How & Why to Open & Inspect Barometric Dampers & Draft Regulators on Oil Fired Heating Equipment
- DRAFT REGULATOR SOOT INSPECTION - CONTENTS: How to inspect the oil fired boiler or furnace flue through the barometric damper opening. How to interpret the level of soot or debris inside of oil fired heating equipment chimneys and vents. Draft Regulators & Barometric Dampers: A Guide to Barometric Dampers on Oil Fired Boilers, Furnaces, Water Heaters: inspection, adjustment, cleaning, troubleshooting. Cleaning & maintenance guide for heating systems
- POST a QUESTION or READ FAQs about Soot, Rust, Debris Seen in the Heating Flue
InspectAPedia tolerates no conflicts of interest. We have no relationship with advertisers, products, or services discussed at this website.
How to inspect through the heating appliance draft regulator or damper opening and why.
This article explains the procedure for opening and inspecting heating flues through the barometric damper or draft regulator, with particular emphasis on problems of soot & debris accumulation. Inspecting inside the boiler flue by the draft regulator opening gives very important information about the operating condition of oil fired heating equipment.
Green links show where you are. © Copyright 2015 InspectApedia.com, All Rights Reserved.
How to open and inspect a barometric damper for Inspection
This article discusses the simple but very useful step of just taking a quick look into the flue pipe through the barometric damper opening on oil fired heating equipment.
This article series answers most questions about central heating system troubleshooting, inspection, diagnosis, and repairs.
We describe how to inspect, troubleshoot and repair heating and air conditioning systems to inform home owners, buyers, and home inspectors of common heating system defects.
Details about draft control on oil fired heating systems (such as the oil fired heater shown in the photo above), including furnaces or boilers, are discussed
at DRAFT REGULATOR, DAMPER, BOOSTER on oil fired equipment.
At DRAFT MEASUREMENT, CHIMNEYS & FLUES we explain in detail how and where to actually measure the heating equipment draft in the course of checking on (or adjusting) the draft regulator.
The barometric damper or draft regulating device we are discussing here is normally used only on oil-fired heating equipment, not on gas-fired equipment. Details about draft control for gas fired heating systems, including furnaces or boilers, are discussed
at DRAFT HOOD, GAS HEATER on gas fired equipment.
Barometric dampers are devices used to regulate the draft on oil-fired heating equipment such as furnaces, boilers, or
On oil fired equipment the barometric damper, or draft regulator is typically a round Tee inserted in the flue vent connector between the heating appliance and the chimney. The face of the tee contains a round "door" with an adjustable weight.
In our photo you may not be able to open this barometric damper - it is improperly installed (out of level), and has been improperly modified, indicating a draft problem with this heating system or its chimney.
The implications of sealed barometric dampers are explained at DRAFT REGULATOR, DAMPER, BOOSTER for oil fired equipment.
How & Why Should You Open & Inspect the Barometric Damper:
When I, the author (DF) first owned a home with a heating boiler I was so terrified of this rumbling flickering box in my basement that I didn't even walk near it. That was a mistake.
And we wasted lots of money on oil before we learned that just a few simple visual checks can tell a lot about how well our heating equipment is running.
So don't worry: it's easy to perform this step - anyone can do it if a barometric damper is actually installed where it should be. Just gently push the hinged door open with a finger, and shine a good flashlight inside to see what you can see.
Warning: of course if your oil fired appliance has been running recently, these parts are HOT and you could get burned. If the damper door itself is hot you can still look inside - just use a screwdriver or wire to push the door open rather than your finger as shown in our photo at left.
A barometric damper installed on a horizontal flue pipe will give a good view of the cleanliness of the flue interior as well as clues about rust and damage in the flue.
A barometric damper installed on a vertical flue pipe may still give a good view of the top of the heating boiler, furnace, or water heater, where you may see accumulated soot or debris, rust stains, or perhaps better news.
Guide to Interpreting Debris Visible in the Chimney Through the Cleanout or Draft Regulator
Debris visible in the flue vent connector (stack pipe) visible through the barometric damper draft control opening. If you see soot, rust flakes, and debris in the flue vent connector this means that the heating system needs to be cleaned and serviced.
