Question? Just ask us!
Free Encyclopedia of Building & Environmental Inspection, Testing, Diagnosis, Repair
InspectAPedia ® Home
ENVIRONMENTAL HAZARDS - INSPECT, TEST, REMEDY
ACCURACY vs PRECISION of MEASUREMENTS
AIR CLEANER PURIFIER TYPES
AIR LEAK DETECTION TOOLS
AIR POLLUTANTS, COMMON INDOOR
AIR QUALITY IMPROVEMENT STRATEGIES
ANIMAL or URINE ODOR SOURCE DETECTION
BACKDRAFTING HEATING EQUIPMENT
BIBLIOGAPHY for ENVIRONMENTAL HEALTH, MOLD, IAQ
BIOGAS PRODUCTION & USE
BLOWER DOORS & AIR INFILTRATION
BOOKSTORE - ENVIRONMENTAL
BUILDING SAFETY HAZARDS GUIDE
CARPETING & INDOOR AIR QUALITY
CHINESE DRYWALL HAZARDS
CHLORINE IN DRINKING WATER
COMBUSTION PRODUCTS & IAQ
COMBUSTION GASES & PARTICLE HAZARDS
CONDENSATION or SWEATING PIPES, TANKS
CPSC Indoor Air Pollution Book Online Copy
DRAFT MEASUREMENT, CHIMNEYS & FLUES
DUST SAMPLING PROCEDURE
EMERGENCY RESPONSE, IAQ, GAS, MOLD
ENVIRO-SCARE - PUBLIC FEAR CYCLES
ENDOCRINE DISRUPTERS at BUILDINGS
Fireplaces & Woodstove Contaminants
FLAME COLOR, BLUE vs YELLOW COMBUSTION
Formaldehyde Gas Hazard Reduction
GAS DETECTION INSTRUMENTS
GAS LP & NATURAL GAS SAFETY HAZARDS
GAS PRESSURES LP vs NATURAL GAS
HEATING OIL EXPOSURE HAZARDS, LIMITS
HOUSE DUST ANALYSIS
HOUSE DUST COMPONENTS
HUMIDITY CONTROL & TARGETS INDOORS
HYDROGEN SULFIDE GAS
Indoor Air Pollution Book Online CPSC
INDOOR AIR QUALITY & HOUSE TIGHTNESS
INDOOR AIR QUALITY IMPROVEMENT GUIDE
LP & Natural Gas Pressures
GAS LP & NATURAL GAS SAFETY HAZARDS
MOLD ODORS, MUSTY SMELLS
MSDS MATERIAL SAFETY DATA SHEETS
MVOCs & MOLDY MUSTY ODORS
Museum Artifact Preservation
ODORS GASES SMELLS, DIAGNOSIS & CURE
ODORS IN WATER
OXYGEN - O2
PARTICLE SIZES & IAQ
PESTICIDE EXPOSURE HAZARDS
PLASTIC ODORS-SCREENS, SIDING
PLUMBING SYSTEM ODORS
PVC - VINYL BUILDING PRODUCTS
RADON HAZARD TESTS & MITIGATION
METHANE GAS HAZARDS
SEPTIC SYSTEM ODORS
SMELL PATCH TEST to Track Down Odors
SULPHUR & SEWER GAS SMELL SOURCES
UFFI UREA FORMALDEHYDE FOAM INSULATION
URETHANE FOAM Deterioration, Outgassing
VAPOR CONDENSATION & BUILDING SHEATHING
VENTILATION in BUILDINGS
VINYL SIDING or WINDOW PLASTIC ODORS
VOCs VOLATILE ORGANIC COMPOUNDS
WATER ODORS, CAUSE CURE
Carbon monoxide (CO) gas hazards home page: carbon monoxide alarms, effects, tests, exposure limits, medical effects. This article describes the toxicity and exposure limits for exposure to carbon monoxide gas (CO).
