP
Classified CIRCUIT BREAKER WARNING
CUTLER HAMMER PANEL FIRE
CORROSION in ELECTRICAL PANELS
DEFINITIONS of ELECTRICAL TERMS
DIRECTORY OF ELECTRICIANS
DMM Digital Multimeter HOW TO USE
ELECTRIC METERS & METER BASES
ELECTRIC MOTOR DIAGNOSTIC GUIDE
ELECTRIC MOTOR OVERLOAD RESET SWITCH
ELECTRIC PANEL AMPACITY
ELECTRIC PANEL INSPECTION
ELECTRIC PANEL MOISTURE
Electric Power Frequency Table
EMF RF FIELD & FREQUENCY DEFINITIONS
ELECTRICAL GROUND SYSTEM INSPECTION
ELECTRICAL SERVICE DROP
ELECTRICAL SERVICE ENTRY WIRING
EMF RF FIELD & FREQUENCY DEFINITIONS
FIRE SAFETY Checklist, CPSC
GFCI PROTECTION,Testing GFCIs AFCIs
HEATING COST FUEL & BTU Cost Table
HEAT TAPE USAGE GUIDE
Hertz - Definitions of KHz MHz GHz THz
KNOB & TUBE WIRING
LIGHTING, EXTERIOR GUIDE
LIGHTING, INTERIOR GUIDE
LIGHTNING PROTECTION SYSTEMS
LOW VOLTAGE BUILDING WIRING
LOW VOLTAGE TRANSFORMER TEST
MAIN ELECTRICAL DISCONNECT
MAIN DISCONNECT AMPACITY
MOISTURE SOURCES in PANELS
MURRAY SIEMENS Recall
PHOTOVOLTAIC POWER SYSTEMS
PUSHMATIC - BULLDOG PANELS
REMOTE ELECTRIC POWER, PHOTOVOLTAIC
RUST in ELECTRICAL PANELS
SAFETY for ELECTRICAL INSPECTORS
SE CABLE SIZES vs AMPS
SIEMENS MURRAY Recall
THERMAL EXPANSION of HOT WATER
THERMAL EXPANSION of MATERIALS
UNDERGROUND SERVICE LATERALS
VOLTS / AMPS MEASUREMENT EQUIP
VOLTAGE MEASUREMENT METHODS
WIND TURBINES & LIGHTNING
ZINSCO SYLVANIA ELECTRICAL PANELS
Copper-Clad Aluminum Elecrical Wiring: this article describes the history of copper-clad aluminum electrical wiring and its safe use in homes in the United States.
Green links show where you are. © Copyright 2014 InspectApedia.com, All Rights Reserved.
Thomas J. D'Agostino, P.E., C.I., & Daniel Friedman
What is copper-clad aluminum wire?
Copper-clad aluminum wire is made of a solid aluminum core covered with a copper skin in order to improve its performance in the field. This produc was installed in homes in the United States between 1972 and 1975. Details are provided by Tom D'Agostino:
I would not assume that copper-clad AL wire might not appear in an older home in which electrical wiring was added or changed during that same interval, and it's also possible, though less likely, that copper clad aluminum wire might appear in new home built after 1975 if an electrician had and wished to use up old copper-clad aluminum wire stock.
[Illustrations needed, CONTACT us]
Is copper-clad aluminum wire safe to leave in place?
Yes. Copper-clad aluminum electrical wire is described in REDUCE THE AL WIRE RISK: DETAILS, as well as in Aronstein (2011). There Aronstein states
How to identify copper-clad aluminum wire
Recognizing that electrical wire is copper clad aluminum is useful for technical reasons.
[Illustrations needed, CONTACT us]
Externally, if we eschew noticing printed labels and marking that may be present on copper clad aluminum wire, and if we simply look at the wire itself, stripped of insulation, the wire looks like a copper. However if we can take a closer look at a relatively square-cut end of the wire we should see an aluminum core surrounded by a copper skin. Without disassembly and possibly even careful cutting of the end of the wire this detail may not be easily visible, since typical wire nippers compress the end of the wire when making a cut.
Scraping copper clad aluminum wire may not be adquate to identify its silver-colored aluminum core unless the scrape is vigorous enough to cut completely through the copper cladding.
Below is a cross-section cut of a solid aluminum electrical wire (with white insulation) and a solid copper aluminum conductor (with black insulation).
History of Copper Clad Aluminum Electrical Wiring
[Click to enlarge any image]
Early work by Carlson (shown at left) described a process "inside-out" of the later copper-clad aluminum wire. That is, Carlson's patent described applying an an aluminum sheath as the exterior of a copper core. Significant was that the metallic sheath was "metallurgically bonded to the inner core".
Illustrated at above left is the production method for cladding one metal with another to produce a wire of one metal with a cladding of another metal. - Carlson et als. (1963).
Dion (1966) and Dion and Thompson (1967) first described the successful manufacture of copper clad aluminum wire. Rolled aluminum wire is pulled through a lubricated draw to eliminate flat spots and to prepare the wire surface for a solid-bonding phase in which two copper cladding strips are added tothe wire exterior.
Illustrated at left is Dion's method of cladding aluminum wire with a layer of copper. It is significant to note that the copper thickness in this method is much greater than the typical thickness imparted by plating one metal on another. It is likely that it's that thickness that prevents a device connector srcew from cutting through the copper, possibly leading to connector failures in field use.