If the heating system has "just been serviced" this debris means that service was incomplete.
A flue vent connector ((also called the "stack pipe" or "flue pipe") is the metal pipe that connects the oil fired heating appliance to a chimney in order to safely vent combustion gases outdoors.
A proper service procedure for oil fired heating equipment includes removal of the flue vent connector and thorough cleaning of all debris from these components as well as a visual inspection of the condition of the chimney to which the flue vent connector joins to send combustion products outside.
Our photo shows what was probably several years of accumulated soot, rust flakes, and debris in the flue vent connector of an oil-fired horizontal furnace in a wet moldy crawlspace. The owner thought that his system, which was almost impossible to access, had "just been cleaned".
Opening this damper and looking inside meant we literally "hit pay dirt". The dirt meant that the system needed to be cleaned, that the owner was paying for heat, but the heat was going up the chimney, not into the home -- as we explain a bit more below.
A hard to access heating system in a cramped nasty area rarely receives thorough cleaning and service. That was the case for this system.
The Significance of Soot, Rust, Debris Seen in the Heating Flue
Question: What is the significance of those "rusty flakes" in the photo of crud visible at the chimney base or through the barometric damper
When I cleaned our flue exhaust, I found 'chips' in the soot like the ones in the image. What are those? I thought they might be from the flue lining chipping off. Are they? - Jessica
The "chips" such as those in our photo are typically soot-coated rust if the flue is metal, or soot-coated flakes of the glazing that was protecting the interior of a clay tile lined chimney flue.
The implications of the chips are that the hard glazed coating is being lost and thus the flue is deteriorating. Just how deteriorated the flue is we can't say from a photo like this one, but it is an indication that a more expert chimney inspection is in order. Use a professional chimney sweep and ask for a complete inspection of the chimney flue interior.
Loss of the chimney tile surface exposes the chimney flue liner to an ever increasing rate of deterioration, especially in climates of harsh or freezing weather. When the chimney liner deteriorates that means that eventually it can become unsafe, risking flue gas leaks, carbon monoxide poisoning, or even sparks and a building fire.
See CHIMNEY CLEANOUT DOORS for more examples of things you may find at the bottom of a chimney when inspecting through the cleanout door, or if it's a "dead end flue" you may find these inspecting through the flue vent connector or, if the flue is without bends and elbows, you may be able to inspect right through the barometric damper such as in our photo above.
When & Why is soot or crud in the oil fired boiler or furnace flue a problem?
When we look in to the flue close to the heating boiler or furnace, such as at the barometric damper shown at the top of this page, it's normal to see a thin coating of soot on the interior of the metal flue pipe (photo at left and photo at page top). .
But thick soot in the flue, the chimney, or inside of the boiler or furnace heat exchanger is a problem (photo below).
Our photo of a soot problem indicator (left) shows soot accumulating in the oil burner flue of the heating boiler connected to the "too short" chimney discussed at Chimney Height & Clearance.
This boiler has a history of blowing soot out of the boiler room and through the garage of the home it serves. This same soot is, of course, accumulating inside the heating boiler itself.
Because soot acts like an insulating coating, too much soot in a heating system causes both system operating problems problems and increased heating cost for the building.
These soot problems on oil fired heating equipment are discussed in detail at SOOT on OIL FIRED HEATING EQUIPMENT [link given just below]
Continue reading at SOOT on OIL FIRED HEATING EQUIPMENT or select a topic from the index of chimney articles listed above.
Or see CHIMNEY CLEANOUT DOORS for another spot where it may be possible to inspect for clues about the condition of a chimney and its safety.
Suggested citation for this web page
DRAFT REGULATOR SOOT INSPECTION at InspectApedia.com - online encyclopedia of building & environmental inspection, testing, diagnosis, repair, & problem prevention advice.
Green link shows where you are in this article series.
Frequently Asked Questions (FAQs)
Click to Show or Hide FAQs
No FAQs have been posted for this page. Try the search box below or CONTACT US by email if you cannot find the answer you need at InspectApedia.
