Question? Just ask us!
Free Encyclopedia of Building & Environmental Inspection, Testing, Diagnosis, Repair
InspectAPedia ® Home
ELECTRICAL INSPECTION, DIAGNOSIS, REPAIR
ACCURACY vs PRECISION of MEASUREMENTS
AFCIs ARC FAULT CIRCUIT INTERRUPTERS
ALUMINUM SECs & WIRING
ALUMINUM WIRING HAZARDS & REPAIRS
AMPS VOLTS DETERMINATION
AMPERAGE MEASUREMENT METHODS
AMPACITY - the LIMITING FACTOR
APPLIANCE EFFICIENCY RATINGS
BACKUP ELECTRICAL GENERATORS
BOOKSTORE - ELECTRICAL
BUILDING SAFETY HAZARDS GUIDE
Cadet & Encore Heater Recall
CIRCUIT BREAKER FAILURES
CIRCUIT BREAKER SIZE for A/C or HEAT PUMP
Classified CIRCUIT BREAKER WARNING
CORROSION in ELECTRICAL PANELS
CORROSION & MOISTURE SOURCES in PANELS
CUTLER HAMMER PANEL FIRE
DEFINITIONS of ELECTRICAL TERMS
DIRECTORY OF ELECTRICIANS
DMM Digital Multimeter HOW TO USE
ELECTRIC METERS & METER BASES
ELECTRIC MOTOR DIAGNOSTIC GUIDE
ELECTRIC MOTOR OVERLOAD RESET SWITCH
ELECTRIC PANEL INSPECTION
EMF RF FIELD & FREQUENCY DEFINITIONS
ELECTRICAL GROUND SYSTEM INSPECTION
EMF RF FIELD & FREQUENCY DEFINITIONS
FIRE SAFETY Checklist, CPSC
GFCI PROTECTION,Testing GFCIs AFCIs
HEATING COST FUEL & BTU COST TABLES
HEAT TAPE USAGE GUIDE
Hertz - Definitions of KHz MHz GHz THz
KNOB & TUBE WIRING
LIGHTING, EXTERIOR GUIDE
LIGHTING, INTERIOR GUIDE
LIGHTNING PROTECTION SYSTEMS
LOW VOLTAGE BUILDING WIRING
LOW VOLTAGE TRANSFORMER TEST
MAIN ELECTRICAL DISCONNECT
MAIN DISCONNECT AMPACITY
MOISTURE SOURCES in PANELS
MURRAY SIEMENS Recall
PHOTOVOLTAIC POWER SYSTEMS
PUSHMATIC - BULLDOG PANELS
REMOTE ELECTRIC POWER, PHOTOVOLTAIC
RUST in ELECTRICAL PANELS
SAFETY for ELECTRICAL INSPECTORS
SE CABLE SIZES vs AMPS
SIEMENS MURRAY Recall
THERMAL EXPANSION of HOT WATER
THERMAL EXPANSION of MATERIALS
UNDERGROUND SERVICE LATERALS
VOLTS / AMPS MEASUREMENT EQUIP
VOLTAGE MEASUREMENT METHODS
WIND ENERGY SYSTEMS
WIND TURBINES & LIGHTNING
ZINSCO SYLVANIA ELECTRICAL PANELS
Examples & photos of damaged lightning protection system components & suggestions for how to inspect lightning protection systems are outlined here. This article series describes common lightning protection systems, certification, installation, and lightning protection system inspection. We provide information about lightning strikes, lightning hazards, related equipment, sources of lightning protection system installers, and lightning strike risk assessment. Our page top photo is of the remains of a lightning protection system found on a Poughkeepsie NY home built ca 1935.
Green links show where you are. © Copyright 2015 InspectApedia.com, All Rights Reserved.
We took these photographs of a damaged lightning protection system on an 1865 house in Orange County, New York. (Newburgh NY).
[Click to enlarge any image]
The air terminal and conductor were bent down away from the top of the home leaving the chimney and roof (a metal one in an area of frequent lightning strikes) unprotected.
This is an example of what can happen when someone who is not qualified works on the system.
The lightning protection system for this home was dangerously compromised when the maintenance crew simply bent components down out of their way.
[The photographs of details of an old lightning protection system shown here were NOT the work of any of the companies or sources described at this website.]
Example of an Improperly Abandoned Lightning Protection System
The two photographs just below show the remains of the grounding connections for a lightning arrestor system that was installed on a Poughkeepsie New York Home.
Leaving an incomplete lightning protection system on a building may actually be worse than having nothing at all, as especially combined with a masonry chimney (wet, conductive in a storm), a copper chimney cap, and a remaining lightning rod that is no longer connected to ground, this system may be saying to nature "go ahead, hit me!".
The arrow at upper left points to the lightning protection air terminal electrode, and the arrow at lower right in our photo points to the conductor cable that was cut off, perhaps by the roofers or by the house painters when they found that the lightning protection system wiring was "in the way".
We recommend removing rooftop electrodes and conductors that are no longer connected to ground, or if you believe that the original owner and installer felt that there was a reason for installing this system, it should be repaired by an expert.
Inspection tips for Lightning Protection Systems
Green link shows where you are in this article series.
Frequently Asked Questions (FAQs)
No FAQs have been posted for this page. Try the search box below or CONTACT US by email if you cannot find the answer you need at InspectApedia.
Use the "Click to Show or Hide FAQs" link just above to see recently-posted questions, comments, replies, try the search box just below, or if you prefer, post a question or comment in the Comments box below and we will respond promptly.
Search the InspectApedia website
HTML Comment Box is loading comments...
Technical Reviewers & References