Question? Just ask us!
Free Encyclopedia of Building & Environmental Inspection, Testing, Diagnosis, Repair
InspectAPedia ® Home
ENVIRONMENTAL HAZARDS - INSPECT, TEST, REMEDY
ACOUSTICAL SEALANT CHOICES
AGE of a BUILDING - how to determine
AIR BYPASS LEAKS
AIR LEAK DETECTION TOOLS
AIR LEAK MINIMIZATION
AIR LEAK SEALING PROCEDURE
AIR POLLUTANTS, COMMON INDOOR
ALLERGENS in BUILDINGS, RECOGNIZING
ANIMAL ALLERGENS / PET DANDER
APPLIANCE EFFICIENCY RATINGS
ARCHITECTURE & BUILDING COMPONENT ID
ASBESTOS CEILING TILES, Asbestos-Containing
ASBESTOS CEMENT ROOFING
ASBESTOS CEMENT SIDING
ASBESTOS DUCTS, HVAC
ASBESTOS-FREE INSULATION MATERIALS
ASBESTOS IDENTIFICATION IN buildings
ASBESTOS FLOORING HAZARD REDUCTION
ASBESTOS FLOORING REMOVAL GUIDE
ASBESTOS LIST of PRODUCTS
ASBESTOS MATERIAL REGULATIONS
ASBESTOS MATERIAL REGULATIONS Update
ASBESTOS MATERIAL REGULATIONS, OSHA
ASBESTOS PHOTO GUIDE to Materials
ASBESTOS REMOVAL, Amateur, Incomplete
ASBESTOS REMOVAL CERTIFICATIONS
ASBESTOS REMOVAL, Wetting Guidelines
ASBESTOS RISK ASSESSMENT
ASBESTOS TESTING LAB LIST
ASBESTOS UNDER the MICROSCOPE
ATTIC LEAKS, CONDENSATION & MOLD
BASEMENT HEAT LOSS
BUCKLED FOUNDATIONS due to INSULATION?
BUILDING NOISE DIAGNOSIS & CURE
CATHEDRAL CEILING INSULATION
CEILING FINISHES INTERIOR
CEILINGS, DROP or SUSPENDED PANEL
CEILINGS & WALLS, PLASTER TYPES
CERAMIC TILE FLOOR, WALL
CERAMIC TILE, ASBESTOS in?
CHIMNEY INSPECTION DIAGNOSIS & REPAIR
CHINESE DRYWALL HAZARDS
DEW POINT CALCULATION for WALLS
EFFLORESCENCE, Salts & White / Brown Deposits
FIBERGLASS INSULATION MOLD
FLOOR TILE HISTORY & INGREDIENTS
FLOOR TILES ASBESTOS
FLOOR TYPES & DEFECTS
HEAT LOSS in BUILDINGS
HOUSE DOCTOR, how-to be
HUMIDITY LEVEL TARGET
ICE DAM PREVENTION
INDOOR AIR QUALITY IMPROVEMENT GUIDE
INSULATION FACT SHEET- DOE
INSULATION IDENTIFICATION GUIDE
INSULATION R-Values & Properties
METAL LATH, PLASTER & STUCCO
METHANE GAS SOURCES
MOISTURE CONTROL in BUILDINGS
MOLD: A COMPLETE GUIDE TO MOLD
Museum Artifact Preservation
NOISE / SOUND DIAGNOSIS & CURE
ODORS GASES SMELLS, DIAGNOSIS & CURE
PAINT FALURE, DIAGNOSIS, CURE, PREVENTION
PLASTER & BEAVERBOARD & DRYWALL
PLASTER BULGES & PILLOWS
PLASTER LATH, METAL
PLASTER, LOOSE FALL HAZARDS
PLASTER TYPE IDENTIFICATION
PLASTER VENEER Best Practices
ROOF VENTILATION SPECIFICATIONS
SAFETY HAZARDS & INSPECTIONS
SEARS KIT HOUSES
SOUND CONTROL in buildings
SPLITS & CRACKS in STRUCTURAL WOOD BEAMS
STAIN DIAGNOSIS on BUILDING EXTERIORS
STAIN DIAGNOSIS on BUILDING INTERIORS
STUCCO WALL METHODS & INSTALLATION
STRUCTURAL DAMAGE PROBING
SWEATING (CONDENSATION) on PIPES, TANKS
Thermal Expansion Cracking of Brick
THERMAL EXPANSION of MATERIALS
THERMAL IMAGING, THERMOGRAPHY
THERMAL MASS in BUILDINGS
THERMAL TRACKING Indicates Heat Loss
VAPOR BARRIERS & CONDENSATION in BUILDINGS
VENTILATION in BUILDINGS
VINYL CHLORIDE HEALTH INFO
VOCs VOLATILE ORGANIC COMPOUNDS
WALL CONSTRUCTION BARRIER vs CAVITY
WATER ENTRY in buildings
WINDOWS & DOORS
WINTERIZE A BUILDING
WOOD Burning Heaters Fireplaces Stoves
WORLD TRADE CENTER 9-11 DUST PHOTOS
Transite HVAC air ducts: this article explains the potential hazards of transite (cement asbestos) air ducts - asbestos fiber release, radon, and indoor air quality concerns, and duct collapse when transite air ducts are is found in buildings. Transite pipe, an asbestos-cement product, was used for HVAC ducts and for chimney or flue material to vent gas-fired appliances. Cement-asbestos transite pipe may also have been used for water piping in some communities. We discuss how to identify cement asbestos transite air ducts, what the safety & health hazards are, how to seal or abandon the ductwork, & alternative approaches. This document assists building buyers, owners or inspectors who need to identify asbestos materials (or probable-asbestos) in buildings by simple visual inspection.
