Question? Just ask us!
Free Encyclopedia of Building & Environmental Inspection, Testing, Diagnosis, Repair
InspectAPedia ® Home
ENVIRONMENTAL HAZARDS - INSPECT, TEST, REMEDY
AGE of a BUILDING - how to determine
AIR POLLUTANTS, COMMON INDOOR
ASBESTOS-FREE INSULATION MATERIALS
ASBESTOS IDENTIFICATION IN buildings
ASBESTOS REMOVAL GUIDE
ASBESTOS TESTING LAB LIST
CEILING FINISHES INTERIOR
CEILINGS, DROP or SUSPENDED PANEL
CEILINGS & WALLS, PLASTER TYPES
CHINESE DRYWALL HAZARDS
EFFLORESCENCE, Salts & White / Brown Deposits
FLOOR TILE HISTORY & INGREDIENTS
FLOOR TILES ASBESTOS
FLOOR TYPES & DEFECTS
HOUSE DOCTOR, how-to be
INDOOR AIR QUALITY IMPROVEMENT GUIDE
INSULATION IDENTIFICATION GUIDE
METAL LATH, PLASTER & STUCCO
Museum Artifact Preservation
NOISE / SOUND DIAGNOSIS & CURE
PLASTER & BEAVERBOARD & DRYWALL
PLASTER TYPE IDENTIFICATION
SAFETY HAZARDS & INSPECTIONS
STUCCO WALL METHODS & INSTALLATION
VINYL CHLORIDE HEALTH INFO
VOCs VOLATILE ORGANIC COMPOUNDS
WORLD TRADE CENTER 9-11 DUST PHOTOS
Transite Asbestos Cement Pipes: this article assists in the recognition of transite pipe used for water pipes, and discusses potential hazards of this material when it is found in buildings. Transite pipe is an asbestos-cement product which was used for both HVAC ducts and for chimney or flue material to vent gas-fired appliances as well as for water piping in some communities.
This article explains the potential health hazards (asbestos exposure by ingestion) as well as practical problems (fragility, collapse, expense of replacement) of cement asbestos transite pipe water piping and we provide citations to authoritative studies of this question. This document assists building buyers, owners or inspectors who need to identify asbestos materials (or probable-asbestos) in buildings by simple visual inspection. We provide photographs and descriptive text of asbestos insulation and other asbestos-containing products to permit identification of definite, probable, or possible asbestos materials in buildings.
Green links show where you are. © Copyright 2014 InspectApedia.com, All Rights Reserved.
Transite pipe or asbestos-cement pipes were used for water supply systems in some municipalities up into the 1970's in the U.S. and probably in other countries. In some cities (Ellwood PA for example), the transite water mains were found to be unable to reliably withstand high water pressures (up to 225 psi in Ellwood according to one of our readers) and the pipes were easily broken.
Asbestos fibers may be ingested from water supplied through transite water piping. Transite piping deteriorates over time, releasing asbestos fibers from the interior of the pipe into the drinking water flowing through that conduit. The level of health risk from ingested asbestos fibers is uncertain and probably low. An NIH report prepared by industry experts concluded:
Another study by Millette JR et als reported
While an expert lab test using polarized light microscopy may be needed to identify the specific type of asbestos fiber, or to identify the presence of asbestos in air dust or water samples, many asbestos-containing building products not only are obvious and easy to recognize, but since there were not other look-alike products that were not asbestos, a visual identification of this material can be virtually a certainty in many cases. Links to U.S. government and other authoritative research and advice are included.
A more immediate water quality hazard has been detected in some vinyl-lined transite water pipes - Tetrachloroethylene. A report on the Sandwich water district on Cape Cod in Massachusetts reported that
Leaks in transite water supply piping underground can result in substantial water losses in districts where this piping was used.
Locating transite water supply mains: We've been informed that excavators complain that its lack of metal makes locating transite water pipes difficult - one cannot use ordinary metal detectors.
Of course a buried pipe of non-metallic material might be located if it is possible to insert a sending probe inside its length but on a water main this procedure is impractical. Contractors joke that they find transite pipe by using the metal bucket of a backhoe as a pipe detector.
Replacement costs for transite water supply piping: because of its age, leaks, fragility, and difficulty of finding transite cement asbestos water supply mains and water piping without also damaging it at the same time, owners of properties and communities served by cement asbestos water pipes (transite) can expect to face increasing costs to replace that piping.
Asbestos fiber release hazards during removal of demolition of transite piping are discussed at TRANSITE PIPE CHIMNEYS & FLUES.
Incorrect spellings of transite piping or transite duct material that we've seen include transit pipe, transit ducts, Transide pipe, transide ducts, tranisite pipe, and transight pipe. "Transite" is the correct spelling.
Green link shows where you are in this article series.
Frequently Asked Questions (FAQs)
No FAQs have been posted for this page. Try the search box below or CONTACT US by email if you cannot find the answer you need at InspectApedia.
Use the "Click to Show or Hide FAQs" link just above to see recently-posted questions, comments, replies, try the search box just below, or if you prefer, post a question or comment in the Comments box below and we will respond promptly.
Search the InspectApedia website
HTML Comment Box is loading comments...
Technical Reviewers & References