Question? Just ask us!
Free Encyclopedia of Building & Environmental Inspection, Testing, Diagnosis, Repair
InspectAPedia ® Home
AIR CONDITIONING & HEAT PUMP SYSTEMS
BACKDRAFTING HEATING EQUIPMENT
BACKUP HEAT for HEAT PUMPS
BANGING HEATING PIPES RADIATORS
BLOWER FAN OPERATION & TESTING
BOOKSTORE - InspectAPedia
BTU USAGE MONITORS
CARBON MONOXIDE - CO
CIRCULATOR PUMPS & RELAYS
DIAGNOSTIC GUIDES A/C / HEAT PUMP
DIAGNOSE & FIX HEATING PROBLEMS-BOILER
DIAGNOSE & FIX HEATING PROBLEMS-FURNACE
DIRECT VENTS / SIDE WALL VENTS
DRAFT REGULATORS, DAMPERS, BOOSTERS
DUCT SYSTEM & DUCT DEFECTS
ELECTRIC MOTOR DIAGNOSTIC GUIDE
FAN, AIR HANDLER BLOWER UNIT
FLOODED HEATING EQUIPMENT REPAIR
FLUE SIZE SPECIFICATIONS
GAS BURNER Flame & Noise Defects
GAS PIPING, VALVES, CONTROLS
GEOTHERMAL HEATING SYSTEMS
HEAT PUMPS, DIAGNOSIS, REPAIR
HEATING COST SAVINGS METHODS
HEATING OIL PIPING TROUBLES
HEATING OIL TANKS
HEATING SYSTEM NOISES
HEATING SYSTEM TYPES
GAS LP & NATURAL GAS SAFETY HAZARDS
MANUALS & PARTS GUIDES - HVAC
MIXING / ANTI-SCALD VALVES
MOTOR OVERLOAD RESET SWITCH
NOISE, HEATING SYSTEMS
ODORS FROM HEATING SYSTEMS
OIL FILTERS on HEATING EQUIPMENT
OIL FILL PIPE LEAKS
OIL SPILL CLEANUP / PREVENTION
PLASTIC Plexvent / Ultravent RECALL
PUFFBACKS, OIL BURNER
RELIEF VALVE LEAKS
Reset Switch - Heater Primary Control
RESET SWITCH - ELECTRIC MOTOR
Reset Switch - Stack Relays
SAFETY, HEATING INSPECTION
SAFETY RECALLS CHIMNEYS VENTS HEATERS
SOLAR HEATING SYSTEM DESIGNS
SOOT on OIL FIRED HEATING EQUIPMENT
STEAM HEATING SYSTEMS
THERMOSTATS, HEATING / COOLING
VIDEO GUIDES: Heating System Videos
WINTERIZE A BUILDING
WOOD, COAL STOVES & FIREPLACES
WOOD STOVE SAFETY
ZONE VALVES, HEATING
Low voltage (12-24 VAC) transformers guide for HVAC systems: this article explains how low-voltage transformers are used on heating, heat pumps, & air conditioning systems to provide power for thermostats, zone valves, and other relays and controls. We explain how a low voltage transformer is installed and wired, where the device is usually located, and how to test or troubleshoot & repair low voltage transformers using a VOM or DMM. Also see LOW VOLTAGE BUILDING WIRING.
Green links show where you are. © Copyright 2014 InspectApedia.com, All Rights Reserved.
Question: How do you tell if a transformer is bad? How do you test a low voltage transformer?
How do you test a low voltage transformer? - Den 7/16/12
Reply: how to test a low voltage transformer for heating or air conditioning
Erwin if you disconnect the low voltage wires connected to the transformer terminals and use a VOM you should find voltage, usually 14V. If the device looks burned, hot, or smells, don't even bother testing. If it has been buzzing that's another clue.
Remove all of the the low voltage wires from the two (or more) screws on the top of the transformer. Usually you'll see a small gauge red and white wire simply connected under two screws on the upper surface of the transformer itself.
And thank you for the question - we have answered your question more extensively and have added details about low voltage transformers used on heaters and air conditioners and how the transformer is located, wired, and tested at LOW VOLTAGE TRANSFORMER TEST.
To test for a bad low voltage transformer you simply need a volt-ohm meter or a digital VOM. See DMMs VOMs SAFE USE OF for advice on how to use a volt-ohm meter, and see Guide to Electrical Test Equipment for advice on how to electrical test equipment safely. And of course you'll have to be sure you have found and are testing the right low voltage relay, as we will explain in the details below.
In our photo you can see a low voltage transformer mounted onto a 4-inch electrical box that is in turn secured to (and powered from) a gray-covered electrical panel. But as there are four circulator pumps shown in the photo, you can figure there will be more LV transformers and more circulator relay switches nearby, connected to other room thermostats in this building. Why? A typical residential-grade low voltage transformer cannot handle the total current draw (in Amps) to support multiple circulator pump relays or other controls.
It's usually pretty simple to understand the wiring and function of a low voltage relay on HVAC/R equipment. The low voltage transformer changes (transforms) house current (at 120V AC) to a lower voltage (usually around 14V to 24V AC) used to operate the room thermostats and possibly other heating or air conditioning controls.
The low-voltage transformer shown at left, a reader-contributed photo, is feeding two pairs of low voltage 24V circuit wires (red and white); the 120V power wires feeding the transformer are the heavier wires in the center of this device. Click to enlarge this or any image.
So the transformer has 12V wires connected to its input terminals (not visible in our photo at left as by code the 120V wires have to be inside of that 4" metal electrical box). The low voltage thermostat wires that bring operating current (14-12V VAC) to the thermostats are on the exposed surface of the transformer.
In the simplest applications, two wires, typically red and white, are connected at the transformer.
an "R" terminal on the transformer is connected first to the thermostat (which acts as an "on-off" switch) and from the thermostat onwards to a thermostat terminal found on the heater or air conditioner's primary control or circuit board.
Details about thermostat wiring and low voltage control wiring are found at THERMOSTAT WIRE CONNECTIONS.
When we think that there may be a problem with getting power to a thermostat (if it needs power) or to other low-voltage-operated controls in an HVAC system, the "test" of the low voltage HVAC transformer involves these very simple steps:
On some modern HVAC equipment the low voltage transformer may be harder to spot as it may be incorporated into a more complex circuit board or component. In all cases, however, if you follow the small gauge low-voltage wires from your thermostat back into the furnace or air handler cabinet you can find wires of this same dimension connected to a transformer.
Watch out: there may be more than one low voltage thermostat, for example one controlling heating and another controlling air conditioning in your building. Or there may be additional low-voltage thermostats providing power to individual hydronic heating zone circulator pump relays and to the thermostats that control each of those zones (see our photo at the top of this page).
Watch out: there are other low voltage transformers found on air conditioners, boilers, furnaces, circulator relays, fan relays, etc. that are not the units providing low voltage to the room thermostat and main on-off HVAC/R controls.
Green link shows where you are in this article series.
Frequently Asked Questions (FAQs)
No FAQs have been posted for this page. Try the search box below or CONTACT US by email if you cannot find the answer you need at InspectApedia.
Check the FAQs just above, try the search box just below, or if you prefer, post a question or comment in the Comments box below and we will respond promptly.
Search the InspectApedia website
HTML Comment Box is loading comments...
Technical Reviewers & References
Related Topics, found near the top of this page suggest articles closely related to this one.