Question? Just ask us!
Free Encyclopedia of Building & Environmental Inspection, Testing, Diagnosis, Repair
InspectAPedia ® Home
ELECTRICAL INSPECTION, DIAGNOSIS, REPAIR
AFCIs ARC FAULT CIRCUIT INTERRUPTERS
ALUMINUM WIRING HAZARDS & REPAIRS
AMPS VOLTS DETERMINATION
AMPERAGE MEASUREMENT METHODS
BOOKSTORE - ELECTRICAL
Classified CIRCUIT BREAKER WARNING
CORROSION in ELECTRICAL PANELS
CUTLER HAMMER PANEL FIRE
DEFINITIONS of ELECTRICAL TERMS
DIRECTORY OF ELECTRICIANS
DMM Digital Multimeter HOW TO USE
ELECTRIC PANEL AMPACITY
ELECTRIC PANEL INSPECTION
ELECTRICAL DISTRIBUTION PANELS
ELECTRICAL GROUND SYSTEM INSPECTION
FEDERAL PACIFIC FPE HAZARDS
GFCI PROTECTION,Testing GFCIs AFCIs
Hertz - Definitions of KHz MHz GHz THz
LIGHTING, EXTERIOR GUIDE
LIGHTING, INTERIOR GUIDE
LOW VOLTAGE BUILDING WIRING
MAIN ELECTRICAL DISCONNECT
MURRAY SIEMENS Recall
PHOTOVOLTAIC POWER SYSTEMS
PUSHMATIC - BULLDOG PANELS
RUST in ELECTRICAL PANELS
SAFETY for ELECTRICAL INSPECTORS
SE CABLE SIZES vs AMPS
SIEMENS MURRAY Recall
UNDERGROUND SERVICE LATERALS
VOLTS / AMPS MEASUREMENT EQUIP
VOLTAGE MEASUREMENT METHODS
ZINSCO SYLVANIA ELECTRICAL PANELS
Identify FPE Stab Lok when there are no labels: this document describes how to identify Federal Pacific Stab-Lok® Electric Panels when there are no markings or labels visible on the panel or its cover, and when you do not see labels on the equipment. .
Green links show where you are. © Copyright 2014 InspectApedia.com, All Rights Reserved.
IF NO LABELS - What if there are no labels on my FPE Electric panel? How can I tell if it is a "Stab-Lok® " or Federal Pacific Electric or Federal Pioneer model panel?
Pictures of the FPE Stab-Lok® E-Bus Design
Watch out: SAFETY WARNING - FATAL SHOCK HAZARD - If it is necessary to remove an electric panel cover to inspect the panel interior, buses, or other components, you should hire a licensed electrician for that purpose. Unless you are a licensed electrician, DO NOT REMOVE ELECTRIC PANEL COVERS, DO NOT INSERT TOOLS INTO ELECTRIC PANELS, DO NOT TOUCH LIVE ELECTRICAL PARTS such as screws, buses, bare wires, or anything that is inside of the electric panel.
Federal Pacific Stab-Lok® Electrical Panel Breaker Bus Designs Can Identify FPE Equipment
Photographs of the FPE Stab-Lok® "F" Bus Design
The shock hazard warning issued above does not prohibit unlatching and swinging open the normal hinged panel covers provided for use by the homeowner to permit access to circuit breaker switches themselves.
The warning refers to disassembling, unscrewing, or otherwise modifying or operating on an electric panel.
Live wires and contacts inside of an electric panel can, if touched, cause fatal shock - death. If you are uncertain of what is safe to touch, do not touch any part of the equipment.
Our photograph at left (and also the one at page top) illustrate the "F" shaped cutout or opening in FPE Stab-Lok® electrical panels or in other words, the "F-bus" design.
More Details of how to recognize FPE Stab-Lok® panel bus designs are given at FPE PANEL BUS DESIGNS
Canadian FP (Federal Pioneer) electrical panels were made to the same design and specifications and look the same, have an identical bus design (not visible without disassembly), but are labeled "Federal Pioneer" instead of Federal Pacific Electric.
Watch out: Safety warning - while opening the hinged door provided for consumer use to access and reset the breakers is permitted, because there is risk of dangerous or even fatal electric shock in any electrical panel interior, only an expert should actually remove the front cover.
Our FPE Stab-Lok® breaker photo (left) illustrates the circuit breaker connector that "stabs" into the electrical panel power bus openings illustrated above.
Readers of this article should also see Federal Pacific Electric Panels: Fires Waiting to Happen and The Federal Pacific Electric FPE Panel/Breaker Hazard Summary - the main FPE Hazard Website.
Frequently Asked Questions (FAQs) about how to identify FPE Federal Pacific Federal Electric Federal Noark and similar electrical panels
Questions & answers or comments about how to identify FPE Stab-Lok® equipment when there are no labels or written id information .
Try the search box just below or if you prefer, post a question or a comment in the Comments box below and we will respond promptly.
Search the InspectApedia website
HTML Comment Box is loading comments...
Technical Reviewers & References
Related Topics, found near the top of this page suggest articles closely related to this one.