Question? Just ask us!
Free Encyclopedia of Building & Environmental Inspection, Testing, Diagnosis, Repair
InspectAPedia ® Home
ENVIRONMENTAL HAZARDS - INSPECT, TEST, REMEDY
ACOUSTICAL SEALANT CHOICES
AGE of a BUILDING - how to determine
AIR BYPASS LEAKS
AIR LEAK DETECTION TOOLS
AIR LEAK MINIMIZATION
AIR LEAK SEALING PROCEDURE
AIR POLLUTANTS, COMMON INDOOR
ALLERGENS in BUILDINGS, RECOGNIZING
ANIMAL ALLERGENS / PET DANDER
APPLIANCE EFFICIENCY RATINGS
ARCHITECTURE & BUILDING COMPONENT ID
ASBESTOS CEILING TILES, Asbestos-Containing
ASBESTOS & FIBER CEMENT ROOFING
ASBESTOS CEMENT SIDING
ASBESTOS DUCTS, HVAC
ASBESTOS-FREE INSULATION MATERIALS
ASBESTOS IDENTIFICATION IN BUILDINGS
ASBESTOS FLOORING HAZARD REDUCTION
ASBESTOS FLOOR TILE IDENTIFICATION
ASBESTOS FLOORING REMOVAL GUIDE
ASBESTOS LIST of PRODUCTS
ASBESTOS MATERIAL REGULATIONS
ASBESTOS MATERIAL REGULATIONS Update
ASBESTOS MATERIAL REGULATIONS, OSHA
ASBESTOS PHOTO GUIDE to Materials
ASBESTOS REMOVAL, Amateur, Incomplete
ASBESTOS REMOVAL CERTIFICATIONS
ASBESTOS REMOVAL, Wetting Guidelines
ASBESTOS RISK ASSESSMENT
ASBESTOS TESTING LAB LIST
ASBESTOS UNDER the MICROSCOPE
ROOF ICE DAM LEAKS
BASEMENT HEAT LOSS
BUCKLED FOUNDATIONS due to INSULATION?
BUILDING NOISE DIAGNOSIS & CURE
CATHEDRAL CEILING INSULATION
CEILING FINISHES INTERIOR
CEILINGS, DROP or SUSPENDED PANEL
CEILINGS & WALLS, PLASTER TYPES
CERAMIC TILE FLOOR, WALL
CERAMIC TILE, ASBESTOS in?
CHIMNEY INSPECTION DIAGNOSIS & REPAIR
CHINESE DRYWALL HAZARDS
DEW POINT CALCULATION for WALLS
EFFLORESCENCE SALTS & WHITE DEPOSITS
FIBERGLASS INSULATION MOLD
FLOOR TILE HISTORY & INGREDIENTS
FLOOR TILES ASBESTOS
FLOOR TYPES & DEFECTS
HEAT LOSS in BUILDINGS
HOUSE DOCTOR, how-to be
HUMIDITY LEVEL TARGET
ROOF ICE DAM LEAKS
INDOOR AIR QUALITY IMPROVEMENT GUIDE
INSULATION FACT SHEET- DOE
INSULATION IDENTIFICATION GUIDE
INSULATION MOLD TEST
INSULATION R-VALUES & PROPERTIES
METAL LATH, PLASTER & STUCCO
METHANE GAS SOURCES
MOISTURE CONTROL in BUILDINGS
MOLD: A COMPLETE GUIDE TO MOLD
Museum Artifact Preservation
NOISE / SOUND DIAGNOSIS & CURE
ODORS GASES SMELLS, DIAGNOSIS & CURE
PAINT FALURE, DIAGNOSIS, CURE, PREVENTION
DRYWALL, PLASTER, BEAVERBOARD
PLASTER BULGES & PILLOWS
PLASTER LATH, METAL
PLASTER, LOOSE FALL HAZARDS
PLASTER TYPE IDENTIFICATION
PLASTER VENEER Best Practices
ROOF VENTILATION SPECIFICATIONS
SAFETY HAZARDS & INSPECTIONS
SEARS KIT HOUSES
SOUND CONTROL in buildings
SPLITS & CRACKS in STRUCTURAL WOOD BEAMS
STAIN DIAGNOSIS on BUILDING EXTERIORS
STAIN DIAGNOSIS on BUILDING INTERIORS
STUCCO WALL METHODS & INSTALLATION
STRUCTURAL DAMAGE PROBING
SWEATING (CONDENSATION) on PIPES, TANKS
THERMAL EXPANSION CRACKS in BRICK
THERMAL EXPANSION of MATERIALS
THERMAL IMAGING, THERMOGRAPHY
THERMAL MASS in BUILDINGS
THERMAL TRACKING Indicates Heat Loss
VAPOR BARRIERS & CONDENSATION in BUILDINGS
VENTILATION in BUILDINGS
VINYL CHLORIDE HEALTH INFO
VOCs VOLATILE ORGANIC COMPOUNDS
WALL CONSTRUCTION BARRIER vs CAVITY
WATER ENTRY in BUILDINGS
WINDOWS & DOORS
WINTERIZE A BUILDING
WOOD Burning Heaters Fireplaces Stoves
WORLD TRADE CENTER 9-11 DUST PHOTOS
Vermiculite insulation home page: how to recognize vermiculite building insulation that may contain asbestos fibers. This article permits visual identification of vermiculite insulation; we include our own as well as US EPA photographs of various forms of vermiculite insulation to assist in recognizing vermiculite in buildings. We describe the history of vermiculite insulation, the asbestos hazard that may be present depending on which vermiculite insulation product is present, and how asbestos is identified in vermiculite insulation.