In companion articles we also describe procedures for inspecting buildings for evidence of carbon monoxide hazards, including visual clues that may suggest a safety problem even if CO testing is not detecting carbon monoxide at the time of the inspection. We describe carbon monoxide testing methods, the medical effects of carbon monoxide exposure, and we cite authorities who set the limits on carbon monoxide exposure in different environments.
We give references and explanation regarding Toxicity of Carbon Monoxide, based on literature search and including research on OSHA, NIOSH, and at the old Compuserve's Safety Forum. This is background information, obtained from expert sources. This text may assist readers in understanding these topics.
Green links show where you are. © Copyright 2014 InspectApedia.com, All Rights Reserved.
Guide to Inspecting buildings for Visible Evidence of Conditions Likely to Produce Dangerous Carbon Monoxide Gas
IF YOU SUSPECT CARBON MONOXIDE POISONING GO INTO FRESH AIR IMMEDIATELY and get others out of the building, then call your fire department or emergency services for help. Links on this page also direct the reader to carbon dioxide gas information in a separate document.
Seek prompt advice from your doctor or health/safety experts if you have any reason to be concerned about exposure to toxic gases. Carbon monoxide poisoning can be fatal but exposure at lower limits can produce flu-like symptoms and headaches that are often mistaken for ordinary illness.
The fact that you cannot see nor smell dangerous carbon monoxide gas does not mean that there is nothing to look for when assessing the safety of heating equipment. Not only are there easily spotted installation errors (the first list below), there may be more subtle but easily visible errors if you know what to look for (the second list below).
Safety Suggestions: Install Carbon Monoxide Detectors in addition to Smoke Detectors
Carbon monoxide detectors are inexpensive and readily available, both as a battery-operated unit and as a unit that plugs into an electrical outlet in the home. No home should be without this safety protection, and homes with gas-fired equipment (natural gas or LP propane), space heaters, or other sources of risk should be extra cautious. Smoke detectors do not protect against carbon monoxide poisoning, and the opposite is also true. Carbon monoxide detectors do not warn of smoke or fire.
Examples of visible building conditions risking carbon monoxide hazards
This is by no means the complete list of errors that can cause dangerous carbon monoxide exposure in buildings, but here are some common foul ups outside of the workplace that can cause dangerous levels of indoor carbon monoxide:
Other clues which can suggest a risk of carbon monoxide hazards in buildings
In addition to the installation of CO monitoring alarms in buildings, a variety of electronic and gas sampling equipment is available to make spot checks for hazardous gases. I have and have used a variety of these devices under a wide range of conditions.
While a "positive" indication of a gas is an important indicator of a hazard, a "negative" or "not found" result is nothing to rely on.
The fact that dangerous levels of CO are not present in a building at a particular instant is absolutely no guarantee that dangerous levels of CO (for example) may not occur even moments later. For example, opening a window, turning on a fan or clothes dryer, closing a door, and similar innocent acts can significantly change air flow, combustion air, and other building conditions.
Therefore spot tests for dangerous gases should not be relied upon to guarantee building safety. This is why the list of visual inspection items and proper heating equipment maintenance are so important.
Watch out: the immediate and most severe effect of carbon monoxide exposure and poisoning can be death, typically loss of consciousness followed by death. In a recent example of carbon monoxide fatality, the manager of a Legal Seafoods restaurant in Huntington Long Island (New York) died and twenty-seven others were sickened as a result of carbon monoxide poisoning traced to a faulty water heating equipment vent.
News media noted that while CO detectors are required in homes just about everywhere, laws requiring carbon monoxide detectors in the workplace are not (as of February 2014) in place in New York where this death occurred. The LA Times news report illustrates the pernicious odorless nature of carbon monoxide gas: when restaurant workers reported that the assistant-manager was unconscious, apparently from a head injury due to a fall, rescue workers, themselves sickened when working in the building, found the restaurant manager also unconscious, but he was later pronounced from carbon monoxide poisoning. - Los Angeles Times (2014)
Here we discuss the effects of CO exposure or chronic CO exposure at less severe levels when death, the ultimate penalty, has not been incurred.
