Question? Just ask us!
Free Encyclopedia of Building & Environmental Inspection, Testing, Diagnosis, Repair
InspectAPedia ® Home
ENVIRONMENTAL HAZARDS - INSPECT, TEST, REMEDY
ACOUSTICAL SEALANT CHOICES
AGE of a BUILDING - how to determine
AIR BYPASS LEAKS
AIR LEAK DETECTION TOOLS
AIR LEAK MINIMIZATION
AIR LEAK SEALING PROCEDURE
AIR POLLUTANTS, COMMON INDOOR
ALLERGENS in BUILDINGS, RECOGNIZING
ANIMAL ALLERGENS / PET DANDER
APPLIANCE EFFICIENCY RATINGS
ARCHITECTURE & BUILDING COMPONENT ID
ASBESTOS CEILING TILES, Asbestos-Containing
ASBESTOS CEMENT ROOFING
ASBESTOS CEMENT SIDING
ASBESTOS DUCTS, HVAC
ASBESTOS-FREE INSULATION MATERIALS
ASBESTOS IDENTIFICATION IN buildings
ASBESTOS FLOORING HAZARD REDUCTION
ASBESTOS FLOORING REMOVAL GUIDE
ASBESTOS LIST of PRODUCTS
ASBESTOS MATERIAL REGULATIONS
ASBESTOS MATERIAL REGULATIONS Update
ASBESTOS MATERIAL REGULATIONS, OSHA
ASBESTOS PHOTO GUIDE to Materials
ASBESTOS REMOVAL, Amateur, Incomplete
ASBESTOS REMOVAL CERTIFICATIONS
ASBESTOS REMOVAL, Wetting Guidelines
ASBESTOS RISK ASSESSMENT
ASBESTOS TESTING LAB LIST
ASBESTOS UNDER the MICROSCOPE
ATTIC LEAKS, CONDENSATION & MOLD
BASEMENT HEAT LOSS
BUCKLED FOUNDATIONS due to INSULATION?
BUILDING NOISE DIAGNOSIS & CURE
CATHEDRAL CEILING INSULATION
CEILING FINISHES INTERIOR
CEILINGS, DROP or SUSPENDED PANEL
CEILINGS & WALLS, PLASTER TYPES
CERAMIC TILE FLOOR, WALL
CERAMIC TILE, ASBESTOS in?
CHIMNEY INSPECTION DIAGNOSIS & REPAIR
CHINESE DRYWALL HAZARDS
DEW POINT CALCULATION for WALLS
EFFLORESCENCE, Salts & White / Brown Deposits
FIBERGLASS INSULATION MOLD
FLOOR TILE HISTORY & INGREDIENTS
FLOOR TILES ASBESTOS
FLOOR TYPES & DEFECTS
HEAT LOSS in BUILDINGS
HOUSE DOCTOR, how-to be
HUMIDITY LEVEL TARGET
ICE DAM PREVENTION
INDOOR AIR QUALITY IMPROVEMENT GUIDE
INSULATION FACT SHEET- DOE
INSULATION IDENTIFICATION GUIDE
INSULATION R-Values & Properties
METAL LATH, PLASTER & STUCCO
METHANE GAS SOURCES
MOISTURE CONTROL in BUILDINGS
MOLD: A COMPLETE GUIDE TO MOLD
Museum Artifact Preservation
NOISE / SOUND DIAGNOSIS & CURE
ODORS & SMELLS DIAGNOSIS & CURE
PAINT FALURE, DIAGNOSIS, CURE, PREVENTION
PLASTER & BEAVERBOARD & DRYWALL
PLASTER BULGES & PILLOWS
PLASTER LATH, METAL
PLASTER, LOOSE FALL HAZARDS
PLASTER TYPE IDENTIFICATION
PLASTER VENEER Best Practices
ROOF VENTILATION SPECIFICATIONS
SAFETY HAZARDS & INSPECTIONS
SEARS KIT HOUSES
SOUND CONTROL in buildings
Splits in Structural Wood Beams
STAIN DIAGNOSIS on BUILDING EXTERIORS
STAIN DIAGNOSIS on BUILDING INTERIORS
STUCCO WALL METHODS & INSTALLATION
STRUCTURAL DAMAGE PROBING
SWEATING (CONDENSATION) on PIPES, TANKS
Thermal Expansion Cracking of Brick
THERMAL EXPANSION of MATERIALS
THERMAL IMAGING, THERMOGRAPHY
THERMAL MASS in BUILDINGS
THERMAL TRACKING Indicates Heat Loss
VAPOR BARRIERS & CONDENSATION in BUILDINGS
VENTILATION in BUILDINGS
VINYL CHLORIDE HEALTH INFO
Volatile Organic Compounds VOCs
WALL CONSTRUCTION BARRIER vs CAVITY
WATER ENTRY in buildings
WINDOWS & DOORS
WINTERIZE A BUILDING
WOOD Burning Heaters Fireplaces Stoves
WORLD TRADE CENTER 9-11 DUST PHOTOS