We give the history of the Libby vermiculite mine, its purchase by WR Grace Corporation, the asbestos-related bankruptcy filing, asbestos abatement cost claims & filings. We also list other, including current producers of vermiculite insulation. This document assists building buyers, owners or inspectors who need to identify asbestos materials (or probable-asbestos) in buildings by simple visual inspection. We provide photographs and descriptive text of asbestos insulation and other asbestos-containing products to permit identification of definite, probable, or possible asbestos materials in buildings.
Green links show where you are. © Copyright 2015 InspectApedia.com, All Rights Reserved.
Vermiculite is a mineral (hydrated laminar mangesium-aluminum-iron silicates or hydrated phlogopite or biotite mica) from the phyllosilicate group. Vermiculite looks somewhat like mica in that it includes shiny flat plates of material that can be separated.
Because this mineral expands to many times its original volume when it is heated, processed vermiculite produces a lightweight material with insulating and other useful properties.
In addition to its use as an insulation product and in construction as a masonry fill, a cavity fill, & in concrete blocks, vermiculite is added to soils in horticultural applications and to cement to make a lightweight concrete swimming pool base. Vermiculite is also used in special applications such as industrial filters.
Watch out: vermiculite from some sources contains asbestos and can be an asbestos dust hazard in buildings. Details about the asbestos content in some vermiculite insulation products is found in this article beginning at: Which Vermiculite Insulation Products Contain Asbestos?
We have observed that depending on the mine from which it originates, and the process used to expand the vermiculite particles, vermiculite may vary in appearance and shininess.
Vermiculite insulation is easy to identify by visual inspection, as it is a granular, loose-fill pour-in insulation comprised of particles typically gray or brown or silver-gold in color, often with bits of reflective mica included.
What can be confusing is that vermiculite particle sizes range from about 1/8" in diameter to more than 1/2" in diameter depending on the producer and batch, with a few large particles that can be more than one inch in length.
The individual vermiculite insulation particles, an expanded mineral, are quite light in weight. Depending on the condition of the vermiculite insulation, whether or not it has been disturbed, and also depending on its original manufacture and quality, various amounts of dust and ultra-small particles may also be present.
Vermiculite insulation may be comprised of particles of several colors and shades (see our page top photo), or nearly all of the particles may be consistently the same color, as we show in our closeup photograph of vermiculite (left). This photo shows how we noticed the presence of vermiculite insulation by peering through a crack between attic floorboards. It was not necessary to remove flooring to find this material.
Our first two vermiculite attic insulation photos (below) show what you may see in the typical attic of an older home where vermiculite was added to the attic floor. You will often find a mix of several kinds of building insulation, and the vermiculite may, for example, have been covered-over by rolled out fiberglass or fiberglass batt insulation.
Below we illustrate that in "original" condition, that is without mechanical damage from being walked-on, vermiculite insulation products can vary considerably in size and appearance.
The two vermiculite photos above and the third at below left illustrate a considerable range in average particle size in different vermiculite insulation products, possibly coming from different mines or from different expansion processes.
For reference, the very large vermiculite particle at below left was 1.5 cm x 1 cm in size, and some reports indicate that pour-in attic insulation can contain vermiculite particles up to an inch (2.5 cm) in length. As you can see in our vermiculite insulation images here, the color of the material ranges from a creamy white to gold or tan in color.