Many sources I (DF) reviewed indicated that if carbon monoxide exposure was sub-acute, that is if the person did not lose consciousness and was removed from the CO exposure before losing consciousness, then any medical effects were temporary. Indeed detection of CO exposure at a hospital is problematic since CO leaves the bloodstream quickly once a person is exposed to normal air.
However there is evidence that lasting physical damage may occur from carbon monoxide exposure, though the popular press has not (2006) discussed the exposure level and duration necessary for these effects.
Heart muscle damage occurs from Carbon Monoxide (CO) exposure, screening recommended
31 January 2006 - The New York Times Science Section reports on a new study, released in JAMA's January 25 2006 Magazine Issue, and which indicated that people exposed to carbon monoxide suffer damage to their heart muscles and are at much greater risk for heart attacks in later years.
The Times article asserted that CO Poisoning results in 40,000 emergency visits a year in the United States - the most common accidental poisoning event in the U.S. with an annual average accidental death rate of about 1000 people and average suicidal death rate of about 2400 people. [U.S. CDC] Five percent of such patients die in the hospital. Research was not cited regarding sub acute exposures and exposures which do not result in a visit to a hospital. -- New York Times Science Section, January 31, 2006 p. F6, "After Crisis, Carbon Monoxide Still Takes a Toll."
The carbon monoxide exposure and heart muscle damage study was led by Christopher R. Henry, Minneapolis Heart Institute Foundation, in the current [Jan 2006] Journal of the American Medical Association The study examined the medical history of 230 people exposed to carbon monoxide and treated at hospital between 1994 and 2002, following their health to 2005.
After 7 1/2 years, in this otherwise low risk (of heart failure) population, 25% of the originally-surviving patients had died - a rate about three times the average heart failure death rate statistic. For people who had suffered heart muscle damage the mortality rate was 38% with half of the mortalities being (apparently) traced to cardiovascular problems.
The study concludes that people who are exposed to carbon monoxide should be screened for heart muscle damage. Heart muscle damage from CO poisoning (in the study) was characterized by elevated levels of cardiac troponin I (a type of protein) or creatine kinase-MB (a type of enzyme), and/or changes in diagnostic electrocardiogram (ECG). -- DJ Friedman paraphrasing the NY Times article and JAMA's news release regarding this study.
More references for this study:
Carbon Monoxide Poisoning Information From U.S. Army Field Manual 8-285:
Pathology of CO poisoning: Asphyxiation is caused by the inactivation of blood hemoglobin through a combination with CO. The resultant anoxia may produce nervous system changes. Postmortem examinations reveal little beyond the characteristic cherry red color of the blood and hemorrhages in the brain
Symptoms of CO poisoning: Carbon monoxide is very insidious in its action and poisoning may occur without appreciable initial signs. The symptoms progress from throbbing headaches, vertigo, yawning, and poor visual acuity, to the development of cherry red mucous membranes, weakness and coma, subnormal temperature, feeble pulse, and death.
Diagnosis of CO poisoning: The diagnosis is made from the
circumstances of exposure and the appearance of
Protection against CO poisoning: In general, exposure to CO should be avoided whenever possible. Adequate ventilation
should be provided for all enclosed spaces where CO
may be produced. The safety of air in the space for
people to breathe may be tested by standard CO indicator or detector devices. Individuals required to
Treatment for Carbon Monoxide Poisoning: Remove the victim to pure air. If respirations are weak or absent, begin assisted ventilation at once. Oxygen, if available, should be given by a face mask, preferably under pressure (up to 3 atmospheres). The patient should be kept warm and at rest (sedated, if necessary).
After resuscitation, initial supportive measures (such as the need for parenteral fluids and pressor drugs) can best be decided by the medical officer. Ordinarily, methylene blue solution, morphine, and atropine should NOT be used (TB MED 269).
