Question? Just ask us!
Free Encyclopedia of Building & Environmental Inspection, Testing, Diagnosis, Repair
InspectAPedia ® Home
CHIMNEY INSPECTION DIAGNOSIS REPAIR
BACKDRAFTING HEATING EQUIPMENT
CARBON MONOXIDE - CO
CHIMNEY COMPONENT DEFINITIONS
CHIMNEY FIRE ACTION / PREVENTION
COMBUSTION GASES & PARTICLE HAZARDS
COMBUSTION PRODUCTS & IAQ
FLAME COLOR, BLUE vs YELLOW COMBUSTION
HEATING SYSTEM INSPECTION
HOME HEATING SAFETY
ODORS GASES SMELLS, DIAGNOSIS & CURE
SAFETY RECALLS CHIMNEYS VENTS HEATERS
STAIN DIAGNOSIS on BUILDING EXTERIORS
WOOD, COAL STOVES & FIREPLACES
WOOD STOVE SAFETY
Chimney fire clearance distances between masonry & wood framing: This article describes the fire clearances required for masonry chimneys. The distance between a brick, stone, concrete block,or other masonry chimney and the nearest combustible material, such as wood framing, is an important fire safety consideration that must be respected.
Green links show where you are. © Copyright 2014 InspectApedia.com, All Rights Reserved.
Masonry Chimney Fire Clearance from Wood Framing
As Carson Dunlop's sketches (above) illustrate, proper masonry construction leaves space between wood framing members and the chimney, or where framing rests on or in a masonry chimney, at least 12" of solid masonry should separate the chimney flue from the nearest wood framing member.
Readers of this article should also see CHIMNEY HEIGHT & CLEARANCE CODE. This article series on chimneys, chimney construction, and chimney safety provide detailed suggestions describing how to perform a thorough visual inspection of chimneys for safety and other defects.
Inspectors of older homes often find wood framing built right against masonry chimneys and at times we find wood framing that rests in a pocket in a masonry chimney structure, using the chimney to support the building framing.
Green link shows where you are in this article series.
Frequently Asked Questions (FAQs)
No FAQs have been posted for this page. Try the search box below or CONTACT US by email if you cannot find the answer you need at InspectApedia.
Questions & answers or comments about fire clearance distances & specificatsions for masonry chimneys.
Try the search box just below or if you prefer, post a question or a comment in the Comments box below and we will respond promptly.
Search the InspectApedia website
HTML Comment Box is loading comments...
Technical Reviewers & References
Related Topics, found near the top of this page suggest articles closely related to this one.