At above right, in the same largest-particle-size vermiculite sample, you can observe the mica-like shiny surface and layering or laminate structure of some of these vermiculite particles.
Watch out: vermiculite insulation was not only poured into attic floors but also into building wall cavities during insulation retrofit projects. Particularly in older balloon-framed buildings, vermiculite could be poured from the attic right into wall cavities extending all the way to the building foundation top. Vermiculite was also often poured into hollow-core concrete block walls.
Mississippi home inspector Dan Phillips sent along these interesting photographs of vermiculite insulation from a 1940's home in Tennessee.
Phillips added "The home itself was built in the 40’s and had several renovations done to it. The vermiculite was added during one of these renovations in the past, and covered some older insulation as well as serving as single insulation to newer portions of the home." He observed that this particular vermiculite insulation was comprised of a mix of both small reflective mineral fragments (mica-like) as well as larger fragments up to almost 1/4" of expanded vermiculite insulation material.
Without testing by a certified asbestos testing laboratory, we don't know if this particular vermiculite contains asbestos or not, - appropriate warnings were issued to the client.
That experience reminds us that in an older home there are often multiple kinds of insulation present, and they may not all be visible, newer materials having covered older.
Web search 08/17/2010, original source: http://www.epa.gov/asbestos/pubs/verm.html#made
Home inspector David Grudzinski provides the following vermiculite insulation photographs. Mr. Grudzinski comments:
Mr. Grudzinski continues with an example of vermiculite insulation that had been missed by previous occupants, owners, buyers of a building.
It appears that some contractors still have no clue how to work around attic insulation, and this home has paid the price. The occupants had no clue and when I arrived and saw what was done, many long faces were observed.
The worst thing you can do when you have Vermiculite in an attic is to allow the bath fan to be blowing the product around.
Vermiculite, depending on its source, (from the Grace mine in Libby Montana) contains tremolite asbestos. For anyone who doesn't’t know the history, serious health and life safety hazards affected mine workers and others exposed to high levels of asbestos dust; millions of dollars in corrections were spent to clean up the site.
The vermiculite insulation product sold under the name Zonolite contained significant levels of asbestos, and was shipped all over the country for use as building insulation, even refrigeration system insulation, and for use in other applications.
Apparently this home owner had no idea of the potential hazard of asbestos dust in his/her home, and allowed this bath fan to blow the vermiculite insulation and its finer dust particles around for years.
The attic hatch from which I took the photo, is a pull down stair. Pull-down attic stairs do not provide an air seal between the attic and the occupied space. Further, under some conditions (such as when air conditioning is in use at a building, air (and attic dust) can be drawn downwards from an attic space into the occupied building areas. In my opinion there is a high probability that asbestos may have been released in the living space of this home.
To make matters worse, all sorts of fabric and carpets were tossed in the attic, and as you see in five vermiculite insulation and insulation contamination photos shown here, the vermiculite was disturbed and is on top of the fabric and is scattered everywhere.
To remove the fabric and debris, one will have to disturb the Vermiculite further.
Worse, bringing carpeting (below right) or other items stored in the attic down into the living area means importing vermiculite insulation (reasonably treated as Presumed Asbestos Containing Material or PACM) into the occupied space as well.
Justification for treating any vermiculite building insulation in the U.S. as PACM comes from the U.S. EPA who point out (later in this article) that Zonolite comprised about 70% of vermiculite insulation sold in the U.S.
Continuing my inspection it was apparent that the air conditioning system air duct (upper center in the photo at above right) passes through the ceiling and down into a closet below
(Second of the next two photos).
The question arose: how well was that ceiling penetration (above left) sealed against the passage of insulation, air or dust from the attic as it entered the closet (below left)?
I found not a shred of evidence that any measures had ever been taken to contain the vermiculite insulation, and it has spilled into the living space as you can see in our next photograph.
Evidence of Vermiculite & PACM (Asbestos) Entering the Living Space
Even at the time of my inspection, vermiculite insulation was seen falling out of the closet ceiling and onto closet contents as well as the closet floor (photo at left) because AC duct was installed in this space.
These conditions - vermiculite insulation and dust entering the occupied space of the building have almost certainly been ongoing for decades.
The actual level of airborne vermiculite (and very likely asbestos) dust would have varied as building air movement conditions varied, and would most likely have been highest when fans and/or the central air conditioning system were in operation.