Ask a Question or Search InspectApedia
Use the "Click to Show or Hide FAQs" link just above to see recently-posted questions, comments, replies, try the search box just below, or if you prefer, post a question or comment in the Comments box below and we will respond promptly.
Search the InspectApedia website
Technical Reviewers & References
Publisher's Google+ Page by Daniel Friedman
Click to Show or Hide Citations & References
- Carson, Dunlop & Associates Ltd., 120 Carlton Street Suite 407, Toronto ON M5A 4K2. (416) 964-9415 1-800-268-7070 firstname.lastname@example.org. The firm provides professional home inspection services & home inspection education & publications. Alan Carson is a past president of ASHI, the American Society of Home Inspectors. Thanks to Alan Carson and Bob Dunlop, for permission for InspectAPedia to use text excerpts from The Home Reference Book & illustrations from The Illustrated Home. Carson Dunlop Associates' home inspection education products include
- The ASHI-adopted Home Inspection Training Program, and Commercial Building Inspection Courses
- The Home Inspection Home Study Course, and publications such as
- The Home Reference Book, a reference & inspection report product for building owners & inspectors.
Special Offer: Carson Dunlop Associates offers InspectAPedia readers in the U.S.A. a ten percent discount on any number of copies of the Home Reference Book purchased as a single order. Just enter HRBUS10 in the order payment page "Promo/Redemption" space. Note: InspectAPedia.com ® editor Daniel Friedman is a contributing author.
- The Home Reference eBook, an electronic version for PCs, the iPad, iPhone, & Android smart phones
- Home Inspection Report writing materials, including the Horizon Software System that manages business operations, scheduling, & inspection report writing using Carson Dunlop's knowledge base & color images. The Horizon system runs on always-available cloud-based software for office computers, laptops, tablets, iPad, Android, & other smartphones.
- The Illustrated Home illustrates construction details and building components, a reference for owners & inspectors
- Dirk Faegre, Camden, Maine (207) 232-9494
is a certified BPI energy auditor and certified Envelope technician who kindly suggested draft regulator and flue vent connector inspection defect additions 6 Sept 09
- Thanks to reader Jessica for discussing chimney debris found by inspecting through the draft regulator - November 2010.
- Plastic Heating Vent Pipe & Other Heating Safety Recall Notices
- Weil McLain Model GV Gas Boiler/gas valve CPSC recall/repair
- Domestic and Commercial Oil Burners, Charles H. Burkhardt, McGraw Hill Book Company, New York 3rd Ed 1969.
- National Fuel Gas Code (Z223.1) $16.00 and National Fuel Gas Code Handbook (Z223.2) $47.00 American Gas Association (A.G.A.), 1515 Wilson Boulevard, Arlington, VA 22209 also available from National Fire Protection Association, Batterymarch Park, Quincy, MA 02269. Fundamentals of Gas Appliance Venting and Ventilation, 1985, American Gas Association Laboratories, Engineering Services Department. American Gas Association, 1515 Wilson Boulevard, Arlington, VA 22209. Catalog #XHO585. Reprinted 1989.
- The Steam Book, 1984, Training and Education Department, Fluid Handling Division, ITT [probably out of print, possibly available from several home inspection supply companies] Fuel Oil and Oil Heat Magazine, October 1990, offers an update,
- Principles of Steam Heating, $13.25 includes postage. Fuel oil & Oil Heat Magazine, 389 Passaic Ave., Fairfield, NJ 07004.
- The Lost Art of Steam Heating, Dan Holohan, 516-579-3046 FAX
- Principles of Steam Heating, Dan Holohan, technical editor of Fuel Oil and Oil Heat magazine, 389 Passaic Ave., Fairfield, NJ 07004 ($12.+1.25 postage/handling).
