Question? Just ask us!
Free Encyclopedia of Building & Environmental Inspection, Testing, Diagnosis, Repair
InspectAPedia ® Home
CHIMNEY INSPECTION DIAGNOSIS REPAIR
BACKDRAFTING HEATING EQUIPMENT
CARBON MONOXIDE - CO
CHIMNEY CAP & CROWN
CHIMNEY CLEANING PROCEDURES
CHIMNEY COMPONENT DEFINITIONS
CHIMNEY CRACK DETECTION & DIAGNOSIS
CHIMNEY DRAFT & PERFORMANCE
CHIMNEY FIRE ACTION / PREVENTION
CHIMNEY HEIGHT & CLEARANCE CODE
CHIMNEY INSPECTION, FLUE INTERIOR
CHIMNEY LEANING, SEPARATION, MOVEMENT
CHIMNEY REPAIR METHODS
CHIMNEY STAINS & LEAKS
CHIMNEY TYPES & MATERIALS
DIRECT VENTS / SIDE WALL VENTS
DRAFT REGULATORS, DAMPERS, BOOSTERS
FIRE CLEARANCES INDOORS
FIREPLACES & HEARTHS
FLUE VENT CONNECTORS
MASONRY CHIMNEY GUIDE
METAL CHIMNEYS & FLUES
SAFETY RECALLS CHIMNEYS VENTS HEATERS
SOOT AT CHIMNEY TOP
STAIN DIAGNOSIS on BUILDING EXTERIORS
WOOD, COAL STOVES & FIREPLACES
Chimney cleanout doors & openings: this article describes chimney cleanout access doors or ports. We explain that in addition to using the chimney cleanout as a service port to remove debris that has fallen to the bottom of a masonry chimney, the cleanout door and the type of debris found inside can tell us something about the condition of the chimney flue even though we cannot see most of it.
These articles on chimneys and chimney safety provide detailed suggestions describing how to perform a thorough visual inspection of chimneys for safety and other defects. Chimney inspection methods and chimney repair methods are also discussed.
Green links show where you are. © Copyright 2014 InspectApedia.com, All Rights Reserved.
Where you can find a chimney cleanout or can remove a flue vent connector to look into a flue, use of a mirror inside the flue to view the flue from below.
[Click to enlarge any image]
This is by no means a thorough and accurate view of all of the chimney flue interior. But if the chimney was constructed as a straight flue up through the building roof, you should see daylight - otherwise the flue has become blocked, perhaps with nesting animals or collapsing debris.
Our photo (left) will provide an easy view into this section of the chimney flue. But even before opening the chimney cleanout door we can see that there has been a history of leaks inside of the chimney flue.Masonry Flues & Clay Tile Lined Flues: If you open a chimney cleanout-door or pull the flue vent connector from a dead end chimney flue, in either case you are looking at the very bottom of the chimney flue. If you are inspecting a masonry chimney, be alert for discovery of masonry fragments when inspecting or cleaning the bottom of the flue.
If a piece of brick, masonry block, concrete, or clay flue tile liner is pulled out of your chimney, ask "where do you suppose this came from?" If the masonry scrap fell during construction of the chimney it may mean nothing.
But if it fell because the chimney has been damaged, perhaps by water, frost, or during cleaning, then you probably have an unsafe chimney flue - more investigation is in order, promptly.
Certainly if you believe that the masonry scrap found at the bottom of a flue fell during original construction, and if you remove it during cleaning, you should never find another piece in the flue bottom.
If you do, the flue has been damaged anew and it is unsafe
Our photo shows normal chimney creosote and debris at the bottom of a flue. When removing this material be alert for surprises such as fragments of clay flue tile liner.
All chimneys must have a cleanout at least 12" below the lowest appliance inlet opening. A fireplace is considered as access for cleaning. Cleanouts must have metal or pre cast concrete doors that can be secured tightly
In the photo at above left, the chimney cleanout is easy to find and the door is in place and closed; look inside for clues of flue damage and also for the presence of a flue liner if this is a single-brick wythe flue.
In the photo at above right the home made cleanout door was a metal scrap propped against the chimney. It has fallen open, and we see some masonry debris that has fallen down the flue.
Chimney cleanout door left open
We found this chimney cleanout door (shown above) ajar. Failure to close the chimney cleanout door can result in a fire and will certainly interfere with good draft in the flue.
This chimney cleanout access port served a common ash dump below both a fireplace flue and a separate heating appliance chimney flue.
Water leaks through the chimney cleanout port
We found this chimney cleanout pouring water into the building basement during a heavy rainstorm.
See CHIMNEY CAP & CROWN for chimney top sources of water leakage.
But in the case of the water leak shown our photo most likely the water source is from roof spillage onto the ground or surface runoff on the ground around the chimney base.
A combination of in-slope grade around the chimney base and leaks into the chimney can be detected by noticing water or creosote leak stains around the chimney cleanout opening even if you don't have the good luck to catch water in the act of entering the building.
ur photo above illustrates this condition - brown rust and creosote stains below the cleanout access opening. This chimney and its rain cap and cap seal need further inspection as may the flue itself.
Watch out: water damage to a chimney flue may leave the chimney unsafe.
Combustibles Stuffed in Chimney Opening
Using a one-gallon plastic bottle (photo below) as a means of sealing off a chimney cleanout opening (photo at left, Poughkeepsie, NY) is nothing less than stupid.
The fire hazard is greater below a fireplace where burning embers may fall into the cleanout pit, but this expedient is not recommended in any case.
Do not use a combustible material in the construction of chimneys or flues.