In the attic the A/C system air handler in the attic is sitting in and on vermiculite insulation.
The A/C return air duct was observed to have vermiculite inside.
This condition virtually guarantees that airborne insulation (and presumably asbestos) dust and fragments would have been drawn into and sent through the air conditioning duct system whenever the air handler blower was operating.
What Should the Building Inspector or Owner Do About Suspected or Known Vermiculite Insulation & Presumed Asbestos Dust Contamination?
Extensive asbestos testing and repairs will be needed in this house.
We [OPINION - InspectApedia] would recommend a professional assessment of the extent of asbestos dust contamination in the building, including settled dust not just airborne dust, and almost certainly professional cleaning of the HVAC system and possibly other building areas are going to be in order.
When a home inspector sees loose vermiculite in a building during an inspection, we recommend not entering such an attic without wearing a HEPA respirator and a TYVEK suit that is bagged and disposed-of (in your home garbage not that at the property) on leaving the attic. If you didn't wear tyvek, dust off outside and wash your clothes. Those steps minimize the risk of importing PACM dust into other areas or buildings.
David Grudzinski, Advantage Home Inspections, is a professional home inspector who contributes on various topics including structural matters. Mr. Grudzinski, Cranston RI serving both Rhode Island and Eastern Connecticut can be reached at 401-935-6547 fax- 401-490-0607 or by email to Davidgrudzinski@aol.com
Our vermiculite insulation photo (left) from the attic of a home in New York state, shows how you might spot the presence of vermiculite insulation even when most of the attic floor has been covered-over. You'll also notice that while most of the vermiculite insulation particles in this photograph are silver-tan or silver gray, some dark fragments are also present, as well as incidental debris.
No. Vermiculite mined at the Libby Montana site until 1990 was formed in the Triassic period (225 million years ago) and contained tremolite asbestos.
Most of the vermiculite in the currently operating vermiculite mines (listed below) was formed 1.5 to 3 billion years ago in the pre-Cambrian and Archaen periods.
See this Vermiculite MSDS from Schundler
Also see ASBESTOS DUCTS, HVAC a field identification guide to visual detection of asbestos in and on heating and cooling system ducts and flue vents. Also see Micro-Photographs of Dust from the World Trade Center collapse following the 9/11/01 attack. Links to U.S. government and other authoritative research and advice are included.
His text and microscopy courses taught at McCrone Research and subsequently at McCrone Institute provided methods for identifying fibrous and non-fibrous asbestos in a wide range of materials.
Dr. McCrones photograph of fibrous tremolite asbestos is illustrated at above left. Like many minerals and some other particles, asbestos, including tremolite asbestos, can occur in both fibrous (above left) and non-fibrous (below left) forms.
Quoting from the U.S. EPA advice on vermiculite:
Zonolite Brand Vermiculite Insulation, ZAI (Zonolite Attic Insulation) Dust & Tremolite Asbestos Hazards
Watch out: Depending on the mine from which this mineral-based insulation was obtained, vermiculite insulation may contain asbestos fibers (including tremolite asbestos) and could present a hazard in buildings, especially if disturbed during renovations.
The U.S. EPA has photos of the original bags in which this product was shipped - you're not likely to see these bags in a home, though I've found them on occasion as you'll see in our own photograph of a Zonolite Insulation Fill bag shown at left.
Vermiculite insulation has an R-value of about 2.13 per inch in buildings.
As we discuss at our notes on other loose-fill insulations such as mineral wool or cellulose, any building insulated with loose-fill or spray-in insulation may benefit from the ability of these loose materials to fill gaps and openings more uniformly than might be found if sloppy workers are careless about installing insulating batts.
Drafty insulation installations can cause more heat loss than is made up for by differences in insulation R-values.
The United States Bankruptcy Court for the District of Delaware set 31 October 2008 as the bar date for Zonolite Attic Insulation (also branded "ZAI") claims to be filed in the W.R. Grace Personal Bankruptcy Case. The claims that were allowed prior to the bar date above included the cost of the abatement or removal of asbestos containing insulation and may have included a claim for other financial losses such as a reduction in property value where this insulation material was installed.
According to a helpful timeline published by Grace , commercial mining of vermiculite began in Libby Montana in 1923, ten years after Vermiculite Mountain was discovered in that town. Twenty one years later, in 1944, a question of possible hazards due to dust levels in the Libby vermiculite production plant was addressed by the Montana Department of Health who found dust levels below 50 ppm/ft3 and concluded that the dust was a nuisance but not hazardous.