Transite asbestos chimneys, ducts, flues, pipes: this article assists in the recognition of transite pipe used for chimneys or heating flues and discusses potential hazards of this material when it is found in buildings. Transite pipe is an asbestos-cement product which was used for both HVAC ducts and for chimney or flue material to vent gas-fired appliances. This document assists building buyers, owners or inspectors who need to identify asbestos materials (or probable-asbestos) in buildings by simple visual inspection. We provide photographs and descriptive text of asbestos insulation and other asbestos-containing products to permit identification of definite, probable, or possible asbestos materials in buildings. Cement-asbestos transite pipe was also used for water piping in some communities, as we discuss at TRANSITE PIPE WATER SUPPLY PIPING.
Green links show where you are. © Copyright 2013 InspectAPedia.com, All Rights Reserved.
Because asbestos cement transite pipe chimneys may have operating and safety problems, concerns completely separate from asbestos handling questions, readers should see our chimney inspection suggestions at CHIMNEY INSPECTION DIAGNOSIS REPAIR.
While an expert lab test using polarized light microscopy may be needed to identify the specific type of asbestos fiber, or to identify the presence of asbestos in air, dust or drinking water samples, many asbestos-containing building products not only are obvious and easy to recognize, but since there were not other look-alike products that were not asbestos, a visual identification of this material can be virtually a certainty in many cases.
Watch out: Unsafe transite pipe heating flue vents may only be noticed by a careful building inspection such as shown in these rooftop photographs of a transite flue vent pipe which deteriorated, became swollen, and risk becoming blocked. In cold climates with these vents from the 1950's era, the real hazard is not so much asbestos fibers as the dangerous obstruction of the vent/flue by the deterioration of the interior of the pipe. [Photographs above and text just above on transite flue deterioration were provided courtesy of Roger Hankey].
In the transite chimney vent photo at above right we note that the exterior has been painted black. We don't know why, possibly the naturally gray-white transite flue was painted black for cosmetic reasons, or perhaps in an effort to slow down its surface deterioration.
Fire Clearance Requirements for & Label Descriptions of Asbestos Cement or Transite Heating Flues & Chimneys
In use as a gas-fired appliance chimney/vent transite pipe may have been classed as a type "B" flue vent which required 1" clearance from combustibles in some jurisdictions. But as we indicate below, the fire clearance required for transite pipe or cement-asbestos pipe flues and chimneys varied from 1" to 3" and limited temperatures to 330 to 550 F depending on the clearance.
Ervin McKinney kindly provided a copy of a November 1948/1949 Underwriters Laboratories UL List of Inspected Gas, Oil, and Miscellaneous Appliances that includes specifications for Outlet and Vent Piping (540 116). That document indicates that
Asbestos Cement Chimney & Flue Venting Products described in this 1948-1949 document include
Enderle, Inc., Ltd., Frank X., Los Angeles Calif.
