Question? Just ask us!
Free Encyclopedia of Building & Environmental Inspection, Testing, Diagnosis, Repair
InspectAPedia ® Home
ELECTRICAL INSPECTION, DIAGNOSIS, REPAIR
ALUMINUM WIRING HAZARDS & REPAIRS
Aluminum Wiring Summary Page for Public Use
BUILDING SAFETY HAZARDS GUIDE
BOOKSTORE - ELECTRICAL
Cadet & Encore Heater Recall
CIRCUIT BREAKER FAILURE
Classified CIRCUIT BREAKER WARNING
CUTLER HAMMER PANEL FIRE
DEFINITIONS of ELECTRICAL TERMS
DMM Digital Multimeter HOW TO USE
ELECTRIC PANEL INSPECTION
ELECTRICAL GROUND SYSTEM INSPECTION
FIRE SAFETY Checklist, CPSC
GFCI PROTECTION,Testing GFCIs AFCIs
KNOB & TUBE WIRING
LIGHTNING PROTECTION SYSTEMS
LOW VOLTAGE BUILDING WIRING
MURRAY SIEMENS Recall
PUSHMATIC - BULLDOG PANELS
RUST in ELECTRICAL PANELS
SAFETY for ELECTRICAL INSPECTORS
SIEMENS MURRAY Recall
VOLTS / AMPS MEASUREMENT EQUIP
VOLTAGE MEASUREMENT METHODS
ZINSCO / SYLVANIA HAZARDS
History of the Ideal No. 65 twist-on connector usage debate regarding aluminum wiring: this document provides opinions, conclusions, and links to public documents outlining the history of debate and research concerning use of the Ideal #65 Twister™, a twist-on connector listed by UL and marketed by Ideal Corporation as a retrofit product for aluminum wiring.
Green links show where you are. © Copyright 2014 InspectApedia.com, All Rights Reserved.
10/04/1999 Independent Research report to IEEE Holm Conference of a study of more than 4,531 of these connectors used in 102 apartments indicates that significant field failures occurred and were attributable to the connector itself, not to installation practices nor to any unusual condition of the aluminum branch circuit wiring.
07/10/1998 CPSC Against Twist-On Aluminum Wire Connectors documents the US CPSC position on the use of twist-on connectors for aluminum wiring repairs
10/20/1997 Independent Research report to IEEE Holm Conference indicates splices using this connector are not capable of long term safe performance as part of the permanent wiring of existing aluminum-wired homes.
9/10/1997 Field failures of this device in actual service have now been reported.
3/29/1996 Independent Tests indicate Ideal-65 purple Twist-on retrofit connector fails UL 486C Safety Standard despite its UL-listing
1/311996 Ideal Corporation has indicated they're sending us additional information. 5/96 note: received, not posted. Reply contained no information except asserts no reported problems.
1/31996 Fire Hazards With Aluminum to Copper Twist-on Connectors & Acceptable Repair Practices Color Photos, Alternative Retrofit/Repair Procedures, Current Issues. From the 9/28/95 CPSC Meeting Minutes.
9/28/1995: AL-Rated Twist-On Connector Debate Continues: At a second meeting at CPSC HQ on 9/28/95, attended by the manufacturer, CPSC, UL, the author, and other professionals we learned that the manufacturer has responded to some of the CPSC concerns. That information, along with information from UL is forthcoming in the meeting log.
Ideal's marketing literature which we received and which opens with "Retrofitting Aluminum Wire Used To Be A Can of Worms"..."Not Any More!" should not be taken literally to mean that this is a general retrofit product.
At the 9/2819/95 meeting at the US CPSC in Washington, D.C., the manufacturer clarified that while their new twist-on connector has been listed under UL486C, this device is not intended for general aluminum wiring retrofit. The new connector is intended for limited special applications involving (only) certain aluminum-to-copper splices such as the addition of a new device (e.g. ceiling fan) to a house wired with aluminum. The manufacturer is reviewing its marketing and instructional literature in order to clarify the intended use.
6/1/1995: Twist-on connectors (wire nuts) have not been recommended (by the CPSC) for permanent repair of aluminum wire electrical circuits. To date, this includes recently-released twist-on connectors manufactured by Ideal Industries and available in some markets. While Underwriters Laboratories has listed these new twist-on's, at a meeting with the CPSC on 1 June,1995, a number of CPSC concerns were reviewed with UL and with the device manufacturer. As a result, additional research was being performed.