By 1950, six years later, vermiculite production under the Zonolite brand reached 150,000 tons per year, and in 1954, as a measure to reduce dust levels in the mill, the first wet mill was installed at the Libby mine.
In 1956 the US Department of Health estimated that vermiculite mined from the Libby site had an asbestos content of 10% but added that there was no reliable way of analyzing asbestos content.
Walter C. McCrone, at McCrone Research Institute published detailed procedures for identifying asbestos by microscopic examination, and identifying which type of asbestos is in a material.
But that work was not published until 1980 in McCrone's "Asbestos Particle Atlas", and again in 1987 in detailed procedures described in his book, Asbestos Identification. See ASBESTOS UNDER the MICROSCOPE for details.
In 1956 the USDOH recommended a 50 mppcf limit of total dust and according to Grace, added "If the company will cooperate and actually attain dust control of this order, the asbestos and silicosis hazard would certainly be minimal."  suggesting that the health risks such as mesothelioma from asbestos dust exposure were still poorly understood.
Tremolite asbestos, the principal form of asbestos found in vermiculite from the Libby Montana mine, was identified by the Montana State Board of Health in 1961.
Up until the 1963 purchase of the Libby Montana vermiculite mine and the Zonolite corporation by W.R. Grace corporation, vermiculite insulation product mined at Libby was under the auspices of the Zonolite corporation. Grace indicates that at the time of the purchase, the company was unaware of the lurking asbestos hazards associated with mining and milling vermiculite. 
However by the following year it is evident that the new Libby Montana vermiculite mining operation had become aware of the health concerns associated with dust at the mining facility, because in 1964 the company initiated an annual x-ray testing program for Libby workers, and in the following year the company began moving employees reporting breathing concerns to less dusty areas of the facility.
Just one year later, in 1966 the Montana Board of Health reported dust concentrations at the Libby Montana vermiculite facility as varying between 9 ppm per cubic foot of air and 52 mppcf, complimenting Graces's efforts to reduce dust levels but indicating that further measures were needed. And in the following year, 1967, the Libby Montana mineworkers' union filed the first asbestos-related health claim. At that time even the union reported that dust levels had been reduced and that most (96%) of the dust level measurements were within Montana's "safe" threshold of 50 ppm per cubic foot or less.
The Libby vermiculite mining operation between 1967 and 1978 includes additional steps by the company to reduce dust exposure for workers. Most likely because it was apparent that there was a connection between airborne asbestos exposure health risks and smoking (tar in the lungs keeps particles therein), led Grace to ban smoking on premises in 1978, prompting a union grievance. And in 1983 Grace, complying with the Toxic Substances Control Act, filed notice of possible health effects from exposure to tremolite asbestos at the mining facility. The company consulted NIOSH, and McGill University began a health study of this topic in that same year. Findings of the McGill study, indicating that the levels of tremolite asbestos were one twentieth the standard set by federal regulations were reported to employees two years later in 1985.
The LIbby Montana vermiculite mine was closed by W.R. Grace corporation in 1990. In that year the company also closed all of its (more than 20) vermiculite insulation processing plants located throughout the U.S.
On 2 April 2001 the corporation filed for bankruptcy under Chapter 11 reorganization procedures in response to an 81% increase in asbestos claims in the preceding year and an increasing claims rate in 2001. According to the company, these asbestos liabilities stemmed from commercially-purchased chrysotile asbestos that Grace added to some of its fire protection products [not the tremolite asbestos found in Zonolite vermiculite building insulation-Ed]. The initial bankruptcy filing was amended on 13 January 2005, and disagreements between the company's creditors and stockholders and asbestosis property damage claimants continued along with further amendments to a final resolution on 31 January 2011.and all objections were closed on 31 January 2012. The corporation describes the final resolution as follows:
Vermiculite mining operations are found world-wide but the largest currently operating vermiculite mining operations continue in
Some Current Producers and/or Vendors of Vermiculite Products
Contemporary Uses of Vermiculite Insulation
Reader Question: accidental exposure of children to vermiculite insulation that might contain asbestos
We were researching when we found your website. We're currently remodeling our bathroom and found vermiculite insulation and the balsam wool insulation. We had no idea what either was and my 5 year old daughter and 2 year old sun were in the bathroom with me playing in the vermiculite insulation.
