Question? Just ask us!
Free Encyclopedia of Building & Environmental Inspection, Testing, Diagnosis, Repair
InspectAPedia ® Home
AFUE DEFINITION, RATINGS
AGE of CHIMNEYS & FIREPLACES
AGE of AIR CONDITIONERS & HEAT PUMPS
AGE of HEATERS, BOILERS, FURNACES
AIR FILTERS for HVAC SYSTEMS
AIR HANDLER / BLOWER UNITS
AIRBOUND HEAT SYSTEM REPAIR by WATER FEED VALVE
ANTIFREEZE for BOILERS
BACKDRAFTING HEATING EQUIPMENT
BACKFLOW PREVENTER VALVE, HEATING SYS
BACKFLOW PREVENTER, HEATER WATER FEEDER
BACKUP HEAT for HEAT PUMPS
BANGING HEATING PIPES RADIATORS
BLOWER FAN OPERATION & TESTING
BOOKSTORE - InspectAPedia
CAPACITORS for HARD STARTING MOTORS
COOL OFF HEAT, Thermostat Switch
COMBUSTION GASES & PARTICLE HAZARDS
DEFINITION of Heating & Cooling Terms
DIAGNOSTIC GUIDES A/C / HEAT PUMP
DIAGNOSE & FIX HEATING PROBLEMS-BOILER
DIAGNOSE & FIX HEATING PROBLEMS-FURNACE
DIRECT VENTS / SIDE WALL VENTS
DIRECTORY of OIL TANK EXPERTS
DRAFT MEASUREMENT, CHIMNEYS & FLUES
DRAFT REGULATORS, DAMPERS, BOOSTERS
DUCT SYSTEM & DUCT DEFECTS
FAN, AIR HANDLER BLOWER UNIT
FAN LIMIT SWITCH
FILTERS, AIR for HVAC SYSTEMS
FILTERS, OIL on HEATING EQUIPMENT
FIRE SAFETY CONTROLS
FLOODED HEATING EQUIPMENT REPAIR
FREEZE-PROOF A BUILDING
FUEL OIL TYPES & CHARACTERISTICS
FUEL UNIT, HEATING OIL PUMPS
GAUGES ON HEATING EQUIPMENT
HEAT LOSS INDICATORS
HEATING COST SAVINGS METHODS
HEATING LOSS DIAGNOSIS-BOILERS
HEATING LOSS DIAGNOSIS-FURNACES
HEATING OIL CLOUD WAX GEL POINT
HEATING OIL EXPOSURE HAZARDS, LIMITS
HEATING OIL - OLD, USEABLE?
HEATING OIL SHELF LIFE
HEATING OIL SLUDGE
HEATING OIL TANKS
HEATING OIL TYPES & PROPERTIES
HEATING OIL USAGE RATE
HEATING SYSTEM INSPECT DIAGNOSE REPAIR
HEATING SYSTEM NOISES
HEATING SYSTEM SERVICE FAQs
HEATING SYSTEM TYPES
HOT WATER HEATERS
LOW VOLTAGE BUILDING WIRING
MANUALS & PARTS GUIDES - HVAC
MIXING / ANTI-SCALD VALVES
MOTOR OVERLOAD RESET SWITCH
NO HEAT - BOILER
NO HEAT - FURNACE
NOISE, HEATING SYSTEMS
NOISE, WATER HEATER
ODORS & SMELLS DIAGNOSIS & CURE
ODORS FROM HEATING SYSTEMS
OIL BURNER FUEL UNIT
OIL BURNER INSPECTION & REPAIR
OIL BURNER NOISE SMOKE ODORS
OIL BURNER NOZZLE & ELECTRODES
OIL BURNERS, RETENTION HEAD
OIL BURNER SOOT & PUFFBACKS
OIL FILTERS on HEATING EQUIPMENT
OIL FILTER MISSING
OIL FUEL TYPES & CHARACTERISTICS
OIL HEAT FIRE SAFETY CONTROLS
OIL LINE CLOGGING FIX
OIL LINE QUICK STOP VALVES
OIL LINE SAFETY VALVES
OIL FILL PIPE LEAKS
OIL PUMP FUEL UNIT
OIL SPILL CLEANUP / PREVENTION
OIL TANK GAUGES
OIL TANK LEAKS & SMELLS
OIL TANK PIPING & PIPING DEFECTS
OIL TANK WATER REMOVAL
RELIEF VALVES - TP Valves on Boilers
RELIEF VALVES - STEAM TP VALVES
RELIEF VALVES - Water Heaters
RELIEF VALVES - Water Tanks
Reset Switch - Heater Primary Control
Reset Switch Broken - Quick RepaiR
RESET SWITCH - ELECTRIC MOTOR
Reset Switch - Stack Relays
SAFETY, HEATING INSPECTION
SAFETY RECALLS CHIMNEYS VENTS HEATERS
SOOT on OIL FIRED HEATING EQUIPMENT
STACK RELAY SWITCHES
STAIN DIAGNOSIS on BUILDING INTERIORS
STEAM HEATING SYSTEMS
THERMAL TRACKING & HEAT LOSS
THERMOSTATS, HEATING / COOLING
THERMOSTATS, WATER HEATER
VIDEO GUIDES: Heating System Videos
VIDEO GUIDES - InspectAPedia.com
Oil quick stop valves or delay valves: this article describes solenoid operated quick stop valves used at oil burners. These oil safety valves, when they include a timer that delays valve opening at burner start-up, are also referred to as oil delay valves or oil delay solenoids.
