Question? Just ask us!
Free Encyclopedia of Building & Environmental Inspection, Testing, Diagnosis, Repair
InspectAPedia ® Home
ELECTRICAL INSPECTION, DIAGNOSIS, REPAIR
ALUMINUM WIRING HAZARDS & REPAIRS
Aluminum Wiring Summary Page for Public Use
BUILDING SAFETY HAZARDS GUIDE
BOOKSTORE - ELECTRICAL
Cadet & Encore Heater Recall
CIRCUIT BREAKER FAILURE
Classified CIRCUIT BREAKER WARNING
CUTLER HAMMER PANEL FIRE
DEFINITIONS of ELECTRICAL TERMS
DMM Digital Multimeter HOW TO USE
ELECTRIC PANEL INSPECTION
ELECTRICAL GROUND SYSTEM INSPECTION
FIRE SAFETY Checklist, CPSC
GFCI PROTECTION,Testing GFCIs AFCIs
KNOB & TUBE WIRING
LIGHTNING PROTECTION SYSTEMS
LOW VOLTAGE BUILDING WIRING
MURRAY SIEMENS Recall
PUSHMATIC - BULLDOG PANELS
RUST in ELECTRICAL PANELS
SAFETY for ELECTRICAL INSPECTORS
SIEMENS MURRAY Recall
VOLTS / AMPS MEASUREMENT EQUIP
VOLTAGE MEASUREMENT METHODS
ZINSCO / SYLVANIA HAZARDS
This article describes a working alternative repair method for aluminum wiring [- Superceded by new alternate repair as of June 2007] but documented here as an aid to recognizing the occurrence of this repair method in existing installations.
Green links show where you are. © Copyright 2014 InspectApedia.com, All Rights Reserved.
Alternative Aluminum Wire Repair Method Using the Scotchlok 3-M Connector & Special Details [obsolete]
The availability of the AlumiConn beginning in July 2007, a UL listed connector intended for this repair and which was tested successfully, resulted in our statement that the alternative method described here has been supersceded by a new alternative repair.
We have maintained this [now obsolete] repair description to aid in recognition of this repair in buildings where it may have been applied. Original quote:
This repair was considered appropriate for cases where the AMP TYCO COPLAUM connector method and electricians trained to use that method were not available.
How to Apply a Special Aluminum Wire Repair Method For Use When the COPALUM Method is Not Available [Obsolete as of June 2011]
For in-depth discussion of the procedures described below also see Reducing the Fire Hazard in Aluminum-Wired Homes by Dr. Jesse Aronstein.
Click any image to see an enlarged version.
This is Aluminum Wiring Repair Procedure - Page 12 Color photos and descriptive captions from a CPSC Meeting held on 9/28/95. This presentation describes an alternative repair method for aluminum wiring which was at that time considered useful where the AMP TYCO COPALUM special connector and electricians trained to use it were not available.
This alternative repair for aluminum electrical wiring used readily-available components. It was tested and found reliable when performed by a properly trained licensed electrician or similarly qualified expert. As with any electrical wiring repair, but perhaps even more important in this case where the starting point is unsafe aluminum electrical wiring, it was essential that the repair procedure was correctly performed.
This document presents color photos and descriptive captions from the CPSC Meeting on 9/28/95 where this aluminum wiring repair method was described. In this document aluminum wire twist-on connector failures and repair procedures are described, including aluminum wire repair methods which work and methods which do not work and are unsafe. Color photos of aluminum wire repair procedures, and photos of failed connectors are included.
This document series describes hazards with existing aluminum wiring repair products, explains the aluminum wiring failure mechanism, and reviews recommended retrofit procedures including use of readily-available materials. This information was presented to the US Consumer Product Safety Commission by Dr. J. Aronstein, 9/28/95.
The US CPSC minutes were obtained under the Freedom of Information Act and posted by Daniel Friedman January 1996, updated June 2007 to reflect
the availability of a new alternative to the COPALUM, the AlumiConn, and noting that the use of the Scotchlok 3-M method described here is - superceded by new alternate repair as of June 2007.
35. Unfortunately, however, the COPALUM repair is not readily available in some areas of the country, and is impractical if there is only need to connect a single fixture or appliance. Some twist-on
connectors may work well as an alternative, providing that they are installed in a special manner - superceded by new alternate repair as of June 2007.
Orrey W. Hiebert was kind enough to suggest another inhibitor: Burndy Pentrox A which he says does not ignite. These compounds are available from most electrical wholesale suppliers.
version of De-Ox by Ilsco, a gel that comes in a white squeeze bottle, is reported by some of our readers to no longer support combustion.
[Email from G.S to DJF 11/16/06)].
38. Other brands, including the one, NOALOX(TM) made by Ideal and used in their #65 connector, ignite readily and burn vigorously.
There is substantially better mechanical and electrical wire-to-wire contact in this pre-twisted splice than can be achieved by simply screwing the connector
onto the straight wires.
The connector that has been found to work well for aluminum and aluminum-copper splices (3M Scotchlok, available from most electrical wholesalers) has several features that make it intrinsically safer than the Ideal #65, including a non-flaming shell, a metal shell around the spring, and heavier spring wire.
The 3M "Scotchlok" connectors are generally available in four sizes, designated
on the box (of 100) as product model "Y", "R", "G", or "B" (in increasing order
of size). The model designation corresponds to the color of the insulating shell
(yellow, red, green, or blue). The "R" and "G" are the most useful sizes for
aluminum wire pigtailing of the #12 and #10 wire (15 and 20 amp circuits,
Other brands and types may be OK. The key factors are:
"live spring" design, non-flaming shell, heavy spring cross section, and non-steel spring if available.
Frequently Asked Questions (FAQs)
No FAQs have been posted for this page. Try the search box below or CONTACT US by email if you cannot find the answer you need at InspectApedia.
Questions & answers or comments about use of the Scotchlok-3M twist on connector for aluminum wiring repairs.
Try the search box just below or if you prefer, post a question or a comment in the Comments box below and we will respond promptly.
Search the InspectApedia website
HTML Comment Box is loading comments...
Technical Reviewers & References
Related Topics, found near the top of this page suggest articles closely related to this one.