Question? Just ask us!
Free Encyclopedia of Building & Environmental Inspection, Testing, Diagnosis, Repair
InspectAPedia ® Home
AIR CONDITIONING & HEAT PUMP SYSTEMS
BACKDRAFTING HEATING EQUIPMENT
BACKUP HEAT for HEAT PUMPS
BANGING HEATING PIPES RADIATORS
BLOWER FAN OPERATION & TESTING
BOOKSTORE - InspectAPedia
BTU USAGE MONITORS
CARBON MONOXIDE - CO
CIRCULATOR PUMPS & RELAYS
DIAGNOSTIC GUIDES A/C / HEAT PUMP
DIAGNOSE & FIX HEATING PROBLEMS-BOILER
DIAGNOSE & FIX HEATING PROBLEMS-FURNACE
DIRECT VENTS / SIDE WALL VENTS
DRAFT REGULATORS, DAMPERS, BOOSTERS
DUCT SYSTEM & DUCT DEFECTS
ELECTRIC HEAT, DIAGNOSIS, REPAIR
ELECTRIC MOTOR DIAGNOSTIC GUIDE
FAN, AIR HANDLER BLOWER UNIT
FLOODED HEATING EQUIPMENT REPAIR
FLUE SIZE SPECIFICATIONS
GAS BURNER Flame & Noise Defects
GAS PIPING, VALVES, CONTROLS
GEOTHERMAL HEATING SYSTEMS
HEAT PUMPS, DIAGNOSIS, REPAIR
HEATING COST SAVINGS METHODS
HEATING OIL PIPING TROUBLES
HEATING OIL TANKS
HEATING SYSTEM NOISES
HEATING SYSTEM TYPES
GAS LP & NATURAL GAS SAFETY HAZARDS
MANUALS & PARTS GUIDES - HVAC
MIXING / ANTI-SCALD VALVES
MOTOR OVERLOAD RESET SWITCH
NOISE, HEATING SYSTEMS
ODORS FROM HEATING SYSTEMS
OIL FILTERS on HEATING EQUIPMENT
OIL FILL PIPE LEAKS
OIL SPILL CLEANUP / PREVENTION
PLASTIC Plexvent / Ultravent RECALL
PUFFBACKS, OIL BURNER
RELIEF VALVE LEAKS
Reset Switch - Heater Primary Control
RESET SWITCH - ELECTRIC MOTOR
Reset Switch - Stack Relays
SAFETY, HEATING INSPECTION
SAFETY RECALLS CHIMNEYS VENTS HEATERS
SOLAR HEATING SYSTEM DESIGNS
SOOT on OIL FIRED HEATING EQUIPMENT
STEAM HEATING SYSTEMS
THERMOSTATS, HEATING / COOLING
VIDEO GUIDES: Heating System Videos
WINTERIZE A BUILDING
WOOD, COAL STOVES & FIREPLACES
WOOD STOVE SAFETY
ZONE VALVES, HEATING
Hot water heating circulators or circulator pumps: install, troubleshoot, repair advice: this article series discusses Circulator Pumps: how to find, inspect, diagnose, and repair problems with Hot Water Heating System Circulator Pumps or circulator pump relay switches and controls. This article series answers most questions about Heating System Boiler Controls on central heating systems to aid in troubleshooting, inspection, diagnosis, and repairs.
Green links show where you are. © Copyright 2014 InspectApedia.com, All Rights Reserved.
Heating circulator pumps or "zone circulators" are used to force hot water from the heating boiler through radianting devices such as hot water baseboards or radiators. The circulator is switched on as needed or in some designs may be wired to run continuously.
Our photo at left of a red B&G heating circulator pump shows equipment more than twenty years old and still spinning along nicely. Proper installation, protection from leaks, and lubrication at annual service can give a long circulator life. Poor maintenance or improper installation can give less happy results.
[Click to enlarge any image]
After a brief introduction we describe what goes wrong (or how to get things to go right with heating zone circulator pumps. We also link to related articles for circulator choices, installation, troubleshooting, repair or replacement. Also see Checks for Circulator Operation.