Quick-stop valves and oil delay valves improve oil burner operation by eliminating the delivery of oil to the oil burner nozzle at low pressures. Low pressure oil delivery, which can be caused by air leaks or just slow burner start-up, causes dirty oil burner operation and can lead to loss of heat or dangerous oil burner puffbacks.
Here we explain how and why quick stop and oil delay valves are used, how they are installed, and how to diagnose problems with OSVs and quickstop or delay valves.
Green links show where you are. © Copyright 2013 InspectAPedia.com, All Rights Reserved.
Oil Delay Solenoid Valve or Quick-Stop Valve or Safety Valve Installations on Oil Burner Pumps / Fuel Units
Oil heating technicians use at least four names for versions this device: an oil shut-off valve, an oil delay valve, a solenoid safety valve or a quick-stop valve. Except for the presence or absence of providing a valve opening delay at oil burner start-up, these are all the same product and they have the same basic purposes:
Shown in our photo above is R.W. Beckett's PD Timer part number 21887, a 120VAC 50/60 Hz control that provides a four second delay at burner start-up. The valve is rated for operating temperatures up to 150 degF.
Sources of Internal Check Valve Troubles in the Oil Pump or Fuel Unit
In standard installations the fuel oil pumping unit sends high pressure heating oil through its outlet tube to an inlet fitting on the oil burner that in turn sends that high pressure oil to the oil burner nozzle where it is sprayed and ignited in the combustion chamber. When the oil burner tops, we want to quickly stop the flow of oil to the nozzle. If we don't stop the oil flow quickly, heating oil at lower pressure continues to squirt, then dribble, out of the end of the nozzle where it will not benefit from complete combustion.
The result is an accumulation of un-burned heating oil in the combustion chamber - the cause of a "bang" or worse an oil burner puffback at the start of a subsequent oil burner "on" cycle.
Oil burner fuel units (oil pumps) already contain an internal check valve intended to quickly stop the flow of oil to the burner when the oil burner motor stops. But with age, or more likely with the passage of dirt and sludge from the oil tank, through the oil lines, through the oil filter, and finally sneaking past the internal filter screen found inside the fuel unit, that crud, or some of it, lands on the internal check valve seat where it can cause the valve to fail to seal quickly or completely.
How does an Oil Shut-off or Oil Delay Shut-off Valve Work & What Problems Does it Solve?
An oil delay solenoid switch or valve, also popularly referred to by some service techs as a quck-stop valve, is an electrically operated valve installed on the oil line between the fuel unit and the oil burner nozzle assembly.
Our photo (left) shows a new oil burner fuel unit installed on our older Beckett oil burner. It's worth reading the label on the fuel unit - it warns Use Only with Valve on Delay.
The oil delay valve, operated by an electrical solenoid switch, closes to immediately stop the flow of oil to the oil burner assembly the second that electrical power to the oil burner is shut off.
This quick-stop valve is a handy "fix" that we can add to an existing oil burner fuel unit if we think that its internal check valve is not working properly. (Few technicians would attempt to disassemble and clean the fuel unit to that level of detail, and an oil delay valve is less expensive than a whole new fuel unit.)
When the oil burner motor starts, the power circuit also powers the oil line solenoid valve. We call the device an oil-delay-valve because the valve includes a built-in time delay that allows the oil burner motor and blower assembly to spin for a brief time before the valve opens to permit oil to pass on to the burner nozzle. This delay, an added feature, helps establish draft and reduces sooting at the oil burner.
