Question? Just ask us!
Free Encyclopedia of Building & Environmental Inspection, Testing, Diagnosis, Repair
InspectAPedia ® Home
ELECTRICAL INSPECTION, DIAGNOSIS, REPAIR
AFCIs ARC FAULT CIRCUIT INTERRUPTERS
ALUMINUM WIRING HAZARDS & REPAIRS
AMPS VOLTS DETERMINATION
AMPERAGE MEASUREMENT METHODS
BOOKSTORE - ELECTRICAL
Classified CIRCUIT BREAKER WARNING
CORROSION in ELECTRICAL PANELS
CUTLER HAMMER PANEL FIRE
DEFINITIONS of ELECTRICAL TERMS
DIRECTORY OF ELECTRICIANS
DMM Digital Multimeter HOW TO USE
ELECTRIC PANEL AMPACITY
ELECTRIC PANEL INSPECTION
ELECTRICAL DISTRIBUTION PANELS
ELECTRICAL GROUND SYSTEM INSPECTION
FEDERAL PACIFIC FPE HAZARDS
GFCI PROTECTION,Testing GFCIs AFCIs
Hertz - Definitions of KHz MHz GHz THz
LIGHTING, EXTERIOR GUIDE
LIGHTING, INTERIOR GUIDE
LOW VOLTAGE BUILDING WIRING
MAIN ELECTRICAL DISCONNECT
MURRAY SIEMENS Recall
PHOTOVOLTAIC POWER SYSTEMS
PUSHMATIC - BULLDOG PANELS
RUST in ELECTRICAL PANELS
SAFETY for ELECTRICAL INSPECTORS
SE CABLE SIZES vs AMPS
SIEMENS MURRAY Recall
UNDERGROUND SERVICE LATERALS
VOLTS / AMPS MEASUREMENT EQUIP
VOLTAGE MEASUREMENT METHODS
ZINSCO SYLVANIA ELECTRICAL PANELS
Replacement FPE Stab-Lok® circuit breakers are unlikely to reduce the failure risk of this equipment. We recommend that residential FPE Stab-Lok® electrical panels be replaced entirely or the entire panel bus assembly be replaced, regardless of FPE model number or FPE year of manufacture. We do not sell circuit breakers nor any other products.
Green links show where you are. © Copyright 2015 InspectApedia.com, All Rights Reserved.
Photo Guide to Electrical Panel TOGGLE SWITCHES - photos of Characteristic FPE Stab-Lok® circuit breaker toggle switch handles
How to identify FPE Equipment: this article series describes how to identify Federal Pacific Stab-Lok® Electric Panels and circuit breakers in buildings. It is information for building inspectors, home buyers, home owners, electricians exploring the background of possible hazards associated with Federal Pacific Electric Stab-Lok® circuit breakers and service panels.
Look for FPE characteristic circuit breaker toggle switch markings, shape, colors.
More examples are in the photos below as well as in some of the other Federal Pacific Electric and Federal Pioneer circuit breaker and panel photos on this page.
[Click to enlarge any image]
Here is a photo of the 100-Amp main breaker from an FPE Stab-Lok® electrical panel. Notice that this breaker does not have the characteristic orange-red paint on the face of the toggle switches.
At left notice the "hexagonal" cross section of the toggle switch on this pre-1970 FPE Stab-Lok® circuit breaker. This hexagonal detail is characteristic of earlier FPE Stab-Lok® equipment.
Photo courtesy of electrical panel researcher David Carrier.
Photo of a Stab-Lok® panel apparent bus overheating or corrosion. This California FPE Panel shows characteristic FPE Stab-Lok® circuit breakers that can be recognized even from a distance.
Interesting Camouflaged FPE Stab-Lok® breaker (of unknown vintage) used alone in a 1950's house in Florida, note the clearly-legible name on the paper label.
This circuit breaker is probably a "one-off" experimental unit which, in that case, would never have been intended for sale, but which might have been brought out of the factory by a worker.
On occasion a Federal Pacific Stab-Lok® Electrical Panel or Breaker manufacturing factory worker might experiment with a mix of plastics in the circuit breaker case molding machine - thanks to J. Bolton, the Inspectigator or select a topic from the More Reading links shown below.
Continue reading at FEDERAL NOARK PANELS or select a topic from the More Reading links shown below.
Suggested citation for this web page
Green link shows where you are in this article series.
Frequently Asked Questions (FAQs)
No FAQs have been posted for this page. Try the search box below or CONTACT US by email if you cannot find the answer you need at InspectApedia.
Use the "Click to Show or Hide FAQs" link just above to see recently-posted questions, comments, replies, try the search box just below, or if you prefer, post a question or comment in the Comments box below and we will respond promptly.
Search the InspectApedia website
HTML Comment Box is loading comments...
Technical Reviewers & References