InspectAPedia tolerates no conflicts of interest. We have no relationship with advertisers, products, or services discussed at this website.
Definitions of electrical ground, grounding, grounding system components & terms: this article defines the terms used to describe the building electrical grounding system & its components, including grounding & grounded conductors, grounding electrode, bonding, ufer and related terms.
Building Electrical Grounding System Terms & Definitions
Here are some elementary electrical ground, grounding, and ground wire definitions to help us get our terms straight when discussing electrical grounds, grounding, and ground bonds.
[Click to enlarge any image]
Page top sketch and other electrical ground system sketches used in this article are used with permission and were provided courtesy of Carson Dunlop Associates, a Toronto home inspection education firm and inspection firm.
Ground: means the physical earth, the soil or ground. In some countries the term earth is used and is synonymous with ground. In the electrical code, ground means an electrically conducting connection, intentional or accidental, between an electrical circuit and the earth.
Grounded means that something has been electrically connected to the earth. Watch out: even among inspectors and electricians, people may use the term "ground" more loosely to refer to the equipment grounding conductor or other components. Also see Grounded Conductor (below).
What is a Grounding Electrode?
Grounding electrode or ground electrode: a metal conductor, usually a solid copper-alloy rod of specified length, driven into the ground in order to provide a point for electrical connection between the building grounding system and ground or earth.
In the electrical code, the grounding electrode conductor is the conductor (a wire) used to connect the grounding rod(s) to the equipment grounding conductor (the ground bus and ground wires in the electrical panel) OR to the grounded conductor (the neutral bus and neutral wires) OR to connect both of these to the grounding electrode (which is usually the case in residential electrical systems).
What's the difference between "Grounded electrical conductor" and "Grounding Conductor"?
GroundedConductor (the neutral wire): by convention the grounded conductor or neutral wire is white or gray. In an electrical circuit the grounded conductor (white or neutral wire) normally carries electrical current between the un-grounded (hot) electrical wire and (back through the main electrical panel and grounding system) earth.
In the electrical code, a grounded conductor is one which has been intentionally grounded - connected to the earth.
The amount of current carried by the neutral wire is called the un-balanced load and depends on the characteristics of the electrical device being operated by the circuit. The neutral conductor is grounded in the main electrical panel. Be careful, inspectors and electricians, speaking loosely, may simply call this the "neutral wire".
Equipment Grounding Conductor (the ground wire): By convention the equipment grounding conductor (ground wire) is bare copper or carries green insulation. the individual wire in a (grounded) electrical circuit that is connected through the ground bus in the electrical panels and ultimately in the main electrical panel is connected to ground or earth.
In the U.S. National Electrical Code and most other model electrical codes, a grounding conductor is a conductor (metal wire, metal bar, etc) which is used to connect electrical equipment (like an electrical panel enclosure) or the grounded circuit (the neutral wires) of a wiring system to a grounding electrode (and thus to earth).
The ground wire in an electrical circuit does not normally carry any electrical current, but it remains available as an emergency path to allow current to flow to earth should an electrical fault such as a short circuit occur (a connection between a hot wire and some metal (conductive) material that could cause an electrical shock to someone), thus assuring that a fuse or circuit breaker in the main panel can sense the current flow and switch off the circuit.
Watch out: In an older two-wire armored cable (BX) electrical circuit, the metallic cable of the circuit may be serving as the only grounding conductor. This is not a safe installation: should the metallic cable sheath carry live current (say due to a fault or faulty electrial wiring) someone touching the BX cable can be shocked - an event witnessed by the author.
It helps to keep these terms straight if we remember that we use the ing form of the word grounding to mean that this conductor causes an electrical connection between earth and whatever the grounding conductor is connected to.
Electrical Bonding Definitions (consistent with NEC article 100)
Bonding or Bonded: means that metallic parts are permanently joined so as to assure that they form a reliably continuous electrical path and that the parts are capable of conducting any electrical current that may be imposed on them.
A bonding jumper is a reliable electrical conductor used to connect metal parts together and a main bonding jumper is the connection between the grounded circuit conductor and the equipment grounding conductor at the electrical service (panel).
Ground bond: refers to a physical electrical connection between any metal component (like metal water pipes, metal gas piping, a metal electrical panel enclosure, or a neutral or ground bus in the main electrical panel) and the building electrical ground system.
