Free Encyclopedia of Building & Environmental Inspection, Testing, Diagnosis, Repair
Ask a Question or Search InspectAPedia
InspectAPedia ® Home
ELECTRICAL INSPECTION, DIAGNOSIS, REPAIR
AFCIs ARC FAULT CIRCUIT INTERRUPTERS
ALUMINUM WIRING HAZARDS & REPAIRS
AMPS VOLTS DETERMINATION
BOOKSTORE - ELECTRICAL
Classified CIRCUIT BREAKER WARNING
CORROSION in ELECTRICAL PANELS
CUTLER HAMMER PANEL FIRE
DEFINITIONS of ELECTRICAL TERMS
DIRECTORY OF ELECTRICIANS
DMM Digital Multimeter, How to Use
ELECTRIC PANEL AMPACITY
ELECTRIC PANEL INSPECTION
ELECTRICAL DISTRIBUTION PANELS
ELECTRICAL GROUND SYSTEM INSPECTION
FEDERAL PACIFIC FPE HAZARDS
GFCI PROTECTION,Testing GFCIs AFCIs
Hertz - Definitions of KHz MHz GHz THz
LIGHTING, EXTERIOR GUIDE
LIGHTING, INTERIOR GUIDE
LOW VOLTAGE BUILDING WIRING
MURRAY SIEMENS Recall
PHOTOVOLTAIC POWER SYSTEMS
PUSHMATIC - BULLDOG PANELS
RUST in ELECTRICAL PANELS
SAFETY for ELECTRICAL INSPECTORS
SE CABLE SIZES vs AMPS
SIEMENS MURRAY Recall
UNDERGROUND SERVICE LATERALS
VOLTS / AMPS MEASUREMENT EQUIP
ZINSCO SYLVANIA ELECTRICAL PANELS
Replacement FPE Stab-Lok® circuit breakers are unlikely to reduce the failure risk of this equipment. We recommend that residential FPE Stab-Lok® electrical panels be replaced entirely or the entire panel bus assembly be replaced, regardless of FPE model number or FPE year of manufacture. We do not sell circuit breakers nor any other products.
This web page explains the issues and recommends solutions for people looking for a replacement FPE Stab-Lok® circuit breaker. We do not sell circuit breakers nor any other products.
Green links show where you are. © Copyright 2013 InspectAPedia.com, All Rights Reserved. Author Daniel Friedman.
From Reliance Electric Company Date-Stamped July 7, 1980 Division of Product Def....Compliance and Enforcement, CPSC [United States Consumer Product Safety Commission] For more information contact: Ricard B. Ainsworth, Jr. (216) 266-5834
For release: Saturday, July 5, after 4 p.m.
Cleveland, Ohio -- Reliance Electric Company has notified the Consumer Product Safety Commission (CPSC) that it is investigating a possible defect in the past production of the Stab-Lok® line of two-pole, 220 volt circuit breakers made by its recently acquired subsidiary, Federal Pacific Electric Company, headquartered in Newark, New Jersey.
It appears that Underwriters Laboratories labels for most of FPE's circuit breakers were obtained through improper practices, a Reliance spokesperson said. Reliance emphasized that current production of these breakers meets the requirements of Underwriters Laboratories tests.
An in-house test by Reliance indicated the possible defect. Reliance has retained Southwest Research Institute, an independent testing laboratory, to conduct further tests.
Reliance has also identified similar problems with some three- pole Stab-Lok® and molded case circuit breakers. Further testing on these breakers is being conducted. These type circuit breakers are used predominantly in commercial and industrial applications.
Reliance and Federal Pacific Electric will work with the CPSC in determining whether further action is required.
Although Reliance has not determined whether a significant hazard exists with regard to these devices, the company has stopped its shipments of the product in question and has requested that distributors stop further sales until tests are completed and evaluated.
Frequently Asked Questions (FAQs)
Use the search box below to ask a question or to search the InspectApedia.com website.
Ask a Question or Enter Search Terms in the InspectApedia search box just below.
Technical Reviewers & References
Related Topics, found near the top of this page suggest articles closely related to this one.