If the chimney cleanout access door is blocked such as by an installed appliance (a water heater in our photo at left) how is someone going to access the flue for inspection or cleanout?
Wait a minute? What's that sitting on the horizontal surface at the top of our photo?
Has an abandoned chimney been partly removed? It is possible that this is an offset access into a common ash pit.
In some constructions multiple chimney flues may terminate in a single large ash pit with one or more individual cleanout doors.
We suspect that this is an improper design, making regulation of draft among the chimneys difficult, since any individual flue that begins to draw may pull air down and into itself from a neighbor
Home made chimney cleanout door closures
If the chimney cleanout door is closed using a permanently-mounted component such as shown in our photo you've got a clue that work was not done by a professional.
This chimney cleanout closure may be fireproof (really?) and it may stop a draft problem, but it violates the readily-accessible and operable chimney cleanout door requirement.
Even a factory-built insulated metal chimney needs to include a cleanout access port.
Here, shown during installation, you can see that this metal chimney includes a removable cleanout door at the bottom of the tee used to turn from horizontal to vertical in the chimney run.
This photo of a metal chimney cleanout port was taken during construction - the required drywall (and an access cover through the drywall if the chimney is enclosed) were not yet installed.
Watch out: opening a cleanout at the bottom of a vertical chimney run like this can spill a horrible mess of ash and debris - be prepared, or better, if the horizontal run to the tee is short, vacuum and clean the chimney first through the horizontal chimney run. - Photo courtesy Galow Homes.
Openings at the chimney base around the cleanout door
In this photo (left) the chimney cleanout is easy to find but isn't that door missing? No not in the first photo at left of this pair of photographs of chimney cleanout doors.
But look carefully at the second photo. Even though a cleanout door is installed, masonry has fallen out above the door, giving an opening right into the flue.
A missing chimney cleanout door or any other hole in the flue means that there is a fire safety hazard (sparks or ashes falling out onto the basement floor) and also that it is impossible to control the draft in the flue.
Watch out: Where the hole in a chimney is lower than or below the flue vent connector joining the heating appliance to the flue, there is also a serious problem with draft control as well as the risk of sparks or embers falling out of the flue into the interior of the building where they may cause a fire.
Where you can find a chimney cleanout or can remove a flue vent connector to look into a flue, use of a mirror inside the flue to view the flue from below. This is by no means a thorough and accurate view of all of the chimney flue interior.
But if the chimney was constructed as a straight flue up through the building roof, you should see daylight - otherwise the flue has become blocked, perhaps with nesting animals or collapsing debris.
We have found heating boilers with draft problems and "repair attempts" like removing the boiler's barometric damper, when all the while the root problem of bad chimney draft was that the cleanout door was open or missing.
Watch out: Our photo (left) shows a chimney thimble blocked by falling debris.
If you find this much trash at the bottom of your chimney or at any other chimney opening, you need an expert to evaluate the chimney condition and safety as soon as possible.
The chunks of masonry debris make it likely that the chimney in our photo at left is in very poor condition and is unsafe.
Continue reading at CHIMNEY CLEANOUT CLEARANCE to COMBUSTIBLES or select a topic from the index of chimney articles listed above.
Suggested citation for this web page
Green link shows where you are in this article series.
Frequently Asked Questions (FAQs)
Question: Do I need cleanout doors?
(Sept 10, 2011) Do I need cleanout doors? said:
As long as the cleanout doors are properly fitted, snug, not leaky, they're not interfering with draft, and should be left intact to permit chimney inspection.
Question: fireplace enclosures?
(Oct 24, 2012) grant said:
i have a wooden enclosed fireplace. in the attic three sides are closed the one facing the interior has been left open . do i need to enclose it as well. if so what material do i use?
I am unclear on what you're describing, Grant. A "wooden" enclosed fireplace sounds to me like kindling designed to set a house on fire.
If you mean you have a zero-clearance metal fireplace enclosed in a wood structure or chimney chase, that can be safe provided the installation followed the manufacturer's installation instructions, including fire safety cleareances (and of course complied with local codes).
I'm unclear on what was left open in the attic and what was enclosed and of course we don't know what type of chimney was installed. So I'm too chicken hearted to recommend specific steps or materials for an installation I know so little about.
Watch out: for safety I suggest asking your local building department of fire department to inspect this installation for safety and code compliance.
(Feb 26, 2014) Anonymous said:
I was told to fill clean out area with insulation to stop draft?
Anon I'm unclear what area you plan to fill with insulation but this does not sound like a safe, recommended treatment of a chimney. See my inspection recommendation for the reader just above.
Question: chimney cleanout installation details.
(5 Oct 2014) Nathhan Miller said:
I have a fireplace with a chimney that slopes about thirty degrees above the damper towards the outer wall of the chimney, leaving it very difficult to clean debris above the damper.
This space is about four feet from my chimney flue. Now I have installed a ceanout door on the outside of the chimney, twelve by twelve. My gflue is eleven by eleven. I put fire brick on the wall where part of the flueliner was broken out. Now my question, do I need to insulate the clean out door somehow?
This question was originally posted at ANGLED CHIMNEYS
Chimney cleanout doors are not normally insulated - and I'd be worried lest someone try doing so, especially if they applied a combustible material.
But you do want to be sure the door closes tightly so as not to subvert the chimney draft.
Use the "Click to Show or Hide FAQs" link just above to see recently-posted questions, comments, replies, try the search box just below, or if you prefer, post a question or comment in the Comments box below and we will respond promptly.
Search the InspectApedia website
HTML Comment Box is loading comments...
Technical Reviewers & References