Question? Just ask us!
Free Encyclopedia of Building & Environmental Inspection, Testing, Diagnosis, Repair
InspectAPedia ® Home
AIR CONDITIONING & HEAT PUMP SYSTEMS
BACKDRAFTING HEATING EQUIPMENT
BACKUP HEAT for HEAT PUMPS
BANGING HEATING PIPES RADIATORS
BLOWER FAN OPERATION & TESTING
BOOKSTORE - InspectAPedia
BTU USAGE MONITORS
CARBON MONOXIDE - CO
CIRCULATOR PUMPS & RELAYS
DIAGNOSTIC GUIDES A/C / HEAT PUMP
DIAGNOSE & FIX HEATING PROBLEMS-BOILER
DIAGNOSE & FIX HEATING PROBLEMS-FURNACE
DIRECT VENTS / SIDE WALL VENTS
DRAFT HOOD, GAS HEATER
DRAFT REGULATOR, DAMPER, BOOSTER
DUCT SYSTEM & DUCT DEFECTS
ELECTRIC MOTOR DIAGNOSTIC GUIDE
FAN, AIR HANDLER BLOWER UNIT
FLOODED HEATING EQUIPMENT REPAIR
FLUE SIZE SPECIFICATIONS
GAS BURNER FLAME & NOISE DEFECTS
GAS PIPING, VALVES, CONTROLS
GEOTHERMAL HEATING SYSTEMS
HEAT PUMPS, DIAGNOSIS, REPAIR
HEATING COST SAVINGS METHODS
HEATING OIL PIPING TROUBLES
HEATING OIL TANKS
HEATING SYSTEM NOISE DIAGNOSIS
HEATING SYSTEM TYPES
GAS LP & NATURAL GAS SAFETY HAZARDS
MANUALS & PARTS GUIDES - HVAC
MIXING / ANTI-SCALD VALVES
MOTOR OVERLOAD RESET SWITCH
NOISE, HEATING SYSTEMS
ODORS FROM HEATING SYSTEMS
OIL FILTERS on HEATING EQUIPMENT
OIL FILL PIPE LEAKS
OIL SPILL CLEANUP / PREVENTION
PLASTIC PLEXVENT ULTRAVENT RECALL
PUFFBACKS, OIL BURNER
RELIEF VALVE LEAKS
RESET SWITCH, HEATER PRIMARY CONTROL
RESET SWITCH, ELECTRIC MOTOR
RESET SWITCH, STACK RELAY
SAFETY, HEATING INSPECTION
SAFETY RECALLS CHIMNEYS VENTS HEATERS
SOLAR HEATING SYSTEM DESIGNS
SOOT on OIL FIRED HEATING EQUIPMENT
STEAM HEATING SYSTEMS
THERMOSTATS, HEATING / COOLING
VIDEO GUIDES: HEATING SYSTEMS
WINTERIZE A BUILDING
WOOD-OIL COMBINATION HEATERS
WOOD STOVE OPERATION & SAFETY
ZONE VALVES, HEATING
Boiler low water cutoff control service or repair: Here we explain Low Water Cutoff Controls: Guide to LWCOs on steam heating and hot water heating systems and we provide a low water cutoff switch Troubleshooting & Repair Guide.
LWCOs are installed on most steam heating boilers and also on many hydronic or "hot water" heating boilers as a safety device to shut down the boiler in the event of loss of water in the system.
This article series answers most questions about central heating systems to aid in troubleshooting, inspection, diagnosis, and repairs.
Green links show where you are. © Copyright 2015 InspectApedia.com, All Rights Reserved.
In order to avoid a heating boiler explosion or damage from loss of water, the low water cutoff is a device intended to shut down unsafe heating equipment by turning off electrical power to the oil burner or gas burner should the water level or pressure in the heating system fall below a safe level.
The schematic at left, courtesy of Carson Dunlop, explains how the low water cutoff valve works.
