Question? Just ask us!
Free Encyclopedia of Building & Environmental Inspection, Testing, Diagnosis, Repair
InspectAPedia ® Home
ELECTRICAL INSPECTION, DIAGNOSIS, REPAIR
AFCIs ARC FAULT CIRCUIT INTERRUPTERS
ALUMINUM WIRING HAZARDS & REPAIRS
AMPS VOLTS DETERMINATION
AMPERAGE MEASUREMENT METHODS
BOOKSTORE - ELECTRICAL
Classified CIRCUIT BREAKER WARNING
CORROSION in ELECTRICAL PANELS
CUTLER HAMMER PANEL FIRE
DEFINITIONS of ELECTRICAL TERMS
DIRECTORY OF ELECTRICIANS
DMM Digital Multimeter HOW TO USE
ELECTRIC PANEL AMPACITY
ELECTRIC PANEL INSPECTION
ELECTRICAL DISTRIBUTION PANELS
ELECTRICAL GROUND SYSTEM INSPECTION
FEDERAL PACIFIC FPE HAZARDS
GFCI PROTECTION,Testing GFCIs AFCIs
Hertz - Definitions of KHz MHz GHz THz
LIGHTING, EXTERIOR GUIDE
LIGHTING, INTERIOR GUIDE
LOW VOLTAGE BUILDING WIRING
MAIN ELECTRICAL DISCONNECT
MURRAY SIEMENS Recall
PHOTOVOLTAIC POWER SYSTEMS
PUSHMATIC - BULLDOG PANELS
RUST in ELECTRICAL PANELS
SAFETY for ELECTRICAL INSPECTORS
SE CABLE SIZES vs AMPS
SIEMENS MURRAY Recall
UNDERGROUND SERVICE LATERALS
VOLTS / AMPS MEASUREMENT EQUIP
VOLTAGE MEASUREMENT METHODS
ZINSCO SYLVANIA ELECTRICAL PANELS
This document discusses the safety of older, "Pre-1970" Federal Pacific Stab-Lok® Circuit Breakers & Electric Panels in buildings. It is information for building inspectors, home buyers, home owners, electricians exploring the background of possible hazards associated with Federal Pacific Electric Stab-Lok® circuit breakers and service panels.
Green links show where you are. © Copyright 2014 InspectApedia.com, All Rights Reserved.
Watch out: Safety warning: while opening the hinged door provided for consumer use to access and reset the breakers is permitted, because there is risk of dangerous or even fatal electric shock in any electrical panel interior, only an expert should actually remove the front cover.
Question: Are pre-1970 FPE Stab-Lok® circuit breakers as unsafe as the later models?
As I searched InspectAPedia I see statements that ALL FPE breakers and panels must be replaced. However the vast majority, if not all of the problem reports that I have read are of FPE circuit breaker equipment installed in the 1970's early 1980's.
We live in a neighborhood built in the 1950's and my wife is a realtor. The houses here have the old 100amp brown FPE breakers with copper split busses. Is there data and problem reports that supports a higher than normal industry failure rate for 1950s manufactured FPE breakers and panels? Or is this a "guilty by 1970s association so all FPE breakers and panels are bad" thing.
-- Loren Schiele. BS EE
The photos below, courtesy of electrical panel researcher David Carrier, show older FPE Stab-Lok® circuit breakers that include the use of some copper components.
This 40-Amp two-pole circuit breaker, FPE Catalog No. 240, lacks an internal common trip mechanism, relying on mechanical linkage between the two breaker halves. Additional photos of FPE Stab-Lok® circuit breakers of various vintages including this pre-1970 set are at FPE BREAKER ID PHOTOS.
Only Limited Testing of Older Pre-1970 Equipment
Among the more than 1600 FPE Stab-Lok® breakers tested to date, there are too few of those with the "old" construction (brown case and/or hexagonal handle) tested to date to conclude that they are substantially different in performance.
Lack of Common Internal Trip Mechanism in Older Circuit Breakers
One significant difference is that the early 2-pole FPE Stab-Lok® breakers had linked handles but lacked an internal common trip mechanism.
The lack of a common-trip mechanism is today considered less safe, which is why the standards were changed to require it. At the same time, these do not have the jamming problem of the later FPE 2-pole breakers that is specifically attributed to the common trip mechanism.
Degradation of Electrical Equipment With Age
The FPE Stab-Lok® performance problems were not restricted to the 1970's and later production. While one could postulate that the quality control, tooling, etc. at the plant degraded with time, so that the early FPE Stab-Lok® breakers might be better than the average FPE, that is in part balanced by the fact that mechanical devices generally degrade with time, and the original FPE Stab-Lok® breakers are now headed toward 60 years in service.
There is also the question of added circuits and replacements
Busbar Contacts in Older FPE Stab-Lok® Panels
Further Study Needed on Older FPE Equipment - Rotating FPE Breaker Replacement & Free Testing Project
If there are enough interested and cooperative homeowners in the neighborhood, perhaps you could organize a rotating breaker substitution system that would allow Dr. Aronstein or our collaborating test engineer David Carrier to test the breakers and return them, so as to obtain the performance data that all of us are interested in.
Green link shows where you are in this article series.
Frequently Asked Questions (FAQs)
No FAQs have been posted for this page. Try the search box below or CONTACT US by email if you cannot find the answer you need at InspectApedia.
Questions & answers or comments about the performance & safety of olde3r FPE Stab-Lok® equipment - made before 1970.
Use the "Click to Show or Hide FAQs" link just above to see recently-posted questions, comments, replies, try the search box just below, or if you prefer, post a question or comment in the Comments box below and we will respond promptly.
Search the InspectApedia website
HTML Comment Box is loading comments...
Technical Reviewers & References