Question? Just ask us!
Free Encyclopedia of Building & Environmental Inspection, Testing, Diagnosis, Repair
InspectAPedia ® Home
CHIMNEY INSPECTION DIAGNOSIS REPAIR
BACKDRAFTING HEATING EQUIPMENT
CARBON MONOXIDE - CO
CHIMNEY CAP & CROWN
CHIMNEY CLEANING PROCEDURES
CHIMNEY COMPONENT DEFINITIONS
CHIMNEY CRACK DETECTION & DIAGNOSIS
CHIMNEY DRAFT & PERFORMANCE
CHIMNEY FIRE ACTION / PREVENTION
CHIMNEY HEIGHT & CLEARANCE CODE
CHIMNEY INSPECTION, FLUE INTERIOR
CHIMNEY LEANING, SEPARATION, MOVEMENT
CHIMNEY REPAIR METHODS
CHIMNEY STAINS & LEAKS
CHIMNEY TYPES & MATERIALS
DIRECT VENTS / SIDE WALL VENTS
DRAFT REGULATOR, DAMPER, BOOSTER
FIRE CLEARANCES INDOORS
FIREPLACES & HEARTHS
FLUE VENT CONNECTORS
MASONRY CHIMNEY GUIDE
METAL CHIMNEYS & FLUES
SAFETY RECALLS CHIMNEYS VENTS HEATERS
SOOT AT CHIMNEY TOP
STAIN DIAGNOSIS on BUILDING EXTERIORS
WOOD, COAL STOVES & FIREPLACES
Catalog of chimney interior flue inspection methods & techniques: this article describes various methods that can be used to make a visual inspection of the interior of a chimney flue. Inspection methods taking advantage of existing openings such as at barometric dampers or chimney thimbles and cleanout doors can tell a lot about the condition of a chimney interior even though a complete view of the entire flue is not available.
Green links show where you are. © Copyright 2014 InspectApedia.com, All Rights Reserved.
Described in this article are more readily-accessible ways to inspect portions of the chimney flue interior by eye. Also see CHIMNEY FLUE INSPECTION CAMERA for a discussion of chimney inspection camera systems.
While none of these methods is comprehensive, valuable information can be easily obtained by putting two and two together combining visual clues about a chimney.
We recommend that you have any questionable chimney inspected by a professional and if necessary, make use of a remote camera and lighting to complete a detailed examination. But you can also make use of the methods we describe in this article.
Odors from a chimney or from heating equipment, high levels of indoor moisture, trouble keeping a gas burner going, rust on top of a heating appliance are examples of indoor observations that could indicate a very dangerous blocked chimney even before the homeowner or home inspector has approached the chimney itself.
Evidence of flue gas spillage may be easy to spot, especially with gas-fired equipment.
For example, the rust on the top of this gas-fired heating boiler was from a long history of spillage
from the boiler's draft hood.
The homeowner contacted us to ask for a diagnosis of the high level of water found on basement walls, not because she suspected an unsafe chimney and indoor carbon monoxide hazards.
It may be possible to obtain a limited view of the chimney interior by looking through the hinged door of a barometric damper, flue vent connector (disassembly required) or thimble (disassembly required), or where no flue vent connector is installed, if you find a cover closing off a previously-used chimney thimble, such as the old spring-loaded metal "pie plate" chimney thimble covers, it may be possible to inspect the chimney interior through those openings.
You may not be so lucky as to find a barometric damper giving view directly into the chimney flue (photo at left) but check to see if the draft regulator on a heater or water heater gives view into the chimney.
This damper location, built right into a chimney works properly only if just a single appliance is vented into this flue.
Also see DRAFT REGULATOR, DAMPER, BOOSTER.
Metal chimney flue liners have to be inspected by removing the vent connector from the chimney breach to check for corrosion. Sight up the liner with a mirror to check straightness, rust, holes, heavy creosote, leak evidence, and for metal flue blockage.
Metal chimney flue interiors & metal chimney liners have to be inspected from the chimney top and inside by removing the vent connector from the chimney breach to check for corrosion. Sight up the liner with a mirror to check straightness and for blockage.
Even when a home inspector cannot see much of the chimney flue through such a limited access opening, certain observations can be critical, such as:
A chimney thimble is a sleeve embedded in the chimney wall designed to accept the flue connector from an appliance. They must be placed with the chimney end flush with the inside wall of the flue lining and cemented in place with the refractory mortar used in the flue tiles.
The thimble is the masonry or clay or insulated metal sleeve that provides an entry passage for a metal flue vent connector to enter a masonry chimney.
The most common defect we see at the chimney thimble is failure to seal the metal flue at the entry to the chimney flue.
A broken or short thimble can allow combustion gases to rise in the air space between the flue liner and the masonry surround. Condensation stains will often appear in the mortar joints and as streaks running down the exterior face of the chimney. Wood or oil burners leave soot that leaches out as black streaks.
At FIREPLACE INSERTS we discuss fireplace inserts and zero-clearance fireplaces, both antique and modern, and their hazards and inspection limitations.
Green link shows where you are in this article series.
Frequently Asked Questions (FAQs)
Reader Question: (Aug 12, 2012) John said: I am getting a pale, sand colored, crystalline buidlup around the joints of my less than one year old I metal flue liner and the stuff has even dripped onto the top of the oil burner box which is also less than a year old. Looking through the flue damper, which is right next to the base of the chimney, I see only rust, which I am also not happy about. What is this stuff and how is it getting into my flue? Thanks
Reply: John, it sounds as if there is a condensation or leak problem in that chimney or the flue vent connector as well as deterioration. If the metal "flue" you describe is the actual chimney I'd ask a certified chimney sweep to inspect, clean, repair the system. Else it may be unsafe. If the metal flue you describe is actually the connector betweeen the heating appliance and the chimney, that's a job for your heating service technician.
Questions & answers or comments about choices among procedures for inspecting the condition of chimney flues
Use the "Click to Show or Hide FAQs" link just above to see recently-posted questions, comments, replies, try the search box just below, or if you prefer, post a question or comment in the Comments box below and we will respond promptly.
Search the InspectApedia website
HTML Comment Box is loading comments...
Technical Reviewers & References