My wife and I feel like horrible parents after reading all about vermiculite insulation. She saw that you guys do testing but we read it can be expensive and the results can be skewed? we're not sure what to do or who to trust. I feel pretty good about the balsam wool insulation but your site seemed very knowledgeable and we read that we need to arrange something before sending out to your lab.
Sorry, I'm not able to perform testing of your insulation. To assure readers of our impartiality, in general we don't offer goods or services for sale.
I'm not sure you need to test as I elaborate below, but if you want to proceed you can use any certified asbestos test lab,
http://inspectapedia.com/hazmat/Asbestos_Test_Labs.htm will help you choose one.
Even if you test a sample and confirm that it contains asbestos I'm doubtful that that will change what you do about the loose insulation now. In any event it'd make sense to handle the material as if it contained asbestos - fine particulates are respiratory irritants regardless. Clean up using a HEPA vacuum cleaner, damp mopping, etc.
Don't berate yourselves. A limited, short term exposure to dust is unlikely to produce measurable effects. The people who developed asbestosis were generally workers in construction or in factories where the air was thick with material. I'm not cavalier about your kids, I've had kids, grandkids and so on myself but that's my OPINION, supported by some of the citations below such as Hughes (1994) and Vinikoor (2010)*.
Wash everybody and stay out of the dust. If you see the kids coughing consult with their pediatrician for follow-up. Take a look at the REFERENCES below for more details from the US EPA. Don't panic - doing so is likely to result in gouging by a clean-up conractor.
References on asbestos hazards from incidental or other vermiculite exposure
Some of these references on asbestos hazards from vermiculte exposure can be scary if you don't read them carefully. Noting the emphasis on the unusual nature of some of these cases means that non-occupational exposure to asbestos-containing vermiculite insulation has only rarely been linked to disease.
From Radon data & research we know that smokers have an 80 times higher risk of lung cancer from breathing in small harmful particles to which radon or its daughters were attached. Smoking is a risk multiplier that it seems to me probably pertained to asbestos hazards as well. Unless your kids are smokers, one might infer that their risk is further reduced.
Keep me posted
Green link shows where you are in this article series.
Frequently Asked Questions (FAQs)
What should I do if I have vermiculite insulation in my building ?
Quoting & paraphrasing or elaborating further from the U.S. EPA information on Vermiculite:
You should assume that the vermiculite insulation contains asbestos and it should not be disturbed. Particularly, do not stir up nor spread dust from this product.! Any disturbance could potentially release asbestos fibers into the air. If you absolutely have to go in your attic and it contains vermiculite insulation, you should limit the number of trips you make and shorten the length of those trips in order to help limit your potential exposure.
We and the US EPA recommend that you:
Our separate websites on Fiberglass building insulation and or series of articles about HVAC duct work defects contain in-depth discussion about possible air quality and health concerns which may be associated with exposure to fiberglass dust.To compare insulating material R-values of fiberglass in various forms as well as other insulating materials, see our Table of Properties of Insulating Materials
Also see these U.S. & Canadian Guides to Asbestos-Hazards in Vermiculite Insulation
How Vermiculite Attic Insulation Becomes Airborne
Any airborne dust particles can be a respiratory irritant, but the hazard level is likely to be increased if the dust contains insect or rodent materials and of course also if it contains asbestos as is present in some vermiculite insulation installations. Particularly where loose fill vermiculite insulation remains exposed in an attic, such as in the attic floor, the following act ivies are likely to cause dust from this product to become airborne.
You can reduce these dust risks by installing a plywood floor over the tops of the floor joists (ceiling joists of the rooms below), by installing fiberglass batts on top of the vermiculite, or by spraying an acrylic encapsulant on the exposed surface of the vermiculite in the attic.
Watch out: spray-coating the upper surface of an attic insulation material installed in the floor risks creating a vapor barrier on the wrong side (the cold side) of the structure, trapping moisture and leading to condensation or even mold troubles.
Question: is .0004% of asbestos ok to be working in and preparing food in?
I work in a school in mt, and 2 years ago this substance was removed from two rooms in the school, one which is right by the kitchen i work in. well 2 days ago i found this substance on top the the cupboards and everywhere else, and can see that it is falling from the ceiling. Very concerned because i have a fan blowing in there, and there was asbestos in the school when they came and had it cleaned. my question to you is, is .0004% of asbestos ok to be working in and preparing food in?
i truly found this site excellent, it answered alot except that one question. thank you - Amy Swanson 9/2/11
Thanks for tine nice note Amy.
