Question? Just ask us!
Free Encyclopedia of Building & Environmental Inspection, Testing, Diagnosis, Repair
InspectAPedia ® Home
ELECTRICAL INSPECTION, DIAGNOSIS, REPAIR
AFCIs ARC FAULT CIRCUIT INTERRUPTERS
ALUMINUM WIRING HAZARDS & REPAIRS
AMPS VOLTS DETERMINATION
AMPERAGE MEASUREMENT METHODS
BOOKSTORE - ELECTRICAL
Classified CIRCUIT BREAKER WARNING
CORROSION in ELECTRICAL PANELS
CUTLER HAMMER PANEL FIRE
DEFINITIONS of ELECTRICAL TERMS
DIRECTORY OF ELECTRICIANS
DMM Digital Multimeter HOW TO USE
ELECTRIC PANEL AMPACITY
ELECTRIC PANEL INSPECTION
ELECTRICAL DISTRIBUTION PANELS
ELECTRICAL GROUND SYSTEM INSPECTION
FEDERAL PACIFIC FPE HAZARDS
GFCI PROTECTION,Testing GFCIs AFCIs
Hertz - Definitions of KHz MHz GHz THz
LIGHTING, EXTERIOR GUIDE
LIGHTING, INTERIOR GUIDE
LOW VOLTAGE BUILDING WIRING
MAIN ELECTRICAL DISCONNECT
MURRAY SIEMENS Recall
PHOTOVOLTAIC POWER SYSTEMS
PUSHMATIC - BULLDOG PANELS
RUST in ELECTRICAL PANELS
SAFETY for ELECTRICAL INSPECTORS
SE CABLE SIZES vs AMPS
SIEMENS MURRAY Recall
UNDERGROUND SERVICE LATERALS
VOLTS / AMPS MEASUREMENT EQUIP
VOLTAGE MEASUREMENT METHODS
ZINSCO SYLVANIA ELECTRICAL PANELS
This document describes how to identify Federal Pacific Stab-Lok® Electric Panels in buildings with special focus on the Federal NOARK Stab-Lok® Panelboard and the Federal NOARK Load Center. This is safety information for building inspectors, home buyers, home owners, electricians exploring the background of possible hazards associated with Federal Pacific Electric Stab-Lok® circuit breakers and service panels.
Replacement FPE Stab-Lok® circuit breakers are unlikely to reduce the failure risk of this equipment. We recommend that residential FPE Stab-Lok® electrical panels be replaced entirely or the entire panel bus assembly be replaced, regardless of FPE model number or FPE year of manufacture. We do not sell circuit breakers nor any other products. For more information see FPE REPLACEMENT PANELS and FPE REPLACEMENT BREAKERS. This page assists in identifying Federal Pacific Electric Stab-Lok® electrical panels and circuit breakers. More FPE information is in the links listed at Related Topics .
Green links show where you are. © Copyright 2014 InspectApedia.com, All Rights Reserved.
Photo Guide to Identification of Federal NOARK Electrical Panel Identification of Stab-Lok® Load Centers
Frequently Asked Questions (FAQs) about Federal No-Ark Stab-Lok FPE designs
Question: is the the history and hazard of Federal Noark panels related to Federal Pacific Electric Stab-Lok Panels?
My electrical panel does not say "Federal Pacific," though it looks like the Federal Pacific panels. It says "Federal NoArk Stab lok panel". Is it safe? Thank you for your help. Best wishes, M.H. 7/8/2013
Reply: Federal Noark electrical panel bus and breaker designs are Stab-Lok products and obtain the same hazard warnings.
[The Federal Noark electrical panel and circuit breaker product line] has the same design and same hazards. Search InspectAPedia for Federal Noark and you should find our article on that name brand.
Thank you, I searched InspectAPedia, but the only "article" I found was a series of pictures. It did not contain any information about the testing of Federal NoArk stab lok panels. It did not say what the years of manufacture were, nor did it say where these panels were made. Were the Federal Pacific panels made in New Jersey? It seems incongruous to name a company on the east coast "Pacific".
