Question? Just ask us!
Free Encyclopedia of Building & Environmental Inspection, Testing, Diagnosis, Repair
InspectAPedia ® Home
ELECTRICAL INSPECTION, DIAGNOSIS, REPAIR
ALUMINUM WIRING HAZARDS & REPAIRS
Aluminum Wiring Summary Page for Public Use
BUILDING SAFETY HAZARDS GUIDE
BOOKSTORE - ELECTRICAL
Cadet & Encore Heater Recall
CIRCUIT BREAKER FAILURE
Classified CIRCUIT BREAKER WARNING
CUTLER HAMMER PANEL FIRE
DEFINITIONS of ELECTRICAL TERMS
DMM Digital Multimeter HOW TO USE
ELECTRIC PANEL INSPECTION
ELECTRICAL GROUND SYSTEM INSPECTION
FIRE SAFETY Checklist, CPSC
GFCI PROTECTION,Testing GFCIs AFCIs
KNOB & TUBE WIRING
LIGHTNING PROTECTION SYSTEMS
LOW VOLTAGE BUILDING WIRING
MURRAY SIEMENS Recall
PUSHMATIC - BULLDOG PANELS
RUST in ELECTRICAL PANELS
SAFETY for ELECTRICAL INSPECTORS
SIEMENS MURRAY Recall
VOLTS / AMPS MEASUREMENT EQUIP
VOLTAGE MEASUREMENT METHODS
ZINSCO / SYLVANIA HAZARDS
This article discusses special problems with the combustibility of antioxidant and plastic used in the Ideal 65 Twist-on purple "twister" connector if used for splicing aluminum to copper wires.
Green links show where you are. © Copyright 2014 InspectApedia.com, All Rights Reserved.
Description of Aluminum Wiring Twist-on Connector Failures: combustible connector shell & combustible antioxidants
This is Aluminum Wiring Repair Procedure - Page 13 Color photos and descriptive captions from CPSC Meeting 9/28/95. In this document aluminum wire twist-on connector failures and repair procedures are described, including aluminum wire repair methods which work and methods which do not work and are unsafe. Color photos of aluminum wire repair procedures, and photos of failed connectors are included.
This document series describes hazards with existing aluminum wiring repair products, explains the aluminum wiring failure mechanism,
and reviews recommended retrofit procedures including use of readily-available materials.
This information was presented to the US Consumer Product Safety Commission by Dr. J. Aronstein, 9/28/95.
The minutes of that meeting were obtained under the Freedom of Information Act and posted by Daniel Friedman January 1996.
50. Installed per the manufacturer's instructions, many in retrofit installations, hazardous failures will occur in considerable numbers over the years. The free-burning connector shell
is then a cause for concern. A substantial fire can grow from ignition of a connector shell, as shown in this demonstration.
Frequently Asked Questions (FAQs)
No FAQs have been posted for this page. Try the search box below or CONTACT US by email if you cannot find the answer you need at InspectApedia.
Questions & answers or comments about aluminum wire repair twist on connector shell and antioxidant inhibitor paste that catch fire.
Check the FAQs just above, try the search box just below, or if you prefer, post a question or comment in the Comments box below and we will respond promptly.
Search the InspectApedia website
HTML Comment Box is loading comments...
Technical Reviewers & References
Related Topics, found near the top of this page suggest articles closely related to this one.