Well this is my first year at this school, and was told that 2 years ago there was asbestos in the library and the music room and they did have it cleaned up professionally, but they didn't do it to the kitchen.
now this stuff that looks like your picture above with the gold and silver flakes in is is all over my kitchen and my boss told me it wasn't harmful cause they had it tested and it was at .0004%, but my concern is that if they had to clean it out of the other 2 rooms that it should be also done to my kitchen and i have 2 other ladies that work with me and we are all really concerned and are wondering what it is or whom it is that we can contact because everyone is telling us its ok and i don't think it is ok.
my boss is having someone come out there to caulk the ceiling again, and that is it...more or less just sweeping this under the rug. ..i have some of this stuff that fell from the ceiling in a plastic folder. it was hanging on the wall and caught it, but my concern is that i didn't know it was in there at the time i pulled a few papers out of it.
that is how it was brought to my attention of what it was. i am seriously concerned and would just like to know whom it is i need to contact outside the school, since no one in the school seems to really care about it or us.
Question: Zonolite Rolled Glass Fiber Home Insulation
i got zonolite rolled glass fiber home insulation is it safe ? - Concerned
Concerned: I don't recognize the product you name - can you send me a photo of the material and of any labels or markings on packaging? Then I can research and comment further. Use the CONTACT US link at page top or bottom to send photos if you can.
Certainly "fiberglass" is not an asbestos material. In our opinion, fiberglass insulation is safe if it has been properly installed and has not been damaged. Severely damaged fiberglass insulation, such as a product that has been walked-upon numerous times, or that has been macerated during demolition, may produce high levels of glass fiber dust, including small particles that may are a respiratory irritant and may be more harmful.
Should I have my Attic Insulation Tested?
I found plastic bags in my attic space that say "Full Fill" Insulation 100% abestos free from Koos Inc. Kenosha, WI. Should I have the insulation tested? - Colleen 3/4/12
Reply: U.S. EPA Koos WI Site Visit Report on Vermiculite & Asbestos Exposure
Colleen, some mesothelioma and asbestosis websites, usually ones seeking to provide legal services, report that workers at Koos corporation in Wisconsin were exposed to dangerous levels of asbestos. The U.S. EPA visited the Koos site in Kenosha, WI on 9 March 2000. Here are two reports from the U.S. Government Accounting Office.
Therefore, while the "safe answer" is to spend your money testing your insulation, and given only the information in your brief question, we caution that as we report in detail in the article above, even if your insulation is a vermiculite product (you did not say that it was), a bulk test can give a false negative result. Therefore the EPA and other experts advise that consumers assume that their vermiculite contains asbestos and follow EPA's advice to leave the material alone, undisturbed.
Question: What are the chances that vermiculite in our home came from the Libby Mine?
I have a house in Massachusetts that was constructed circa 1770. Local lore has it that there was an attic fire circa 1890. The wood work and plaster indicate that the attic was "finished" circa 1900. Some floor boards are missing, the floorboards are 1" hard pine, T&G. They also indicate late 19th, early 20th century. The floorboards were removed in the 1950's for electrical wiring (I am certain vermiculite was not added at that time). I can see about 1 1/2 inches of vermiculite between the joists.
Watch out: It might be useful to have your vermiculite insulation tested. If the result shows Tremolite asbestos (vermiculite mined at Libby Montana had a 10% Tremolite asbestos content) that probably points to the Libby vermiculite mine. But the US EPA warns that bulk testing of vermiculite for asbestos content can sometimes lead to a false negative finding (failing to detect asbestos even though it is present). That's a reason that the US EPA warned that people should err on the side of caution, assuming that it is asbestos-contaminated.
We also are researching the question of whether or not one can report a contents profile that would let one assay a vermiculite sample and guess at its source - as can be done very accurately with roofing slates. We will add that information here.
Question: Insulation in a 1969 house looks like white and gray furry stuff - is this vermiculite or asbestos?
I am buying a house that was build in 1969. I have not tested the insulation yet (I will). However, it doesn't looks like any of the above pictures. It looks like white and gray and furry. Are there still chance for the insulation to contain vermiculite or asbestos? - Will 7/12/2012
Question: was asbestos-contaminated vermiculite imported into the U.K.?
Are you aware if any of this contaminated vermiculite was imported to the UK? Thank you. - Laurence 9/15/2012
Sorry Laurence, no I don't know.
