Question? Just ask us!
Free Encyclopedia of Building & Environmental Inspection, Testing, Diagnosis, Repair
InspectAPedia ® Home
ELECTRICAL INSPECTION, DIAGNOSIS, REPAIR
AFCIs ARC FAULT CIRCUIT INTERRUPTERS
ALUMINUM WIRING HAZARDS & REPAIRS
AMPS VOLTS DETERMINATION
AMPERAGE MEASUREMENT METHODS
BOOKSTORE - ELECTRICAL
Classified CIRCUIT BREAKER WARNING
CORROSION in ELECTRICAL PANELS
CUTLER HAMMER PANEL FIRE
DEFINITIONS of ELECTRICAL TERMS
DIRECTORY OF ELECTRICIANS
DMM Digital Multimeter HOW TO USE
ELECTRIC PANEL AMPACITY
ELECTRIC PANEL INSPECTION
ELECTRICAL DISTRIBUTION PANELS
ELECTRICAL GROUND SYSTEM INSPECTION
FEDERAL PACIFIC FPE HAZARDS
GFCI PROTECTION,Testing GFCIs AFCIs
Hertz - Definitions of KHz MHz GHz THz
LIGHTING, EXTERIOR GUIDE
LIGHTING, INTERIOR GUIDE
LOW VOLTAGE BUILDING WIRING
MAIN ELECTRICAL DISCONNECT
MURRAY SIEMENS Recall
PHOTOVOLTAIC POWER SYSTEMS
PUSHMATIC - BULLDOG PANELS
RUST in ELECTRICAL PANELS
SAFETY for ELECTRICAL INSPECTORS
SE CABLE SIZES vs AMPS
SIEMENS MURRAY Recall
UNDERGROUND SERVICE LATERALS
VOLTS / AMPS MEASUREMENT EQUIP
VOLTAGE MEASUREMENT METHODS
ZINSCO SYLVANIA ELECTRICAL PANELS
Does age matter when evaluating FPE Stab-Lok® elecrical panels or circuit breakrs? Is Federal Electric Pacific Stab-Lok® design equipment safer if made during certain years?
Replacement FPE Stab-Lok® circuit breakers are unlikely to reduce the failure risk of this equipment. We recommend that residential FPE Stab-Lok® electrical panels be replaced entirely or the entire panel bus assembly be replaced, regardless of FPE model number or FPE year of manufacture. We do not sell circuit breakers nor any other products.
Green links show where you are. © Copyright 2014 InspectApedia.com, All Rights Reserved.
AGE MATTERS? - Does the age of Federal Pacific Electric Stab-Lok® Electric Panels make a difference in the safety concerns?
The following is a personal opinion by the website author: From my knowledge of the history, pattern, and nature of FPE manufacturing and management difficulties, and from a study of the nature of the cause of the fail-to-trip problem, bus connection problems, overheating and fire reports, as well as the history of how the product was made, on-the-fly un-approved changes, label swapping, and other troubles, it appears that the entire FPE-Stab-Lok® product line may have had defects, labeling errors, safety, or other performance issues for both commercial and residential equipment, where circuit breakers and panels are concerned. (I do not have similar criticism of the older FUSE equipment).
However we have test data only for the FPE Stab-Lok® series of residential electrical panels and circuit breakers. The "Stab-Lok® " product involves a specific electrical panel, bus, and circuit breaker design. Therefore the FPE Stab-Lok® Panel Website only includes research and warnings for this specific product line.
People write to ask if their Federal Pacific Electric equipment is "OK" based on a particular age of their house and presumably of the panel. "Year" criteria is not useful in evaluating risk as there is no data that demonstrates that FPE Stab-Lok® equipment is better or worse after specific dates.
Furthermore, the age of a piece of equipment installed in a house can be older or newer than the age of the house itself.
Frequently Asked Questions (FAQs) about electrical panel age effects
Questions & answers or comments about the effects of electrical panel age and FPE Stab-Lok® circuit breaker & panel hazards.
Try the search box just below or if you prefer, post a question or a comment in the Comments box below and we will respond promptly.
Search the InspectApedia website
HTML Comment Box is loading comments...
Technical Reviewers & References
Related Topics, found near the top of this page suggest articles closely related to this one.