Prognosis for people exposed to carbon monoxide poisoning: The longer the period of the coma,
This section has been moved to CO EXPOSURE LIMITS.To convert between % and ppm concentration of carbon monoxide air see CONVERT PPM to % CONCENTRATION
Carbon Monoxide Hazards - Carboxyhemoglobin levels and related health effects on people
Quoting from CPSC Indoor Air Pollution Book Online Copy
Carbon monoxide is an asphyxiant. An accumulation of this odorless, colorless gas may result in a varied constellation of symptoms deriving from the compound's affinity for and combination with hemoglobin, forming carboxyhemoglobin (COHb) and disrupting oxygen transport. The elderly, the fetus, and persons with cardiovascular and pulmonary diseases are particularly sensitive to elevated CO levels.
Methylene chloride, found in some common household products, such as paint strippers, can be metabolized to form carbon monoxide which combines with hemoglobin to form COHb. The following chart shows the relationship between CO concentrations and COHb levels in blood.
Tissues with the highest oxygen needs -- myocardium, brain, and exercising muscle -- are the first affected. Symptoms may mimic influenza and include fatigue, headache, dizziness, nausea and vomiting, cognitive impairment, and tachycardia. Retinal hemorrhage on funduscopic examination is an important diagnostic sign19, but COHb must be present before this finding can be made, and the diagnosis is not exclusive.
Studies involving controlled exposure have also shown that CO exposure shortens time to the onset of angina in exercising individuals with ischemic heart disease and decreases exercise tolerance in those with chronic obstructive pulmonary disease (COPD)20.
Note: Since CO poisoning can mimic influenza, the health care provider should be suspicious when an entire family exhibits such symptoms at the start of the heating season and symptoms persist with medical treatment and time.
carbon monoxide (CO) concentrations and carboxyhemoglobin (COHb) levels in blood
Table of Carboxyhemoglobin levels and related health effects on people
- SOURCE: a U.S. EPA (1979); b U.S. EPA (1985)
Nitrogen dioxide (NO) and sulfur dioxide (SO2) act mainly as irritants, affecting the mucosa of the eyes, nose, throat, and respiratory tract. Acute S02-related bronchial constriction may also occur in people with asthma or as a hypersensitivity reaction. Extremely high-dose exposure (as in a building fire) to N02 may result in pulmonary edema and diffuse lung injury. Continued exposure to high N02 levels can contribute to the development of acute or chronic bronchitis.
The relatively low water solubility of N02 results in minimal mucous membrane irritation of the upper airway. The principal site of toxicity is the lower respiratory tract. Recent studies indicate that low-level N02 exposure may cause increased bronchial reactivity in some asthmatics, decreased lung function in patients with chronic obstructive pulmonary disease, and an increased risk of respiratory infections, especially in young children.
The high water solubility of S02 causes it to be extremely irritating to the eyes and upper respiratory tract. Concentrations above six parts per million produce mucous membrane irritation. Epidemiologic studies indicate that chronic exposure to S02 is associated with increased respiratory symptoms and decrements in pulmonary function21. Clinical studies have found that some asthmatics respond with bronchoconstriction to even brief exposure to S02 levels as low as 0.4 parts per million22.
Continue reading at CO DETECTION OPTIONS or select a topic from the More Reading links shown below.
Suggested citation for this web page
Green link shows where you are in this article series.
Frequently Asked Questions (FAQs)
Question: My furnace service tech shut down my gas fired unit and says I need a new one. He said he could smell the CO and he wouldn't let me see his CO detector meter. Am I getting scammed?
I recently had a serviceman come to work on our natural gas furnace. When he was done he said that it was unsafe and needed to be replaced. He indicated that there was a high level of carbon monoxide (10,000 ppm) and shut the furnace off. I was made a little suspicious when he directed me to the exhaust pipe for the furnace and told me that the leak was so bad he could smell the CO. Since I always thought that CO is odourless that hit me a little strange. Plus the fact that he shoved the meter he was using under my nose for 3 seconds, not enough time for me to even read what was on the display.
