Question? Just ask us!
Free Encyclopedia of Building & Environmental Inspection, Testing, Diagnosis, Repair
InspectAPedia ® Home
ELECTRICAL INSPECTION, DIAGNOSIS, REPAIR
ACCURACY vs PRECISION of MEASUREMENTS
AFCIs ARC FAULT CIRCUIT INTERRUPTERS
ALUMINUM SECs & WIRING
ALUMINUM WIRING HAZARDS & REPAIRS
AMPS VOLTS DETERMINATION
AMPERAGE MEASUREMENT METHODS
AMPACITY - the LIMITING FACTOR
APPLIANCE EFFICIENCY RATINGS
BACKUP ELECTRICAL GENERATORS
BOOKSTORE - ELECTRICAL
BUILDING SAFETY HAZARDS GUIDE
Cadet & Encore Heater Recall
CIRCUIT BREAKER FAILURE
CIRCUIT BREAKER SIZE for A/C or HEAT PUMP
Classified CIRCUIT BREAKER WARNING
CORROSION in ELECTRICAL PANELS
CORROSION & MOISTURE SOURCES in PANELS
CUTLER HAMMER PANEL FIRE
DEFINITIONS of ELECTRICAL TERMS
DIRECTORY OF ELECTRICIANS
DMM Digital Multimeter HOW TO USE
ELECTRIC METERS & METER BASES
ELECTRIC MOTOR DIAGNOSTIC GUIDE
ELECTRIC MOTOR OVERLOAD RESET SWITCH
ELECTRIC PANEL INSPECTION
EMF RF FIELD & FREQUENCY DEFINITIONS
ELECTRICAL GROUND SYSTEM INSPECTION
EMF RF FIELD & FREQUENCY DEFINITIONS
FIRE SAFETY Checklist, CPSC
GFCI PROTECTION,Testing GFCIs AFCIs
HEATING COST FUEL & BTU COST TABLES
HEAT TAPE USAGE GUIDE
Hertz - Definitions of KHz MHz GHz THz
KNOB & TUBE WIRING
LIGHTING, EXTERIOR GUIDE
LIGHTING, INTERIOR GUIDE
LIGHTNING PROTECTION SYSTEMS
LOW VOLTAGE BUILDING WIRING
LOW VOLTAGE TRANSFORMER TEST
MAIN ELECTRICAL DISCONNECT
MAIN DISCONNECT AMPACITY
MOISTURE SOURCES in PANELS
MURRAY SIEMENS Recall
PHOTOVOLTAIC POWER SYSTEMS
PUSHMATIC - BULLDOG PANELS
REMOTE ELECTRIC POWER, PHOTOVOLTAIC
RUST in ELECTRICAL PANELS
SAFETY for ELECTRICAL INSPECTORS
SE CABLE SIZES vs AMPS
SIEMENS MURRAY Recall
THERMAL EXPANSION of HOT WATER
THERMAL EXPANSION of MATERIALS
UNDERGROUND SERVICE LATERALS
VOLTS / AMPS MEASUREMENT EQUIP
VOLTAGE MEASUREMENT METHODS
WIND ENERGY SYSTEMS
WIND TURBINES & LIGHTNING
ZINSCO SYLVANIA ELECTRICAL PANELS
This article series describes common lightning protection systems, certification, installation, and lightning protection system inspection. We provide information about lightning strikes, lightning hazards, related equipment, sources of lightning protection system installers, and lightning strike risk assessment
Green links show where you are. © Copyright 2014 InspectApedia.com, All Rights Reserved.
[Click to enlarge any image]
So it's job is both to provide a path for the lightning strike to reach ground (instead of reaching the ground through the building or its components), and to avoid damaging the building as the electrical current of the lightning bolt flows through the protection system components. In other words, a lightning rod and its components do not prevent a lightning strike, rather they give it a safer pathway to earth than would occur if the energy passed through building components on the way down.
The basic components of a lightning protection system include the following
As we mentioned above, a lightning protection system does not prevent lightning from striking; it provides a means for controlling it and preventing damage by providing a low resistance path for the discharge of lightning energy. This means that the energy from a lightning strike is directed along a heavy metal cable from an air terminal or other protection device down to a rod driven into the earth.
If an easier path is not provided for the energy (or current) to flow to earth, the energy from the lightning strike will find its own, often remarkably odd, pathway to earth anyway, perhaps moving on building water piping, electrical wiring, or even through damp timbers.
When the tremendous energy of a lightning strike moves through these building components instead of through a desired and safest cable designed for that purpose, damage to the building is likely, including explosion, fire, or electrical damage.
But lightning protection systems have a confusing history. The earliest lightning rod design, by Ben Franklin in 1752, ended in a sharp pointed trident which may have actually created an electrical field around the tip which invited strikes.
You'll notice that modern lightning rods have a short blunt tip and that they are connected to earth by heavy metal cables, often using braided copper. Having a properly-designed lightning protection system is very important if you're going to have one at all, since an improperly designed or installed system might actually increase the chances of a building being damaged by a lightning hit.
Lightning strikes at buildings and other sudden electrical currents (such as a tree touching a high tension power line) produce very high voltages which can take surprising routes at a property such as following underground tree roots, metal porch railings, and copper or steel building water pipes.
Lightning protection may be needed for tall trees on a property, either to protect the trees themselves from damage, or to avoid subsequent tree damage to nearby buildings if the tree is stuck.
As a child on the Rappahannock river in Virginia I watched storms come up the river as a solid front of rain and lightning. Our house (photo at left), had been built in the 1930's and sat high on a hill overlooking the Rappahannock river. Built originally as a farmhouse, the building had a standing seam metal roof and had been protected with a lightning rod system.
[Click to enlarge any image]
But we regularly saw nearby trees take a strike. The energy from the lightning strike appeared to vaporize the sap within the tree, causing it to literally explode outwards.
I have also inspected a home damaged by an indirect electrical strike which originated below an electrical power transmission line at a nearby tree, traveled down the tree under the garage concrete slab, exploding the slab (there was perhaps water below the slab), blowing the car up through the garage roof.
The electrical energy from this strike continued, following the roots of the tree across the property, up a metal entry stair railing, and into metal siding on the home and into the home's metal water supply piping system. Aluminum rivets holding corner trim onto the aluminum-sided home melted and the siding corner trim fell to the ground. The water main melted, leaving a burst and leaking water entry line which then flooded the home's basement.
See LIGHTNING PROTECTION for TREES for more details of protecting trees from lightning strikes.
Green link shows where you are in this article series.
Frequently Asked Questions (FAQs)
No FAQs have been posted for this page. Try the search box below or CONTACT US by email if you cannot find the answer you need at InspectApedia.
Use the "Click to Show or Hide FAQs" link just above to see recently-posted questions, comments, replies, try the search box just below, or if you prefer, post a question or comment in the Comments box below and we will respond promptly.
Search the InspectApedia website
HTML Comment Box is loading comments...
Technical Reviewers & References