Question? Just ask us!
Free Encyclopedia of Building & Environmental Inspection, Testing, Diagnosis, Repair
InspectAPedia ® Home
CHIMNEY INSPECTION DIAGNOSIS REPAIR
BACKDRAFTING HEATING EQUIPMENT
CARBON MONOXIDE - CO
CHIMNEY COMPONENT DEFINITIONS
CHIMNEY FIRE ACTION / PREVENTION
COMBUSTION GASES & PARTICLE HAZARDS
COMBUSTION PRODUCTS & IAQ
FLAME COLOR, BLUE vs YELLOW COMBUSTION
HEATING SYSTEM INSPECTION
HOME HEATING SAFETY
ODORS & SMELLS DIAGNOSIS & CURE
SAFETY RECALLS CHIMNEYS VENTS HEATERS
STAIN DIAGNOSIS on BUILDING EXTERIORS
WOOD, COAL STOVES & FIREPLACES
WOOD STOVE SAFETY
This article describes the types of manufactured metal chimneys. We explain the difference between Class-A Chimneys, Metalbestos chimneys, Type B Vents, Type L Vents, Triple Wall metal chimneys, and Super Chimneys, 629 Chimneys, and 650-C Chimneys. Each of these chimney types has specific intended uses, fire clearances, and installation requirements. Improperly-installed chimneys, use of the wrong chimney type, or failure to properly maintain the chimney are likely to lead to unsafe conditions and risk a building fire.
Green links show where you are. © Copyright 2013 InspectAPedia.com, All Rights Reserved.
Our page top photo shows a remarkable number of metal chimneys (at least 24) on a Duluth Minnesota building. Can you explain it?.
The metal faux-chimney top shown in our photo is being inspected by an ASHI Headquarters staff member during a Chicago IL field trip.
Disassembly would be required to know much about the interior of this chimney, but from the exterior we can inspect for
Without more information we cannot see for sure just what kind of metal chimney terminates in the chimney cap shown by our ASHI Staff person.
FAQs about metal chimneys and flues: types, clearances, installation, inspection, fire hazards
Question: Metalbestos stove pipe fire clearances: roofing mastic was blobbed around our metalbestos chimney
I have an 8 inch Metalbestos™ stove pipe going through an open beam ceiling, with an avalon wood stove.My question is how hot does the outside of the metalbestos pipe get on the roof in the area of the stove pipe flashing, its a reddish rubber boot style?
The reason I am asking is a roofer installed a new metal roof and rubber boot flashing and cut the back side of boot to get it to fit then patched it with a black sticky flexible flashing, with flash point of 201 degrees. Thanks - R.W.Our photo (left) shows a Class A "Metalbestos™ type chimney at a low slope EPDM roof penetration - not the chimney penetration in the reader question described above. Photo courtesy Galow Homes.
Reply: Follow the manufacturer's instructions for air spaces and chimney clearances
A competent onsite inspection by an expert usually finds additional clues that help accurately diagnose a problem or identify fire clearance and chimney safety issues including the one you raise. But when workmanship is amateur or incomplete, keep in mind that the same installer may have made other errors..That said, here are some things to consider:The temperature that you will find on the outside of the metalbestos chimney pipe varies from cold (not in use) to warm (in normal use) to potentially higher, depending on what fuel is being burned, distance from the fire source, conditions in the chimney, and other variables.
Example of an insulated metal chimney surface temperature
At a new Class "A" insulated metal flue venting an oil fired heating boiler and located about 35" from the flue vent connector atop the boiler and with the boiler at operating temperature (about 450 degF inside the flue vent connector at the boiler top) the outside temperature of the metalbestos chimney was "hot" to the touch but less than 200 degF.But because of the variables involved that cause variation in metal chimney surface temperatures, I'm not sure anyone could quote a specific number to answer your question.
You will find in the metal chimney installation instructions (and perhaps your local building codes) that the manufacturer wants 2" or 2 1/2" air space clearance between the Class "A" chimney sections and any nearby combustibles.
So if your roofer put combustible roofing mastic against a Class-A chimney chimney s/he has probably violated the instructions and possibly local and national building codes.
Details about fire clearances for different types of metal flues and chimneys are found at FIRE CLEARANCES, METAL CHIMNEYS
These articles on chimneys and chimney safety provide detailed suggestions describing how to perform a thorough visual inspection of chimneys for safety and other defects. Chimney inspection methods and chimney repair methods are also discussed.This article explains the types, uses, characteristics, and installation requirements for different classes of metal chimneys.
All of these metal chimneys use multiple-walled metal pipe; some products add a fire-proof insulating material between the walls of the chimney pipe while others rely on air space.
Single-wall metal pipes used to connect heating appliances to chimneys (metal or masonry) are discussed separately at Single-Wall Metal Flue Vent Connectors where we provide details about single wall metal flues and their fire clearance requirements.
Green link shows where you are in this article series.
Frequently Asked Questions (FAQs)
No FAQs have been posted for this page. Try the search box below or CONTACT US by email if you cannot find the answer you need at InspectApedia.
Use the search box below to ask a question or to search the InspectApedia.com website.
Ask a Question or Enter Search Terms in the InspectApedia search box just below.
Technical Reviewers & References
Related Topics, found near the top of this page suggest articles closely related to this one.