Question? Just ask us!
Free Encyclopedia of Building & Environmental Inspection, Testing, Diagnosis, Repair
InspectAPedia ® Home
ELECTRICAL INSPECTION, DIAGNOSIS, REPAIR
AFCIs ARC FAULT CIRCUIT INTERRUPTERS
ALUMINUM WIRING HAZARDS & REPAIRS
AMPS VOLTS DETERMINATION
AMPERAGE MEASUREMENT METHODS
APPLIANCE EFFICIENCY RATINGS
BOOKSTORE - ELECTRICAL
CADET & ENCORE HEATER RECALL
CHALLENGER ELECTRIC PANELS
CIRCUIT BREAKER SIZE for A/C or HEAT PUMP
Classified CIRCUIT BREAKER WARNING
CUTLER HAMMER PANEL FIRE
CORROSION in ELECTRICAL PANELS
DEFINITIONS of ELECTRICAL TERMS
DIRECTORY OF ELECTRICIANS
DMM Digital Multimeter HOW TO USE
ELECTRIC METERS & METER BASES
ELECTRIC MOTOR DIAGNOSTIC GUIDE
ELECTRIC MOTOR OVERLOAD RESET SWITCH
ELECTRIC PANEL AMPACITY
ELECTRIC PANEL INSPECTION
ELECTRIC PANEL MOISTURE
Electric Power Frequency Table
EMF RF FIELD & FREQUENCY DEFINITIONS
ELECTRICAL GROUND SYSTEM INSPECTION
ELECTRICAL SERVICE DROP
ELECTRICAL SERVICE ENTRY WIRING
EMF RF FIELD & FREQUENCY DEFINITIONS
FIRE SAFETY Checklist, CPSC
GFCI PROTECTION,Testing GFCIs AFCIs
HEATING COST FUEL & BTU COST TABLES
HEAT TAPE USAGE GUIDE
Hertz - Definitions of KHz MHz GHz THz
KNOB & TUBE WIRING
LIGHTING, EXTERIOR GUIDE
LIGHTING, INTERIOR GUIDE
LIGHTNING PROTECTION SYSTEMS
LOW VOLTAGE BUILDING WIRING
LOW VOLTAGE TRANSFORMER TEST
MAIN ELECTRICAL DISCONNECT
MAIN DISCONNECT AMPACITY
MOISTURE SOURCES in PANELS
MURRAY SIEMENS Recall
PHOTOVOLTAIC POWER SYSTEMS
PUSHMATIC - BULLDOG PANELS
REMOTE ELECTRIC POWER, PHOTOVOLTAIC
RUST in ELECTRICAL PANELS
SAFETY for ELECTRICAL INSPECTORS
SE CABLE SIZES vs AMPS
SIEMENS MURRAY Recall
THERMAL EXPANSION of HOT WATER
THERMAL EXPANSION of MATERIALS
UNDERGROUND SERVICE LATERALS
VOLTS / AMPS MEASUREMENT EQUIP
VOLTAGE MEASUREMENT METHODS
WIND TURBINES & LIGHTNING
ZINSCO SYLVANIA ELECTRICAL PANELS
Lost neutral wire - lost grounded conductor wire:
Lost neutral or weak neutral wire electrical connections at a building: what can happen?
This document describes a case history of loss of the neutral connection in an electrical panel combined with failure to isolate the neutral and ground buses leading to an electrical shock.
Green links show where you are. © Copyright 2014 InspectApedia.com, All Rights Reserved.
Case History of an Electrical Ground Failure - Loss of a Neutral Connection in an Electrical Sub Panel Badly Shocks a Homeowner
Building owner gets a nasty electrical shock: In an electrical failure case which we investigated, a building owner asked us to determine why he had received a severe electrical shock when he touched his metal work bench located in a detached garage.
Here is what we found in the electrical sub panel in the detached garage:
[Click any image in these articles to see an enlarged, detailed version.]
Our photo at left has a black arrow pointing to the incoming neutral wire in the sub panel. The neutral wire looked connected, but it was not.
Technical note: as reader Jim Benson pointed out, the proper and electrical-code term for the popularly-referred-to "neutral wire" is "grounded conductor wire".
Question: What did all of these sub panel neutral and ground wire problems & electrical wiring errors mean?
When the air compressor motor was running it was producing a significant current on the compressor's neutral circuit.
The garage neutral circuit had no connection back to the main building (where it would have been connected to earth in the main panel, but because the owner had (improperly) bonded together the ground and neutral bus in his garage sub panel, the garage neutral circuit was indeed finding a path to earth through a small diameter (and thus overheated and dark) copper ground wire and a local grounding electrode.
Bud, a master electrician from Minnesota points out that in the 2005 NEC there are 2 ways to connect a subpanel in a detached garage. In both methods grounding electrode(s) are required at the garage.
Normally the neutral-to-ground bond is made in the main electrical panel and not in sub panels, lest grounding conductors end up carrying current during normal operations - a shock hazard. As Bud describes above, in the now obsolete, not allowed case, it was possible to wire a remote outbuilding sub panel as if it were a "main", with no ground returning to the actual remote main panel, and with a neutral-ground bond in the sub panel plus an effective local grounding electrode. We do not recommend this obsolete wiring approach. - Ed.
