Question? Just ask us!
Free Encyclopedia of Building & Environmental Inspection, Testing, Diagnosis, Repair
InspectAPedia ® Home
CHIMNEY INSPECTION DIAGNOSIS REPAIR
BACKDRAFTING HEATING EQUIPMENT
CARBON MONOXIDE - CO
CHIMNEY CAP & CROWN
CHIMNEY CLEANING PROCEDURES
CHIMNEY COMPONENT DEFINITIONS
CHIMNEY CRACK DETECTION & DIAGNOSIS
CHIMNEY DRAFT & PERFORMANCE
CHIMNEY FIRE ACTION / PREVENTION
CHIMNEY HEIGHT & CLEARANCE CODE
CHIMNEY INSPECTION, FLUE INTERIOR
CHIMNEY LEANING, SEPARATION, MOVEMENT
CHIMNEY REPAIR METHODS
CHIMNEY STAINS & LEAKS
CHIMNEY TYPES & MATERIALS
DIRECT VENTS / SIDE WALL VENTS
DRAFT REGULATORS, DAMPERS, BOOSTERS
FIRE CLEARANCES INDOORS
FIREPLACES & HEARTHS
FLUE VENT CONNECTORS
MASONRY CHIMNEY GUIDE
METAL CHIMNEYS & FLUES
SAFETY RECALLS CHIMNEYS VENTS HEATERS
SOOT AT CHIMNEY TOP
STAIN DIAGNOSIS on BUILDING EXTERIORS
WOOD, COAL STOVES & FIREPLACES
Concrete block or cinder block chimney cracks & damage: this article describes cracks in masonry block or concrete block chimneys and suggests possible causes and crack severity.
These articles on chimneys and chimney safety provide detailed suggestions describing how to perform a thorough visual inspection of chimneys for safety and other defects. Chimney inspection methods and chimney repair methods are also discussed.
Green links show where you are. © Copyright 2014 InspectApedia.com, All Rights Reserved.
Cracked concrete block chimneys risk unsafe chimney flues, presenting fire and flue gas hazards in buildings
Both outdoors and indoors we may also see chimney cracks which could be due to chimney movement (introduced above) or due to compression loads or other chimney construction problems (photograph below).
Our photo (left) illustrates serious frost cracking damage in a concrete block (or masonry block or "cinder block") chimney serving a home in upstate New York. Notice that there is no rain cap and no chimney cap protecting this chimney against water intrusion - defects likely to lead to frost damage and an unsafe flue, especially in freezing climates.
Cracks in a masonry block chimney always deserve further investigation to identify the probable cause, to decide on the remedy and to evaluate the safety and function of the chimney.
We recommend that you have any cracked or damaged chimney thoroughly inspected by a professional, including an inspection of the integrity of the chimney flue and of any fireplaces or other attached heating systems.
Common Causes of Concrete Block ("cinder block") Chimney Cracking
Our photo (left) illustrates a concrete block chimney suffering from both extensive cracking as well as spalling surfaces (CHIMNEY SPALLING). We think there are leaks into the internal structure of this chimney, probably originating at the chimney cap.
It looks as if someone thought they might repair the chimney by coating its exterior with a masonry sealer paint or a thin stucco covering. But as leaks are originating from the chimney top and passing within the chimney structure, that repair did little good.
Cracks in a masonry chimney, particularly concrete block chimneys (this article) and perhaps brick may be caused by
Readers should also see CHIMNEY INSPECTION from GROUNDChimney Cracks, Separation, Movement.
Cracks in Masonry Chimneys May be Very Dangerous
Watch out: a chimney fire, even if it does not set the building ablaze, is likely to have caused serious damage to the chimney itself, leaving it unsafe, as may other chimney cracks or movements for any reason. The risks include building fires, potentially fatal flue gas leaks, improper draft, and unsafe heating equipment operation.
Our photo at left shows dangerous cracking indoors in a concrete block chimney used to vent a heating appliance.
Also see CHIMNEY CRACK DETECTION & DIAGNOSIS
Evidence of Prior Repairs May Indicate a History of Chimney Cracking & Movement in a Concrete Block Chimney
If you see repairs such as shown in the our photo (left) the chimney should be professionally inspected, especially to establish the condition of the flue liner as it may be unsafe.
Our pen points to a gap between masonry block chimney and a building wall, indicating chimney movement and raising question about other less obvious crack and damage to this structure.
It may be possible to repair minor chimney racks with masonry products provided that the underlying cause is also identified and corrected. Also, some concrete blocks may be cracked during their individual drying/curing process, a condition not to be confused with chimney cracking.
The usual repair when a significant chimney crack has occurred, damaging the chimney and the flue is to remove and replace the chimney, though in some cases it may be possible to re-line the chimney and to jack an intact masonry chimney back to level and repair its connections into the building.
Green link shows where you are in this article series.
Frequently Asked Questions (FAQs)
No FAQs have been posted for this page. Try the search box below or CONTACT US by email if you cannot find the answer you need at InspectApedia.
Questions & answers or comments about diagnosing & repairing cracked concrete block or masonry block chimneys.
Check the FAQs just above, try the search box just below, or if you prefer, post a question or comment in the Comments box below and we will respond promptly.
Search the InspectApedia website
HTML Comment Box is loading comments...
Technical Reviewers & References
Related Topics, found near the top of this page suggest articles closely related to this one.