Continuing by quotation:
Later work described by Ziemek (1974) reversed this process, placing the copper as the outer sheath and solid aluminum as the interior or main body of the wire.
Quoting from a later description of this process, a copper band is formed around an aluminum core wire and the single seam in the sheath material is welded without bonding of the sheath and core, care being taken that all surfaces are clean and maintained free of oxides. - Ziemek (1974)
Mr. D'Agostino relates that in 1971 as project engineer at UL, he conducted tests evaluating the performance of copper-clad aluminum conductor wiring using a number of types of copper-only receptacles (i.e. binding head screw terminals, back-wired terminals, pressure plate screw terminals) and a number of types of AL-CU pressure wire connectors. That research, conducted under the auspices of U.L., demonstrated that performance of copper-clad wire was
The findings of this research was published in a 1971 UL bulletin that was distributed / reviewed by industry and government (i.e. David Rabinov of theU.S. National Bureau of Standards).
The copper clad aluminum wire product produced by Texas Instruments is attributed by D'Agostino to John Fan (see patent citations below). Following successful testing by D'Agostino at U.L., copper-clad alulminum wiring was reognize by UL/Industry and soon thereafter UL Listed NM Sheathed Cable with Nos. 10-12 AWG solid copper-clad aluminum conductor was distributed and installed in homes in the United States (and possibly Canada) between 1972 and 1975.
Original patents on the production of copper-clad aluminum wire were awarded to a variety of parties (cited below) with early patent applications in 1956 (Carlson) and key patents (Carlson, Roserans, Westinghouse Electric) dating from 1963.
Research into the production and use of copper-clad aluminu wire continues to the present, with work by Kwon (2004) and Rhee (2004) and others on fabrication methods and by Sasaki (2010) on the metallurgy of copper-clad aluminum.
- Special thanks to Tom D'Agostino for recapping the history of aluminum electrical wiring and copper clad aluminum electrical wiring. Personal communication 5/3/2014. Mr. D'Agostino presently lives on Long Island, NY. and continues to write and research electrical hazards. He has also worked as a professional home inspector and is a member of ASHI, the Amerian Society of Home Inspectors.
At above left, even without any disassembly we can see a solid conductor aluminum wire (center breaker connection) double-tapped (two wires under one connector) into a circuit breaker along with a silver-colored solid conductor electrical wire that is probably aluminum wire. (The large multi-strand red-insulated wire is a multi-strand aluminum conductor.)
Double-tapping electrical wire connections is improper and unsafe unless the connector is specifically designed for that purpose and is so-indicated by its manufacturer.
But from just this photograph alone one cannot be sure if the silver colored wire is aluminum or plated copper.
Note: Tin plated copper wire was generally a practice used before 1965 on small-sized 14-12 copper wire. On second look, the size of the silver-colored black insulated wire shown above is likely to be a size 10 or 12 AWG aluminum. Further, tin-plated copper presents a "dirty silver" look. - D'Agostino (2014)
A closer look will be needed to confirm the opinions of our note above. Notice that the circuit breaker is marked CU-AL indicating that the manufacturer represented that the breaker could be used with either aluminum or copper wire, notwithstanding that this is not an accepted nor recommened repair for aluminum electrical wiring.
Watch out: In addition to the improper double-tapping in the center circuit breaker shown above, copper wire in contact with an aluminum conductor in an AL-CU rated circuit breaker is not covered by the UL-listing. The device is listed for use with either copper-only or aluminum only.
Details are at ALUMINUM WIRING REPAIR COALR & CU-AL.
We can see silver-colored (soft) metal that is aluminum at three locations:
Watch out: plated copper wire is a completely different product that, because its conductors sport a thin plated silver colored surface, might be mistaken for unsafe alumium wire. It is not aluminum and it is safe unless, as with any electrical wiring, it has been damaged in some manner.
Not all rubber insulated copper wire is plated, but if you suspect that the silvery-colored wire is plated copper, it's easy enough to determine: with the wire disconnected from any power source, scratch the silver colored surface of the rubber-insulated wire and you'll see its red copper interior.
In REDUCE THE AL WIRE RISK: DETAILS, as well as in Aronstein (2011). There Aronstein describes plated-copper wire as:
Above we show solid aluminum conductor wire and solid copper conductor electrical wire in cross section.
Watch out: don't confuse references to copper-clad aluminum wire or copper-plated electrical wire with devices such as electrical receptacles and switches marked COALR or CU-AL. The latter two are device labels not wire types and are not a recommended repair for aluminum electrical wire. COALR and CU-AL and their field performance and safety warnings are described in more detail at ALUMINUM WIRING REPAIR COALR & CU-AL
Contact the authors
References for copper clad aluminum wire & related research
Suggested citation for this web page
Green link shows where you are in this article series.
The link just above provides access to Reducing the Fire Hazards in Aluminum-Wired Homes, by Dr. Jess Aronstein, Ph.D., This document answers most technical questions about the hazards and remedies of aluminum electrical wiring.
Frequently Asked Questions (FAQs)
No FAQs have been posted for this page. Try the search box below or CONTACT US by email if you cannot find the answer you need at InspectApedia.
Check the FAQs just above, try the search box just below, or if you prefer, post a question or comment in the Comments box below and we will respond promptly.
Search the InspectApedia website
HTML Comment Box is loading comments...
Technical Reviewers & References
Related Topics, found near the top of this page suggest articles closely related to this one.