- "Residential Steam Heating Systems", Instructional Technologies Institute, Inc., 145 "D" Grassy Plain St., Bethel, CT 06801 800/227-1663 [home inspection training material] 1987
- "Residential Hydronic (circulating hot water) Heating Systems", Instructional Technologies Institute, Inc., 145 "D" Grassy Plain St., Bethel, CT 06801 800/227-1663 [home inspection training material] 1987
- "Warm Air Heating Systems". Instructional Technologies Institute, Inc., 145 "D" Grassy Plain St., Bethel, CT 06801 800/227-1663 [home inspection training material] 1987
- Heating, Ventilating, and Air Conditioning Volume I, Heating Fundamentals,
- Boilers, Boiler Conversions, James E. Brumbaugh, ISBN 0-672-23389-4 (v. 1) Volume II, Oil, Gas, and Coal Burners, Controls, Ducts, Piping, Valves, James E. Brumbaugh, ISBN 0-672-23390-7 (v. 2) Volume III, Radiant Heating, Water Heaters, Ventilation, Air Conditioning, Heat Pumps, Air Cleaners, James E. Brumbaugh, ISBN 0-672-23383-5 (v. 3) or ISBN 0-672-23380-0 (set) Special Sales Director, Macmillan Publishing Co., 866 Third Ave., New York, NY 10022. Macmillan Publishing Co., NY
- Installation Guide for Residential Hydronic Heating Systems
- Installation Guide #200, The Hydronics Institute, 35 Russo Place, Berkeley Heights, NJ 07922
- The ABC's of Retention Head Oil Burners, National Association of Oil Heat Service Managers, TM 115, National Old Timers' Association of the Energy Industry, PO Box 168, Mineola, NY 11501. (Excellent tips on spotting problems on oil-fired heating equipment. Booklet.)
Books & Articles on Building & Environmental Inspection, Testing, Diagnosis, & Repair
- The Home Reference Book - the Encyclopedia of Homes, Carson Dunlop & Associates, Toronto, Ontario, 25th Ed., 2012, is a bound volume of more than 450 illustrated pages that assist home inspectors and home owners in the inspection and detection of problems on buildings. The text is intended as a reference guide to help building owners operate and maintain their home effectively. Field inspection worksheets are included at the back of the volume. Special Offer: For a 10% discount on any number of copies of the Home Reference Book purchased as a single order. Enter INSPECTAHRB in the order payment page "Promo/Redemption" space. InspectAPedia.com editor Daniel Friedman is a contributing author.
Or choose the The Home Reference eBook for PCs, Macs, Kindle, iPad, iPhone, or Android Smart Phones. Special Offer: For a 5% discount on any number of copies of the Home Reference eBook purchased as a single order. Enter INSPECTAEHRB in the order payment page "Promo/Redemption" space.
- Carson Dunlop, Associates, Toronto, have provided us with (and we recommend) Carson Dunlop Weldon & Associates' Technical Reference Guide to manufacturer's model and serial number information for heating and cooling equipment
Special Offer: Carson Dunlop Associates offers InspectAPedia readers in the U.S.A. a 5% discount on any number of copies of the Technical Reference Guide purchased as a single order. Just enter INSPECTATRG in the order payment page "Promo/Redemption" space.
- Carbon Monoxide Gas Toxicity, exposure limits, poisoning symptoms, and inspecting buildings for CO hazards
- DUST, HVAC CONTAMINATION STUDY An Investigation of Indoor Dust Debris Blamed on a Heating/Cooling System Reveals Carpet Dust
- Fuel Oil & Oil Heating Magazine, 3621 Hill Rd., Parsippany, NJ 07054, 973-331-9545
- Goodman Furnace High Temperature Plastic Vent HTPV safety recall US CPSC notice
- Home Heating System Should Be Checked[for proper venting and for CO Carbon Monoxide Hazards - DJF]
- Inspection Procedures for Oil-Fired Heating Systems Detailed step by step approaches for inspecting complex systems]
- Lennox Pulse Furnace Safety Inspection/Warranty Program: Carbon Monoxide Warning
- Oil Tanks - The Oil Storage Tank Information Website: Buried or Above Ground Oil Tank Inspection, Testing, Cleanup, Abandonment of Oil Tanks
- Oil Tanks Above Ground, UL Standards, guidance for home owners, buyers, and inspectors