Green links show where you are. © Copyright 2014 InspectApedia.com, All Rights Reserved.
Transite ducts used for HVAC air flow, especially when used buried in building
concrete floors or slabs, may break, collapse, leak water in (forming a mold and bacterial reservoir in the HVAC system,
or may release asbestos and other particles in building air when the HVAC system is operating.
The photograph above shows a transite cement asbestos heating duct in a carpeted floor slab. We recommend that in-slab heating or air conditioning ducts made of transite be sealed and abandoned, and alternate heat sources installed. This improvement removes an asbestos hazard, a flooded duct and mold hazard, and in some locales, also a radon gas entry point.
The photograph shows the edges as well as surface of the transite material. Transite pipe HVAC ducts get quite dirty and are not always easy to identify. [Photo and comments on transite in-slab HVAC ducts courtesy of Roger Hankey, a Minnesota home inspector.]
Incorrect spellings of transite asbestos piping or transite duct material that we've seen include transit pipe, transit ducts, transite chimneys, transide pipe, transide ducts, and transight pipe or transight ducts. "Transite" is the correct spelling.
There are also duct-sealants that some contractors offer as an in-duct sealant/spray. The contractor extends a spray wand into the HVAC ducts to deliver a coating that, if perfectly successful, can prevent or at least reduce the risk of asbestos fiber release into the building air. And Andrew Oberta has described standards methods for repairing asbestos-cement products including underground transite piping.
A down-side with in-slab ductwork is the difficulty in accessing for application of the spray and difficulty in inspection in the future to see what's going on inside the duct: collapsing walls, sealant falling off of duct interior, flooding, mold, asbestos-releasing scraps, rodents, etc.
Our in-slab air duct photo (left) shows evidence of a history of floods in the duct system as well as rodents (the rodent poison).
A second concern is that even if the coated transite air duct interior surfaces appear to have been treated successfully, especially with in-slab ducts (SLAB DUCTWORK) we are not assured that the in-slab ducts remain clean, dry, and undamaged in the future nor that the transite duct interior coating remains bonded to the duct surfaces.
Green link shows where you are in this article series.
Frequently Asked Questions (FAQs)
Question: can I seal a crack in a transite HVAC duct?
Can a crack in a transite HVAC "duct" be sealed or repaired. I am having foundation issues with my slab on grade living room and one of the ducts is cracked. - Brad 8/6/11
Brad transite is a cementious product. It could be "repaired" using a bonding agent and high-portland content patching cement, and perhaps even duct seal.
Question: Water leaked into our transite air ducts - is this a problem?
I had some water get into my transite pipe buried into the slab of my house. I stopped the water by putting a new cement slab and redirecting the water. I immediately dried it up with a wet vac and kept the air conditioning on. I obviously have a leak in the pipe and have noticed some debris which I had removed by a HVAC vacuum company. I was told by an inspector when I bought the house that the transite probably had asbestos. Is this a problem? What should I do ? - Jack 9/22/12
Jack: I'm not sure which concern or problem you were asking about.
Basically if you abandon an in-slab transite pipe duct and seal the floor (you added another layer of concrete over your original floor slab) so that it can't easily send radon, rats, or mold into the building, it's not much of a concern - the cement-asbestos material won't move up through the new slab and thus won't be an ongoing asbestos hazard.
Your inspector, by saying that transite "probably had asbestos" was perhaps trying to please the seller and real estate agent from whom s/he receives referrals. Transite HVAC ducts are a cement-asbestos product and contain about 50% asbestos materials (fibers and powder filler) by volume.
Because it's in a cementious form the transite duct material is not normally friable so is less likely to release significant levels of asbestos into building air than softer asbestos materials such as asbestos pipe or boiler insulation. But when water-damaged or mechanically damaged, the asbestos release hazard from transite ducts can increase significantly.
What should a homeowner do about a transite air duct system? Is it a health hazard? I have two 12 - 15 foot lengths of HVAC ducts under a slab portion of my home. The ducts look to be in good shape through visual inspection from the floor vents with the exception of one crack (see post and answer below). If I want to stop using the ducts, what should I do as far as sealing them off from the furnace? I have installed a gas burning insert in the room so I can get away without using the ducts. Any help would be greatly appreciated. - Brad 6/11/12
If you abandon use of a transite duct, and provided it's not damaged so as to have become friable (releasing dust, easily crumbled between your fingers) it can be left in place - it's not "radioactive" - and is better left undisturbed. Don't run power tools, saws, grinders, etc. on cement asbestos material. But in the article above we give some reasons why in-slab air ducts of any sort present indoor air quality risks and hazards from future and un-discovered flooding, rodents, mold, etc. Add to that the risk of softening (asbestos fiber release) from water or moisture condensation in the ductwork, and the collapse risk. I'd prefer to abandon the in-slab ducts (SLAB DUCTWORK) and seal off those supply registers.
With that approach, and as long as there are not other slab cracks that leak contaminants into the building, it may not be necessary to try fill the entire in-slab duct with cement or other fillers, and the material can safely be left in place.
Questions & answers or comments about transite air ducts: asbestos cement air duct issues.
Try the search box just below or if you prefer, post a question or a comment in the Comments box below and we will respond promptly.
Search the InspectApedia website
HTML Comment Box is loading comments...
Technical Reviewers & References
Related Topics, found near the top of this page suggest articles closely related to this one.