His sales pitch was that the heat exchanged was clogged and needed to be replaced. Would there really be a CO level that high with a blocked exchanger or would it need to have a leak? Is it possible he is just trying to get some work out of me and hoping that I won't know any better? - Matthew
Reply: CO itself is odorless, but mixed in with combustion flue gases there would be a "flue gas" smell that someone might observe;
Watch out: Because of very serious life safety issues, do not turn the equipment back on.
But before replacing the gas furnace due to a carbon monoxide hazard I'd want an accurate diagnosis of just what the problem really is. Some problems might indeed justify a whole new heater, for example if the heat exchanger is perforated and if the cost to remove and replace the damaged heat exchanger is close to the cost of a whole new furnace, I'd consider going with the latter.
Other problems can cause flue gas spillage, equally dangerous, but with different solutions such as
I wouldn't insult the service tech when s/he may have been saving your life. But it's quite reasonable to ask that a carbon monoxide hazard be properly diagnosed and the evidence shown to you before you approve equipment replacement. After all, if you replace the gas furnace but leave an unsafe chimney in place a fatal carbon monoxide hazard could still be present.
Question: what does a utility company gas furnace safety check red-tag placed on our heating equipment mean?
When your Utility Company Technician performs a safety check of your gas furnace and determines it to be "unsafe/hazardous" plus "Shut off and capped due to recirculation," what exactly does this mean? - Chris
Reply: significance of red-tagging heating equipment - serious safety hazards are present and the equipment cannot be safely used until repaired
Chris: details may vary by state or municipality, but in general you are describing what the industry calls "red tagging" - a utility company or a heating contractor or even a licensed plumber or other trades expert who inspects heating equipment and finds that it is in a condition that is unsafe to operate should leave the system turned off and red-tagged with - usually - an attached red safety tag that indicates the date, the identity of the inspector, and the unsafe condition.
Question: asphyxiation hazards from gas fired water heaters?
what asphyxiation statistics are available for water heaters and water heater venting? - Dan Lewis
Dan that's an interesting way to put a carbon monoxide hazard question. Asphyxiation from CO depends on the concentration and exposure time, as we've published. One could calculate some theoretical carbon monoxide production rates from water heaters of various BTUH input ratings, but frankly in my opinion such data would be wild speculation. That's because the accumulation of a toxic gas in a building or any enclosed space depends on so many variables, such as:
Question: how to conduct a carbon monoxide CO survey of CO from street traffic?
I live on a residential street in the community of Glendale Ca. My street happens to be the only access to a regional park that was developed by the city. There are not only the hundreds of cars that access the park but also continual city large truck traffic and school busses that are creating high levels of CO. How can I get someone to take readings and correct this situation - Ken Steele
different times of day and in different seasons
All of that data, collected and prepared with sufficient professionalism to be credible would be very expensive, surely thousands of dollars.
Question: what might be causing a smell in my basement?
aerosol smell in basement - what could be the cause - 6/26/2012 Anonymous
Gee, Anon, I have no idea what an "aerosol" smell is. But you've posted the question on a carbon monoxide article - CO gas is odorless, though it can appear transported by gases from an oil or gas burner whose other combustion products may smell. For such a broad question, I suggest starting odor track-down at ODORS GASES SMELLS, DIAGNOSIS & CURE.
Question: gas odors in my heating system - no leak was detected, why does it still smell
I smell gas in my heating system.. I called for them to do a test... they said no alarm regeisterd a leak..
CO alarms and detectors respond to that gas - Carbon Monoxide, but not necessarily to other combustion gases that would be present in escaping heating system exhaust. So if your chimney or heater is leaking - still potentiallyi dangerous including as a possible fire or as a possible inadequate draft equipment problem - relying on a CO detector alone would be nonsense.
Ask your heating service manager to send an experienced technician to inspect your heating equipment for safe, proper operation.
Use the "Click to Show or Hide FAQs" link just above to see recently-posted questions, comments, replies, try the search box just below, or if you prefer, post a question or comment in the Comments box below and we will respond promptly.
Search the InspectApedia website
HTML Comment Box is loading comments...
Technical Reviewers & References
Gases: Toxic gases, indoor exposure levels, testing, identification