Typically, because of price competition and the importance of shipping costs, insulation products are produced and shipped from locations a bit closer to their point of use.
Question: where can I have a sample of vermiculite insulation to have it tested?
I recently purchased a house from HUD. I had my home inspected and found out there is exposed vermiculite in the basement that has fallen to the floor and is now been tracked around. Where can I take a sample of this insulation to have it tested ? - Tim 9/16/2012
Tim, you can use any test laboratory certified for asbestos testing. Both the US EPA and many U.S. states or Canadian provinces maintain lists of currently-approved asbestos testing labs.
Most state and provincial governments regulate and certify asbestos testing laboratories, and we recommend that where there are health, legal, or cost concerns, you should only use a certified and competent asbestos testing laboratory to examine material samples for asbestos content.
We give a list of several ways to find a certified asbestos test lab at ASBESTOS TEST LABS.
Question: worried sick after our home inspector tested our "vermiculite insulation" for asbestos - lab said it was cellulose
I recently bought a 1940s house which upon inspection was suspected to have vermiculita in a small area of the attic. The home inspector got it tested and it came back composed of cellulose and non fibrous materials, no asbestos. fast forward a few months we are now having our batting insulation replaced and the guys doing the work tell us its vermiculite. What do we go by? we also had our contractor tell us that its not vermiculite...im worried sick that now that the batting insulation is being removed, asbestos fibers might flying all over our house! - Worried sick., 10/5/2012
Reply: cellulose is not vermiculite and is not asbestos; but one insulation sample may not represent all building insulation in the structure
You might be best off trying to not be worried sick, as that itself may be an immediate health hazard and also invites opportunists who may price-gouge you when they see that you're terrified. Scared means costly.
Provided your home inspector used a qualified forensic or asbestos test lab (see Where to Find a Certified or Accredited Asbestos Testing Laboratory), I'd trust their lab result for the insulation sample that was actually tested.
I am a little surprised that your home inspector could not himself tell the very obvious difference between cellulose building insulation and vermiculite insulation. They are not at all visually similar. Why did he test cellulose (Cellulose loose fill insulation - basically paper) for asbestos? Did he charge you a profit beyond the actual lab fee for that test?
I am not surprised that workers may have found vermiculite insulation in a 1940's house; Vermiculite was widely used as a pour-in insulation retrofit and often a 1940's home was originally built with little or no insulation to start with. In the 1970's many of us (including myself) added various insulation products, including vermiculite, in those homes.
By taking a look at the photographs in this article, even a child should be able to see the difference between vermiculite and other building insulation products. Our photo above shows a typical blown-in cellulose insulation installation. If indeed your workers are correct and vermiculite is in place, you should
Question: did Vermiculite Insulation sold in the U.K. (Ireland in this case) contain asbestos?
I hope you can help me with a query I have. [Paraphrasing at reader request]: there was a vermiculite spill in my home in Ireland. How do I make sure that the home has not been contaminated with asbestos?
Reply: Dust sampling theory: usefulness & definitions of "old dust" and "recent dust" in buildings & where these are found
In an effort to be more clear about dust sampling theory I have expanded the descriptions of old dust, recent dust, where such samples are usually found, and why one would collect them for analysis - that discussion is now found at
DUST SAMPLE TYPES
The vermiculite spill was not professionally cleaned, and was swept and vacuumed with a standard household vacuum cleaner by the plumber before I ever knew what vermiculite was
Thanks for the follow-up; Ordinary vacuuming actually increases the level of fine particulates; HEPA vacuuming would have been in order if we thought that asbestos was present, along with damp wiping of horizontal surfaces.
Most likely, from your case history, you're ok. If you want to get a settled-dust sample analyzed just send it to a certified asbestos testing laboratory and allow them to choose their method of analysis; typically the lab uses polarized light microscopy following the Walter McCrone procedure. Some asbestos test labs may also make use of other methods such as SEM; any certified lab will use appropriate asbestos identification procedures - as an amateur I would not second guess the lab ty telling them what to do, just make sure the sample is collected and question posed following their requrested procedure.
Questions & answers or comments about vermiculite insulation & asbestos.
Use the "Click to Show or Hide FAQs" link just above to see recently-posted questions, comments, replies, try the search box just below, or if you prefer, post a question or comment in the Comments box below and we will respond promptly.
Search the InspectApedia website
HTML Comment Box is loading comments...
Technical Reviewers & References