Hot water may be circulated throughout multiple zones using a single circulator pump and individual zone flow control valves, or each heating zone may be built with its own individual circulator pump. Either approach to individual heating zone control can work just fine - using zone valves or using individual circulators.
Our photo above shows a single circulator system (no zone valves are in the photo - this may be a single-zone heat system) while at left our photograph shows a three-zone heating system with three B&G circulators in a home in Two Harbors, MN. You'll notice that one of the circulators has been replaced with a newer Bell & Gossett Circulator SLC-30.
Arguing whether multiple circulators or multiple zone valves is better is like arguing religion. Some heating contractors prefer using individual circulator pumps, one per zone, perhaps because they recall the history of unreliable zone valves which tended to clog or jam in some models by some manufacturers.
The "zone valve" gang retort that modern heating zone valves are as reliable or more reliable than [some models of] heating circulator pumps and that a zone valve costs a lot less. And adding zone control to an existing heating system may be less costly by adding a zone valve than by adding a circulator pump.
The heating system circulator pump, such as the trio of pumps shown at the top of this page, is used to move hot water from the heating boiler out through one or more loops of piping in a building, through heating devices such as radiators, heating baseboards, or convector units, then through return piping back to the heating boiler. When the water temperature drops to a pre-set level the heating boiler will re-heat the water.
[Click to enlarge any image]
The circulator relay is an electrical switch which, in response to a request for heat from a thermostat, turns on the circulator pump.
Some heating systems use a single circulator to move hot water through the building's heating devices. In a one-circulator system, the building may still divide its heat into various zones or sub-areas of individual heat control, by using either individual radiators in rooms or perhaps by using electrically controlled zone valves which open and close flow of hot water through sub-loops in the building heating piping.
Some heating systems use multiple circulators to provide heat to individual building areas or "zones". In this case each heating zone will have its own thermostat which, acting as a low-voltage "heat on-off switch" will turn on individual circulator pumps when heat is desired in that zone.
Less common are mixed heating zone systems in which multiple circulators are used but one or more of the circulators feeds a heating water pipe which is subsequently divided into additional sub-zones of heat control, each sub-zone being controlled by a zone valve.
Before assuming the heating system is not working when the thermostat is calling for heat, feel the radiators or baseboards to see if they are getting hot. On a call for heat at the thermostat, if the heating boiler is already hot (above the lower limit or cut-in temperature) then the circulator should turn on and move hot water to the baseboards or radiators.
Only after the boiler temperature drops below the cut-in temperature will the heating boiler turn on to re-heat the water. The connection between the thermostat and the heating boiler turning on or off is indirect. On most heating systems the thermostat turns the circulator pump on or off and the temperature of the heating water turns the heating boiler on or off.
If the boiler runs but the heating baseboard or radiators in an area do not get hot, the problem could be
If the heating boiler itself if does not turn on in a response to a call for heat see NO HEAT - BOILER.
Green link shows where you are in this article series.
Frequently Asked Questions (FAQs) about hot water heating circulator pumps & relays: installation, troubleshooting, repair
Question: circulator pump runs in short bursts
My furnace's circulator pump has been running in short bursts only lately, as opposed to full length cycles. It's a gas-fired hydronic system, a high efficient one w/ a Peerless Pinacle furnace. never experienced this before.Do you have any ideas? - mark4man 12/5/2012
First I'd check for a bad circulator control relay or possibly a thermostat wire that is intermittently shorting together. Occasionally a bad thermostat can also cause intermittent on-off calls for heat that can lead to odd circulator behavior.
A second set of possibilities might be a circulator pump that is binding or failing.
Try the search box just below or if you prefer, post a question or a comment in the Comments box below and we will respond promptly.
Search the InspectApedia website
HTML Comment Box is loading comments...
Technical Reviewers & References
Related Topics, found near the top of this page suggest articles closely related to this one.