Question? Just ask us!
Free Encyclopedia of Building & Environmental Inspection, Testing, Diagnosis, Repair
InspectAPedia ® Home
ELECTRICAL INSPECTION, DIAGNOSIS, REPAIR
ACCURACY vs PRECISION of MEASUREMENTS
AFCIs ARC FAULT CIRCUIT INTERRUPTERS
ALUMINUM SECs & WIRING
ALUMINUM WIRING HAZARDS & REPAIRS
AMPS & VOLTS DETERMINATION
AMPACITY - the LIMITING FACTOR
APPLIANCE EFFICIENCY RATINGS
BACKUP ELECTRICAL GENERATORS
BACK-WIRED ELECTRICAL DEVICES
BOOKSTORE - ELECTRICAL
BUILDING SAFETY HAZARDS GUIDE
Cadet & Encore Heater Recall
CIRCUIT BREAKER FAILURE
CIRCUIT BREAKER SIZE for A/C or HEAT PUMP
Classified CIRCUIT BREAKER WARNING
CIRCUIT BREAKER SIZE for A/C or HEAT PUMP
Classified CIRCUIT BREAKER WARNING
CORROSION in ELECTRICAL PANELS
CORROSION & MOISTURE SOURCES in PANELS
CUTLER HAMMER PANEL FIRE
DEFINITIONS of ELECTRICAL TERMS
DIRECTORY OF ELECTRICIANS
DMM Digital Multimeter HOW TO USE
ELECTRIC METERS & METER BASES
ELECTRIC PANEL AMPACITY
ELECTRIC PANEL INSPECTION
ELECTRIC PANEL MOISTURE
Electric Power Frequency Table
EMF RF FIELD & FREQUENCY DEFINITIONS
ELECTRICAL GROUND SYSTEM INSPECTION
ENERGY SAVINGS in buildings
FEDERAL PACIFIC FPE HAZARDS
FIRE SAFETY Checklist, CPSC
GFCI PROTECTION,Testing GFCIs AFCIs
HEATING COST FUEL & BTU Cost Table
KNOB & TUBE WIRING
LOW VOLTAGE BUILDING WIRING
LOW VOLTAGE TRANSFORMER TEST
MAIN ELECTRICAL DISCONNECT
MAIN DISCONNECT AMPACITY
PUSHMATIC - BULLDOG PANELS
RUST in ELECTRICAL PANELS
SAFETY for ELECTRICAL INSPECTORS
SE CABLE SIZES vs AMPS
UNDERGROUND SERVICE LATERALS
VOLTS / AMPS MEASUREMENT EQUIP
VOLTAGE MEASUREMENT METHODS
WIND ENERGY SYSTEMS
WIND TURBINES & LIGHTNING
ZINSCO SYLVANIA ELECTRICAL PANELS
This article series discusses the electrical, fire, and shock hazards associated with Zinsco electrical components, circuit breakers, electrical panels, including certain Sylvania electrical panels and breakers which are in fact of the same product design and origin. Page top photo of a Zinsco electrical panel provided by Washington state electrician J. P. Simmons
Green links show where you are. © Copyright 2014 InspectApedia.com, All Rights Reserved.
How and Where to Report Zinsco or Sylvania Electrical Equipment Failures to the U.S. Consumer Product Safety Commission
Dangerous Product Reports to the US CPSC: To report a dangerous product or a product-related injury, call CPSC's hotline at (800) 638-2772 or CPSC's teletypewriter at (800) 638-8270, or visit CPSC's web site at SaferProducts.gov.
You can use this CPSC web page to report Zinsco or Sylvania-Zinsco equipment failures and problems.
Please also report incidents to the InspectAPedia. com Editor.
How and Where to Report Zinsco or Sylvania Electrical Equipment Failures to the Website Author for Compilation
Submissions of field failure reports and failure photographs wanted. Contact the web author
Visual Inspection of Zinsco Panels Will Not Reliably Show Unsafe Conditions
Most of the time we check a Zinsco/Sylvania panel it looks great to the naked eye even with the cover off. There may be no obvious heat damage or signs of conductor damage. Home inspectors who comply with the ASHI or other Standards of Practice will remove the electric panel cover but they will not remove the circuit breakers themselves nor perform any other disassembly of electrical panel components. This restriction is established for the safety of the inspector who will not usually have the same level of electrical training as a licensed electrician.