In the main electrical panel the neutral wires are physically bonded to the ground wires (by a larger diameter wire or by a metal bar inside the panel) and the ground wire bus (a metal bar) is further connected to a grounding conductor that connects those components to the building ground system: one or more grounding electrodes and possibly a connection to an incoming metal water pipe that is buried outside. An electrician would say that the building's ground and neutral wires are bonded to earth
Bonding electrical components together makes certain that all of the joined items are at the same electrical potential (that is, that current will not flow from one to the other). Examples of electrical bonds in buildings include:
In electrical panels or sub panels the neutral wires are all bonded together on a neutral bus or bar.
In individual electrical panels or sub-panels the ground wires are all bonded together on a ground bus or bar.
In the main electrical panel at a building, the neutral bus and ground bus and electrical panel itself are all bonded together and are connected to the building grounding system. In a sub panel the neutral bus and ground bus are not bonded together and must be kept separate.
Definition of Ufer ground: electrical grounding using concrete & electrodes
What is a Ufer ground?
A UFER is an electrical ground connection to earth provided by a concrete encased grounding electrode. This approach to electrical grounding improves the ground connection to earth in areas where soils are so dry that otherwise grounding may be ineffective. UFER grounding has been included in the U.S. National Electrical Code (NEC) since 1968.
UFER electrical grounding was developed in 1942 by Herbert G. Ufer who worked as a consultant to the U.S. Army to improve electrical grounding for bomb storage vaults in Arizona where dry soils limited the efficacy of electrical grounding using a driven copper electrode hammered into the soil.
Below we include additional research citations on the efficacy of Ufer grounding for electrical systems & buildings where you'll see H.G. Ufer's seminal paper on Ufer ground in in bold font. Wikipedia's entry for Ufer ground points out that Ufer observed that concrete was more conductive than most types of soil, permitting grounding by concrete-encased electrodes.
In modern construction a UFER connection may refer to a continuously bonded steel re-bar (or other grounding electrode) used in construction of a concrete footing or slab that is in turn bonded to the electrical ground system for the building.
We presume that the increased area and conductivity of the larger area of concrete in contact with the soil combined with conductivity of the concrete itself is what gives an improved local electrical ground-to-earth connection for the building. - "Ufer ground", Wikipedia, retrieved 4/27/14, original source: http://en.wikipedia.org/wiki/Ufer_ground
Useful References & Citations on Ufer Grounding
Collatz, L., G. Meinardus, and H. Unger. "Zur Berechnung des zeitabhangigen Neutronenausflusses mit der Monte-CarlodMethode."
Durham, Marcus O., and Robert A. Durham. "Grounding system design for isolated locations and plant systems." In Petroleum and Chemical Industry Conference, 1995. Record of Conference Papers., Industry Applications Society 42nd Annual, pp. 145-153. IEEE, 1995.
Fagan, Eugene J., and Ralph H. Lee. "The use of concrete-enclosed reinforcing rods as grounding electrodes." Industry and General Applications, IEEE Transactions on 4 (1970): 337-348.
Hope, Roger, Dave Harrold, and David Brown. Control System Power and Grounding Better Practice. Elsevier, 2004.
McIntosh, Donald H. "Grounding where corrosion protection is required." Industry Applications, IEEE Transactions on 6 (1982): 600-607.
MORA, PABLO JOSÉ JIMÉNEZ. "UTILIZACION DE PILOTES DE CONCRETO REFORZADO COMO ELECTRODOS DE PUESTA A TIERRA EN LINEAS DE TRANSMISION."
Preminger, Julius. "Evaluation of concrete-encased electrodes." Industry Applications, IEEE Transactions on 6 (1975): 664-668.
Rowland, Phillip W. "Industrial system grounding for power, static, lightning and instrumentation, practical applications." In Textile, Fiber and Film Industry Technical Conference, 1995., IEEE 1995 Annual, pp. 1-6. IEEE, 1995.
Stockin, David R. "Design and testing of facilities ground." In Electrical Overstress/Electrostatic Discharge Symposium Proceedings 2000, pp. 368-374. IEEE, 2000.
Ufer, H. G. "Investigation and testing of footing-type grounding electrodes for electrical installations." Power Apparatus and Systems, IEEE Transactions on 83, no. 10 (1964): 1042-1048.
"Ufer ground", Wikipedia, retrievd 4/27/14, original source: http://en.wikipedia.org/wiki/Ufer_ground
Vaselich, R., and J. Dixon. Lightning Protection Documentation. No. NWL-AR-124. NAVAL WEAPONS LAB DAHLGREN VA, 1973.