[Click to enlarge any image]
In short, LWCOs are among multiple heating system safety controls that help prevent a boiler explosion or BLEVE
Low Water Cutoff - LWCO's on heating boilers: this steam heating boiler safety device contains a mechanical or electronic sensor to monitor water level in the boiler. LWCOs are installed on many modern residential hydronic (hot water) heating boilers and on virtually all steam boilers. LWCOs are also installed on all commercial boilers of both types.
Original LWCO valve designs like the low water cutoff mounted on the face of the boiler shown at left used a mechanical float which operated not unlike the float arm in a toilet tank.
As water level drops the arm moves down and ultimately trips a mechanical switch that operates an electrical contact to turn the heating system off.
Watch out: Mechanical-float LWCOs are subject to jamming due to sludge that forms in the steam boiler as water is lost and mineral debris is left behind.
Electronic LWCOs: Newer LWCO controls replace the mechanical float switch with a sensor, reducing the chances of a cutoff malfunction.
By monitoring boiler water level and turning off the oil or gas or electric heat source to the heating boiler should water level drop too low in the steam boiler, this important safety device prevents damage to the boiler should the system lose its water.
Sediment and Low Water Cutoff Valves - Flushing Needed: how to use the Steam Boiler Blowdown Valve
As we explained above, mechanical-float LWCO's need to be flushed to remove sediment that could prevent the cutoff from working. In the photo at page top you can see that the owner has left a 5-gallon plastic bucket below the low water cutoff drain pipe. That's for flushing out the LWCO valve.
Watch out: if the low water cutoff valve is not flushed often enough, the residue of solid debris (minerals, rust, dirt, also referred to as "TDS" or total dissolved solids) can clog the low water cutoff valve so that it will stop working and could fail to sense an unsafe low-water condition in the heating boiler.
Low boiler water level can lead to costly boiler damage or even a BLEVE explosion (see BLEVE EXPLOSIONS). Ask your heating service technician how often your LWCO needs to be flushed.
In the photo at left you can see that the system has two low water cutoff valves installed, at two different levels on the steam boiler. Perhaps this setup was installed for an extra measure of safety?
Since steam heating systems are constantly using water, losing some of it as water vapor venting at steam radiators, and regaining water as the automatic (or on some systems manual) water feeder replaces water in the system, these systems tend to produce sediment at the boiler.
If sediment collects in the low water cutoff valve it could prevent the valve's internal float from falling as water level in the steam boiler drops, thus preventing the valve from safely shutting down the boiler should water level fall to an unsafe level. For this reason the low water cutoff valve needs to be flushed regularly, often once a week.
How to Use the Blowdown Valve - Steam Boiler Low Water Cutout Valve Flushing Procedure
When we flush a steam boiler or a hydronic heating boiler low water cutoff valve we:
Safety warning: Be careful, when a steam boiler has been running, water coming out of the low water cutoff flush valve is hot and can scald a bystander.
Watch out: don't confuse water well low-water cutoff controls with heating system low water cutoff controls. The low water cutoff devices that we discuss here are intended for protecting the safe operation of building heating boilers or steam boilers. Heating low water cutoff devices (LWCO) are distinct from and have nothing to do with the well piping or building water supply cutoff safety devices discussed at WELL PIPING TAIL PIECE.
If you don't know what kind of heat your building uses, we explain how to figure out the answer at HEATING SYSTEM TYPES.
If your heating system is not working properly, see NO HEAT - BOILER or NO HEAT - FURNACE. Contact us to suggest text changes and additions and, if you wish, to receive online listing and credit for that contribution.
Continue reading at WATER FEEDER VALVE, STEAM or select a topic from the More Reading links shown below.
Suggested citation for this web page
Green link shows where you are in this article series.
Frequently Asked Questions (FAQs)
No FAQs have been posted for this page. Try the search box below or CONTACT US by email if you cannot find the answer you need at InspectApedia.
Questions & answers or comments about diagnosing & repairing LWCOs low water cutoff switches & controls on heating boilers
Use the "Click to Show or Hide FAQs" link just above to see recently-posted questions, comments, replies, try the search box just below, or if you prefer, post a question or comment in the Comments box below and we will respond promptly.
Search the InspectApedia website
HTML Comment Box is loading comments...
Technical Reviewers & References