Inspecting in this manner will usually not disclose damage even though very significant damage such as overheated connections, blown-out circuit breakers, or other failures may be present. Many of the panels we see do not have a main breaker so the only way to disconnect all the power is to have the meter pulled out by the power company - a step well beyond the scope of a home inspection.
Inspection of Zinsco Electrical Panels Might Actually Increase the Risk of a Future Failure
Many times when a licensed electrician pulls out the breakers, the breakers and bussing are damaged. I [J. Simmons] have personally seen them in such poor condition that the part of the breaker that pushes onto the bussing has become welded to the buss. The breaker actually broke apart with the connection staying on the buss and the rest of the breaker coming out) when I tried to remove it.
How Often do Experts find Damaged Zinsco Electrical Equipment
We see damage in about 25% of the Zinsco/Sylvania panels that are checked. The problem occurs mostly on circuit breakers feeding circuits that have a steady heavy load on them (like heaters, hot water tank, dryer), and on circuits that are often overloaded such as circuits that supply the kitchen or bathroom.
In houses with Zinsco/Sylvania electrical panels and circuit breakers, I [Simmons] have tested these circuits with up to 30 amps on a 20 amp circuit breaker. The Zinsco circuit breaker will carry the overload for a long time without tripping. This causes the connection to heat up and start arcing to the buss bar. The problem is primarily in the panels with aluminum buss bars, but also has been seen in the ones with copper buss. Moisture seems to accelerate the process.
Recommended Home Inspection Report Warning Language for Zinsco Electrical Panels & Circuit Breakers
These circuit breakers are very poor quality and do not provide a safe level of over current or short circuit protection. In our opinion [J. Simmons and D. Friedman], home inspectors who observe Zinsco or Sylvania-Zinsco electrical equipment in a home should warn the homeowner that
A Zinsco TM or GTE-Sylvania™ -Zinsco™ [or Kearney™] electrical panel is installed in this building. Serious electrical hazards may be present in the electrical panel which could result in overheating, fire, or inability to turn off the electrical power in the home. A licensed electrician who is familiar with this equipment should be called to inspect the panel for immediate fire and shock hazards.
While replacement of this equipment is not currently required by law, regardless of its visually-apparent condition, we recommend that homeowners replace this equipment. Significant expense may be involved.
With the exception of the more extensively-studied FPE Stab-Lok electrical panels, we have not received a significant number of field failure reports concerning any other electrical panel brands that also use aluminum parts and that are or were priced in the same range as this Zinsco equipment. This means homes with this equipment are at greater risk of fire or other electrical hazard.
Additional information about this hazards is available at an independent building failures research website: http://InspectAPedia.com/electric/Zinsco.htm
More in-depth, un-biased, expert information on these topics and on building defect inspection, diagnosis, & repair can be found at More Information below.
© Copyright 2010 Daniel Friedman, All Rights Reserved -MAKING
ELECTRONIC COPIES THIS WEB PAGE or PHOTOS IS PROHIBITED - but readers and inspectors are permitted to print and
pass on this information to interested parties, and you are encouraged to provide interested parties with the address
of this web pageInspectAPedia.com/electric/Zinsco.htm.
Link exchanges between industry experts and this page are welcome and will be provided if you contact the author.
Green link shows where you are in this article series.
Frequently Asked Questions (FAQs)
No FAQs have been posted for this page. Try the search box below or CONTACT US by email if you cannot find the answer you need at InspectApedia.
Try the search box just below or if you prefer, post a question or a comment in the Comments box below and we will respond promptly.
Search the InspectApedia website
HTML Comment Box is loading comments...
Technical Reviewers & References
Related Topics, found near the top of this page suggest articles closely related to this one.