Oil Shut-Off Valves Integral with New Fuel Units
Interestingly, some fuel units now come from the manufacturer with an oil delay valve assembly already attached. The importance of a sharp clean cessation of oil flow makes this added feature desirable. We had asked our heating service company to install an oil delay valve on our oil burner to stop a startup "Bang" and soot problem that was chronic on our lab heating system. Bob, Bottini's service tech, inspected more closely and found that the fuel unit had a small leak around its shaft. That leak sent oil into the oil burner assembly, crudding up the oil burner combustion air fan and adding to a dirty oil burner flame problem.
Since our oil burner fuel unit needed to be replaced anyway, it was more economical to install a new fuel unit that included as well an oil delay solenoid valve than it would have been to buy and install those parts separately.
Wiring the Oil Shut-off or Oil Delay Valve
Wiring the oil delay solenoid: for most models, the solenoid valve's electrical wires are connected to the oil burner "run" circuit inside the primary control by connecting the solenoid control circuit wires to the oil burner motor leads - in this case, the nearby cad cell relay.
The standard oil burner solenoid valve cordset can be replaced with a PD timer kit such as the R.W. Beckett PD Timer #21887U that provides a precise 4-second delay between the oil burner motor start-up and the opening of a valve that admits oil from the fuel unit to the oil burner nozzle. You should follow the wiring diagram that will certainly come with the product that you purchase.
Above we provide an example wiring diagram for an oil delay valve time, from Beckett's 21887U PD Timer delay cordset.
How Long does an Oil Shut-off Valve Delay at Oil Burner Start-up
To be clear, we want a zero-second delay at oil burner shut-down, as we explained above. But we may want our solenoid operated shut-off valve to delay its open by a few seconds to allow the burner and blower assembly to get up to full speed, improving draft and combustion air flow to assure a very clean start-up when oil is released to the oil burner nozzle and igniter.
Suntec, a manufacturer of fuel units and delay valves describes a solenoid dumping pump used on their A-7400 fuel unit as including
Solenoid operated shut-off valves are sold in both non-delay models (Such as Suntec R642NL) and delay models that provide a 1-2 second delay (Suntec R641DL) or a 3-5 second delay (Suntec R643LL) or even up to 15 seconds of delay to suit various application needs.
No Heat Call Traced to Open Quick Stop Valve or Oil Delay Valve Electrical Connector
On a recent no-heat call we were embarrassed to learn from Bob, the service tech, that the problem was most likely that somebody had accidentally knocked loose an electrical connector at the oil delay valve (aka "quick stop valve").
The valve in our photos is used by Beckett on some oil burner models (depending on fuel unit features) and is labeled PD Timer.
The connector may still appear to be in place but may have been pushed slightly back or askew.
The result is that on a call for heat the oil burner motor will run but the burner will never ignite.
Because the oil delay valve delays forever - without its own electrical connector it never opens. The result is that the burner will shut off on reset due to a failure of the cad cell to see flame.
We tied the rubber boot (black rectangle at the right side of the valve itself) to the PD Timer oil delay valve body (gray in center of the photo) using plastic ties.
As Bob pointed out, this step to prevent the oil delay valve or PD Timer connector from being knocked loose again is ok as long as you're not foolish enough to wrap the plastic tie around the oil line (copper in our photo, above the PD Timer delay valve body).
The PD Timer is produced by xxx. Beckett, a manufacturer of the oil burner in our photos indicates that an alternative to the PD Time is to "Use 21844U Clean Cut Pump without PD Timer when primary control has a pre-time (valve on delay)."
We might wish that the manufacturer of the PDTimer had included a simple clip that would prevent the connecting wiring boot from being knocked off of the valve body. Other than the loose-connector trouble leading to no-heat calls, this quick stop / oil delay valve has performed flawlessly on our test system since installation.
Don't confuse oil safety valves, oil delay valves, or oil quick stop valves discussed just above with Fusible Link Oil Safety Valves, Vacuum-Activated Oil Safety Valves, OSVs & PRVs, Check Valves on Heating Oil Lines, and Tigerloop™ or similar oil line de-aerator/prime-protection devices.
This article series explains the installation & use of Fusible Link Oil Safety Valves, Vacuum-Activated Oil Safety Valves, OSVs & PRVs, Check Valves on Heating Oil Lines, and . Oil delay valves, also called quick-stop valves and also referred to as oil safety valves, are discussed separately at OIL LINE QUICK STOP VALVES.
Green link shows where you are in this article series.
Frequently Asked Questions (FAQs) about Quick Stop Oil Safety Solenoid Valves & Timers & Oil Delay Valves
Questions & answers or comments about quick-stop valves, oil delay valves, & oil solenoid valves: definition, installation, uses, & troubleshooting.
Ask a Question or Enter Search Terms in the InspectApedia search box just below.
Technical Reviewers & References
Related Topics, found near the top of this page suggest articles closely related to this one.