Wiener, Paul. "A comparison of concrete encased grounding electrodes to driven ground rods." Industry and General Applications, IEEE Transactions on 3 (1970): 282-287.
Zipse, D. W. "Grounding: The good, the bad and the stupid." In Petroleum and Chemical Industry Technical Conference (PCIC), 2013 Record of Conference Papers Industry Applications Society 60th Annual IEEE, pp. 1-9. IEEE, 2013.
Zipse, Donald W. "Earthing-Grounding methods: a primer." In Petroleum and Chemical Industry Conference, 2001. IEEE Industry Applications Society 48th Annual, pp. 11-30. IEEE, 2001.
Zipse, Donald W. "Grounding." Wiley Encyclopedia of Electrical and Electronics Engineering (1999).
Other electrical ground system citations are at REFERENCES
No FAQs have been posted for this page. Try the search box below or CONTACT US by email if you cannot find the answer you need at InspectApedia.
Ask a Question or Search InspectApedia
Use the "Click to Show or Hide FAQs" link just above to see recently-posted questions, comments, replies, try the search box just below, or if you prefer, post a question or comment in the Comments box below and we will respond promptly.
At ALUMINUM GROUND WIRES we discuss proper repair of aluminum ground wires found in solid conductor branch circuit wiring.
Mark Cramer Inspection Services Mark Cramer, Tampa Florida, Mr. Cramer is a past president of ASHI, the American Society of Home Inspectors and is a Florida home inspector and home inspection educator. Mr. Cramer serves on the ASHI Home Inspection Standards. Contact Mark Cramer at: 727-595-4211 mark@BestTampaInspector.com
John Cranor is an ASHI member and a home inspector (The House Whisperer) is located in Glen Allen, VA 23060. He is also a contributor to InspectApedia.com in several technical areas such as plumbing and appliances (dryer vents). Contact Mr. Cranor at 804-747-7747 or by Email: email@example.com
Home Inspection Education Home Study Courses - ASHI@Home Training 10-course program. Special Offer: Carson Dunlop Associates offers InspectAPedia readers in the U.S.A. a 5% discount on these courses: Enter INSPECTAHITP in the order payment page "Promo/Redemption" space. InspectAPedia.com editor Daniel Friedman is a contributing author.
The Home Reference Book, a reference & inspection report product for building owners & inspectors. Special Offer: For a 10% discount on any number of copies of the Home Reference Book purchased as a single order. Enter INSPECTAHRB in the order payment page "Promo/Redemption" space. InspectAPedia.com editor Daniel Friedman is a contributing author.
The Home Reference eBook, an electronic version for PCs, the iPad, iPhone, & Android smart phones. Special Offer: For a 5% discount on any number of copies of the Home Reference eBook purchased as a single order. Enter inspectaehrb in the order payment page "Promo/Redemption" space.
The Illustrated Home illustrates construction details and building components, a reference for owners & inspectors. Special Offer: For a 5% discount on any number of copies of the Illustrated Home purchased as a single order Enter INSPECTAILL in the order payment page "Promo/Redemption" space.
The Horizon Software System manages business operations,scheduling, & inspection report writing using Carson Dunlop's knowledge base & color images. The Horizon system runs on always-available cloud-based software for office computers, laptops, tablets, iPad, Android, & other smartphones
Wikipedia provided background information about some topics discussed at this website provided this citation is also found in the same article along with a " retrieved on" date. NOTE: because Wikipedia entries are fluid and can be amended in real time, we cite the retrieval date of Wikipedia citations and we do not assert that the information found there is necessarily authoritative.
Books & Articles on Building & Environmental Inspection, Testing, Diagnosis, & Repair
The Home Reference Book - the Encyclopedia of Homes, Carson Dunlop & Associates, Toronto, Ontario, 25th Ed., 2012, is a bound volume of more than 450 illustrated pages that assist home inspectors and home owners in the inspection and detection of problems on buildings. The text is intended as a reference guide to help building owners operate and maintain their home effectively. Field inspection worksheets are included at the back of the volume. Special Offer: For a 10% discount on any number of copies of the Home Reference Book purchased as a single order. Enter INSPECTAHRB in the order payment page "Promo/Redemption" space. InspectAPedia.com editor Daniel Friedman is a contributing author.
Or choose the The Home Reference eBook for PCs, Macs, Kindle, iPad, iPhone, or Android Smart Phones. Special Offer: For a 5% discount on any number of copies of the Home Reference eBook purchased as a single order. Enter INSPECTAEHRB in the order payment page "Promo/Redemption" space.