Question? Just ask us!
Free Encyclopedia of Building & Environmental Inspection, Testing, Diagnosis, Repair
InspectAPedia ® Home
CHIMNEY INSPECTION DIAGNOSIS REPAIR
BACKDRAFTING HEATING EQUIPMENT
CARBON MONOXIDE - CO
CHIMNEY COMPONENT DEFINITIONS
CHIMNEY FIRE ACTION / PREVENTION
COMBUSTION GASES & PARTICLE HAZARDS
COMBUSTION PRODUCTS & IAQ
FLAME COLOR, BLUE vs YELLOW COMBUSTION
HEATING SYSTEM INSPECTION
HOME HEATING SAFETY
ODORS & SMELLS DIAGNOSIS & CURE
SAFETY RECALLS CHIMNEYS VENTS HEATERS
STAIN DIAGNOSIS on BUILDING EXTERIORS
WOOD, COAL STOVES & FIREPLACES
WOOD STOVE SAFETY
Chimney wet time: definition of chimney wet time. Modern metal chimneys, regardless of the metal used or other chimney construction details,have a significant potential for condensation and corrosion - conditions that can make a chimney unsafe and that lead to need for costly repairs. Here we give an explanation of hidden safety hazards caused by rust and corrosion of metal chimneys and flues.
These articles on chimneys and chimney safety provide detailed suggestions describing how to perform a thorough visual inspection of chimneys for safety and other defects. Chimney inspection methods and chimney repair methods are also discussed.
Green links show where you are. © Copyright 2013 InspectAPedia.com, All Rights Reserved.
Recommended venting systems with draft hood appliances were developed in the 50's for atmospheric aspirated appliances. The efficiencies were low and approximately 35% of the energy input was wasted.
Newer mid-efficiency Category I appliances have a much lower flue gas temperature and reduced off-cycle losses.
These new furnace designs alter the vent gas temperature, dew point temperature, flow rate and dilution air in the vent.
The result is that in modern metal chimneys, regardless of the metal used or other chimney construction details, there is much greater potential for condensation and corrosion.
Factors that control the degree and duration of wet conditions in metal chimneys and vent systems are critical to the life of the appliance.
The Gas Research Institute Venting Project reported (and subsequently published in the 1996 National Fuel Gas Code) the following venting occurrences:
Therefore, during the flue heat up time condensation forms inside the connector or flue. This moisture can dislodge soot products inside the flue which will fall to the bottom of the chimney or connector and become a corrosive media.
Rust and pitting: While rust is not as likely on a stainless steel chimney, corrosion can occur because of the corrosives in flue gases and in moisture that may develop inside of a chimney.
Carson Dunlop's sketch (above) warns us to inspect metal chimneys (of all types) for signs of rust and pitting.
Because metal flues corrode from the inside out, and because we on occasion find leaks between the layers of multiple-wall metal chimneys, discovery of these damage signs is important in evaluating chimney safety.
we have observed leaks and corrosion of metal chimneys from interior corrosion (described above) and also on occasion we have found exterior leaks into the interstitial space between the chimney walls due to loss of the rain cap or improper exterior installation or flashing.
Even a small amount of visible pitting on the exterior of a metal chimney or flue is likely to mean that the components are unsafe and need replacement.
Read More: see CONDENSING BOILERS/FURNACES DAMAGE
Thanks to home inspector Arlene Puentes for technical editing - 4/2014
Green link shows where you are in this article series.
Frequently Asked Questions (FAQs)
No FAQs have been posted for this page. Try the search box below or CONTACT US by email if you cannot find the answer you need at InspectApedia.
Use the search box below to ask a question or to search the InspectApedia.com website.
Ask a Question or Enter Search Terms in the InspectApedia search box just below.
Technical Reviewers & References
Related Topics, found near the top of this page suggest articles closely related to this one.