Johns-Manville Corp. New York, NY., [Transite or cement asbestos flue vent and chimney piping description]
This same document also describes several other flue gas vent piping products made of vitreous coated steel, asbestos, sand, and cement, sand and pumicite with aluminum collar joints, sheet aluminum tube and asbestos insulating or steel spring spacer with an outer shell of galvanized sheet metal, and other aluminum and galvanized sheet metal piping.
Where transite pipe (asbestos-cement pipe) has been used as a building chimney to vent combustion gases, if the chimney becomes blocked there could be a dangerous carbon monoxide hazard in the building.
The transite pipe chimney - carbon monoxide hazard occurs when the (usually above-roof outdoor portion) of a transite pipe chimney becomes soft with age and exposure to weather, leading to swollen chimney sides and even chimney internal collapse.
The swollen and collapsing transite pipe chimney blocks the venting of exhaust gases from the building heating equipment.
Blocking the venting of exhaust gases, particularly for natural gas or LP gas fired heating appliances, is very likely to interfere with proper combustion at the appliance itself. In turn, this condition results in the production of carbon monoxide at high levels.
The transite flue vents, shown here are passing through a building interior closet.
Transite-asbestos piping used as plumbing vents or as chimneys for gas-fired appliances such as gas furnaces becomes swollen and deteriorated due to condensation of the water vapor in the combustion gases being vented, especially above the roof line or in a cold attic.
The acidic flue-gas-condensate combined with the effects of frost in cold climates causes a delamination and swelling and blockage of the transite pipe chimney-flue.
A blocked or constricted flue vent pipe can cause production of dangerous or even fatal carbon monoxide gas in the building.
While the transite pipe shown above was in use as an exhaust flue (what is the fire rating and fire clearance required?), this material was also used in some buildings for both exposed air ducts and for in-slab duct work (SLAB DUCTWORK) for heating and air conditioning systems, as shown in the photos below.
Transite pipe, which contains significant percentage of asbestos fibers, was often used for heating ducts and on occasion heating and cooling ducts in older buildings.
The transite pipe was used in a buried-in-slab construction methods which placed the transite piping below or in a building floor slab, and asbestos-containing transite pipe ducts were also used in exposed areas such as shown in the crawl space photographs above. [Photo above showing transite duct material is provided courtesy of Thomas Hauswirth, a Connecticut home inspector.]
At CHIMNEY INSPECTION DIAGNOSIS REPAIR we describe chimney inspections in detail.
Asbestos hazards of transite duct or chimney piping: Cementious duct material may contain asbestos. What is this "cement"
duct work made of? Cement and asbestos fibers.
Transite pipe typically contains about
15% to 25% asbestos fibers, typically fibrous chrysotile asbestos.
Health Hazards from Handling Transite Pipe or Asbestos Cement Piping for Vents, Chimneys, or Air Ducts
Where are the chief health risks with cementious asbestos materials?
Transite pipe, whether it has been used as an air duct, flue vent, chimney, or water pipe, is still a cementious material that is unlikely to release high levels of airborne fibers when it is in good condition.
Touching transite pipe, or simply removing and disposing of an intact section of this material from a building by carrying it outside should not release a significant level of airborne asbestos fibers unless:
In summary, if it has become soft and friable, or if transite pipe is damaged or is cut mechanically (such as by using power equipment), friable, airborne asbestos fibers may
be generated - a health and potentially a costly cleanup concern.
Incorrect spellings of transite piping or transite duct material that we've seen include transit pipe, transit ducts, Transide pipe, transide ducts, tranisite pipe, and transight pipe. "Transite" is the correct spelling.
Green link shows where you are in this article series.
Frequently Asked Questions (FAQs)
No FAQs have been posted for this page. Try the search box below or CONTACT US by email if you cannot find the answer you need at InspectApedia.
Use the search box below to ask a question or to search the InspectApedia.com website.
Ask a Question or Enter Search Terms in the InspectApedia search box just below.
Technical Reviewers & References
Related Topics, found near the top of this page suggest articles closely related to this one.