The problem in this case is the loss of the feeder neutral.
Summarizing some key observations in this lost neutral sub panel case:
Summarizing our conclusions (we will amend if with readers we develop a different analysis of this case):
A combination of missing main neutral in sub panel back to main panel, connecting neutral and ground buses in the sub panel, local ground at the sub panel, connection of metal work bench to panel ground bus, and modified 3-phase compressor in operation produced an electrically live workbench (owner was shocked), and conspired to visibly overheat grounding conductors, hot wires to the panel, panel bus behind the breakers, and grounding wire to the local electrode.
Additional photographs from this case are shown just below. Thanks to reader Randy Gardner for discussing this lost neutral case and opening an argument for clarification of just what was going on.
Below left: metal workbench that was connected to ground wire bus in the sub panel. Below right: overheated corroded main bus connections in the sub panel.
Below left: 3-phase compressor "re-wired" to run on 240V (we suspect that a 3rd leg was connected to a neutral or ground wire at this hookup. Below right: overheated wires in the sub panel at circuit breakers (we suspect these were powering the compressor motor).
Why Do Electrical Power Surges or Lightning Strike Current Go to Ground While Short Circuits Follow a Path to the Utility Ground?
Question: We were a little unclear as to why surges find their way to the local earth connection (higher resistance path) while in an emergency such as a short circuit hot to neutral or hot to ground wire, the current does not.
Answer: Bud continued this helpful explanation:
Question: Isn't it the case that current always prefers the path of least resistance and that the current can actually be calculated to flow on two (for example) different paths as a direct function of the relative resistance of each path?
Answer: Nicely stated, particularly the end.
And in the case of the ground fault tripping a breaker there will be some current through the earth, just like there is some normal neutral current through the earth. But the resistance of the service neutral is far lower than the earth.
The root causes of this electrical shock were:
Because the garage electrical system was carrying current that should have been flowing only on the insulated neutral wires in the building, when the owner touched his grounded metal work bench and was also touching a damp floor, current flowed through the ground wire, through the metal work bench, through the owner, to earth.
Sketch courtesy of Carson Dunlop Associates.
Our case study of a DOUBLE FAULT involving loss of both the utility company ground and the local building ground shows how power can simply be lost in a building due to grounding system defects.
Continue reading at FALSE NEUTRAL CONNECTIONS or select a topic from the More Reading links shown below.
Suggested citation for this web page
Green link shows where you are in this article series.
Frequently Asked Questions (FAQs)
Question: neutral lost at transformer connection
(June 10, 2011) Ralph Griswold said:
The electric utility servicing my sister's home in West Boylston, MA lost the neutral on the transformer connection so she only had single phase 240 volt service. In turn her TV, stove, and refrigerator as well as a few lights were lost. Is there any way that the home owner can protect his home when the failure is the Utility?
A residential electrical system should have a local ground that offers SOME protection should the neutral line from the utility company become lost. However such a condition is still UNSAFE for several reasons including that the local ground itself may be unreliable and also because unexpected live electrical current may be present on un-insulated ground system components - someone could be shocked or electrocuted.
More, from what you describe there appears to have been more than one problem - such as losing half of the electrical panel.
In an any case the safe procedure would have been to turn off ALL electrical power pending repairs from the electrical company and a local licensed electrician.
The ONLY setup that occurs to me that could be SAFE in the condition you describe is one in which an isolation switch is installed such as the system used when a backup home generator is installed and in use. The isolation switch disconnects the electrical panel from the utility company wiring entirely and connects it over to the backup generator system. It's an "either-or" system: either you are connected to the utility company or your are connected to the local generator, but never to both at the same time.
12/21/2014 Jim Benson said:
Hi, I really like all the info for guys and gals coming up in the trade, I was gonna do it but my patience just wasn't in it. Im disabled and get bored so all I do is read code and do electronics. Ive been in the biz for 32 yrs and have been a licensed master and inspector in NJ and PA. I wanted to ask you if you ever thought of removing the word "neutral" and using grounded conductor, not grounding just grounded as the NEC uses. Its hard to change I know because Im in a world of electronics I wanna see if you have any material on. Thanks! Really great work....... Jim
Thanks Jim you are of course entirely correct, that is, speaking codewise or electrically properly we'd call the neutral wire the grounded conductor.
As an editor and writer I've got a different, messier idea. If I want our readers to be able to find information or to understand it, I need to use both the technically correct language AND the terms that those readers use themselves.
We've also got to recognize that we have readers all over the world. So for example we may refer to a septic drainfield also as a leach field or as a soakpit or as a soakaway bed and so-on.
If you see specific places in the text where we ought to add language to make this point more clear I'd appreciate having those editorial suggestions.
Use the "Click to Show or Hide FAQs" link just above to see recently-posted questions, comments, replies, try the search box just below, or if you prefer, post a question or comment in the Comments box below and we will respond promptly.
Search the InspectApedia website
HTML Comment Box is loading comments...
Technical Reviewers & References