6/1/1995 CPSC, UL, Ideal Corp, Meeting Log 6/1/95 documenting UL-CPSC agreements for report exchange and additional testing of twist-on connectors for aluminum retrofit
5/1/1995 CPSC Letter Aluminum Wiring Connectors letter to UL documents concerns with twist-on connectors for aluminum wire retrofit
Conclusions & Opinions
08/03/2010: The results of independent testing and studies of both field use and laboratory testing of aluminum electrical wiring repairs using this twist-on connector and using materials and connections such as found in homes wired with aluminum wiring indicate that the Ideal #65™ does not meet the UL Standard UL486C even though the connector is UL listed for those wire combinations.
Our interpretation of this result is that there are possible fire hazards using this connector for general retrofit of aluminum wiring, and we advise against its recommendation or use in this manner. Consumers and building professionals should watch for any CPSC update of their current position: The US Consumer Product Safety Commission (CPSC) does not recommend use of this connector for retrofit of aluminum-wired homes.
1/31/1996: Previous position: We view the CPSC and independent consultant's concerns as serious, and have some additional opinions based on field experience. The CPSC is waiting for additional information before deciding on any recommendations or actions.
We advise consumers, electricians, and building inspectors to wait for follow up information from the CPSC or other authorities before recommending this new product to their clients. Any new information we receive will be posted here promptly.
Despite some recent misunderstandings to the contrary, ASHI, the American Society of Home Inspectors does not approve nor recommend products, including this one, but does provide information for building professionals and consumers on this and other topics.
More Information - Detection, Repair, Advice for Aluminum Wiring in buildings
"Analysis of field failures of aluminum-copper pigtail splices made with twist-on connectors",
Comments: In 1997 a licensed electrician was contracted to replace all aluminum branch wiring in a 1968 residential apartment building used CO/ALR type devices to replace existing devices; the electrician "pigtailed" (aluminum spliced to copper conductor pigtails) heavily loaded branch circuits using a recently-introduced twist-on connector rated for that purpose. Independent testing (see Evaluation of a Twist-on Connector for Aluminum Wire", J. Aronstein, below) had previously demonstrated significant weaknesses of this connector. Other aluminum to copper splices using this connector involved connections to copper wire leads of lighting fixtures, HVAC equipment, and appliances.
Electrical failures were noted within the first year after these repairs had been made, detected by smell or device malfunction. Infra-red temperature measurements showed abnormal heating of other splices. By the end of 1998 these conditions had led to replacement of all of the newly-made twist-on splices, this time using the COPALUM connector recommended by the US CPSC for this application. During replacement, additional examples of overheating were discovered.
All of the 4,531 removed connectors that had been installed in 102 apartments were retained and provided to Dr. Aronstein for further study. The results were published in the 1999 IEEE paper cited above. Aronstein did not find evidence of improper installation of the devices, and study of the aluminum wire itself for abnormalities (such as abnormal levels of oxide film on wire surfaces leading to higher wire-to-wire resistance in the splices) did not find that abnormal wire conditions were a factor in the failures.
These studies left the failures to be attributed to the devices themselves, by components and mechanisms within the device as Aronstein explains in detail in the paper. This article describes the field results and testing of a twist on connector produced by Ideal Industries, Ideal#65 purple "Twister"™ twist-on connector listed and sold as a repair/retrofit for residential aluminum wiring.
"Evaluation of a twist-on connector for aluminum wire",
Poughkeepsie, NY, USA;
Based on the test
results, it is concluded that this connector has not overcome the fundamental deficiency of twist-on connectors for use with aluminum wire, and is not considered to be suitable for permanent splices in residential aluminum wire applications
Frequently Asked Questions (FAQs)
No FAQs have been posted for this page. Try the search box below or CONTACT US by email if you cannot find the answer you need at InspectApedia.
Try the search box just below or if you prefer, post a question or a comment in the Comments box below and we will respond promptly.
Search the InspectApedia website
HTML Comment Box is loading comments...
Technical Reviewers & References
Related Topics, found near the top of this page suggest articles closely related to this one.