Thank you for this feedback. I will review that article with your comments in mind [and will make more clear that we are talking about the same product design, materials, producing company, and hazards as are discussed under related names for this product line such as Federal Pacific Electric Stab-Lok.
A look through FPE HISTORY for the list of company names, dates, locations and history helps clarify that Federal Noark and Federal Electric and Federal Pacific Electric are the same product line and company. Or if you prefer to go directly to an example source document that ties these company names together see U.S. Patent No. 3,093,773.
Lack of Testing of Federal Noark Equipment
The number of Federal Noark panels available for testing has been miniscule; but the history of their production, the company, the product, and its design are unambiguous. The variety of names on the product line reflects the history of names used by the company producing the product, not differences in product design nor performance. Because the breaker performance problems are traced to the circuit breaker design, bus design, and a history of dishonest test procedures, product labeling violations, as well as actual field failures, there should be no question remaining about the product.
Sources of Disinformation & Misinformation about FPE Stab-Lok & related product names
Unfortunately, and quite transparently, out of a wish to avoid liability, there has also been a long history of counter-PR released from the company, its successors, and even today, its remains. That misinformation has been the chief source of confusion among consumers about the hazards of the product.
While FPE and its interests made much of the CPSC's dropping of its original investigation of the Stab-Lok product failure history, the CPSC never said that it found the product to be safe. The US CPSC, in an effort to correct the record and to warn consumers, issued FPE INVESTIGATION CPSC Revised 2011.
Such advice is incorrect and can be dangerous. While we agree that it always makes sense to avoid overloading any electrical circuit, overcurrents and short circuits can still occur on any electrical circuit, even one into which nothing is plugged-in whatsoever! Should an overcurrent or short circuit occur on an electrical circuit, the consumer is relying on the circuit breaker to trip in time to prevent a fire.
Will avoiding an electrical circuit overload prevent an FPE Stab-Lok Failure and resulting fire?
No. Avoiding an overload may reduce but will not eliminate risk on an inadquately protected electrical circuit.
Avoiding an FPE-failure and its concomitant risks of a building fire by advising the consumer to "avoid overloading the circuit" is therefore as incoherent as telling occpuants in a car whose seat belts have been cut through to a mere single thread that the seatbelts are quite safe - as long as the vehicle avoids getting in an accident. Such misinformation, or in some cases deliberate disinformation, arise from a melange of conflicting interests (avoid liability, or in the case of some home inspectors, please real estate agents who are a source of referrals) or perhaps in a few cases out of simple ignorance.
We would much appreciate hearing any comments, critique, suggestions, or further questions that you may have after you've taken another look at this article as well as at the very long, documented, and well-tested information about the FP, FE, FPE, Federal Noark, product line.
Also, you are absolutely welcome to make PRINTED copies of any of our pages that you find useful, and to give them away to others where you find that useful. Our policy on use our website content, which does not permit people making online or electronic copies for the obvious reasons, can be read in more detail at COPYING
InspectAPedia is an independent publisher of building, environmental, and forensic inspection, diagnosis, and repair information provided free to the public - we have no business nor financial connection with any manufacturer or service provider discussed at our website.
We are dedicated to making our information as accurate, complete, useful, and unbiased as possible: we very much welcome critique, questions, or content suggestions for our web articles. Working together and exchanging information makes us better informed than any individual can be working alone.
Website content contributors whether it is just a small correction or an in-depth article series (which of course invites more search engine attention), are cited, quoted, and linked-to from the appropriate additional web pages and articles - which benefits us both.
A brief summary about InspectAPedia.com can be read at ABOUT
Questions & answers or comments about Federal NoArk electric panels and circuit breakers.
Try the search box just below or if you prefer, post a question or a comment in the Comments box below and we will respond promptly.
Search the InspectApedia website
HTML Comment Box is loading comments...
Technical Reviewers & References
Related Topics, found near the top of this page suggest articles closely related to this one.