Question? Just ask us!
Free Encyclopedia of Building & Environmental Inspection, Testing, Diagnosis, Repair
InspectAPedia ® Home
OIL STORAGE TANKS - home
ABANDONING OIL TANKS
ABOVE GROUND OIL TANK (AST) GUIDE
BURIED OIL TANK (UST) GUIDE
HEATING OIL TYPES & PROPERTIES - home
HOME BUYERS GUIDE TO OIL TANKS
OIL SPILL CLEANUP / PREVENTION
OIL TANK ABANDONING PROCEDURE
OIL TANK INSPECTION & TROUBLESHOOTING
OIL TANK LEAKS & SMELLS
OIL TANK PIPING & PIPING DEFECTS
OIL TANK REGULATIONS
OIL TANK REMOVAL COs
OIL TANK SPILL CLEANUP / PREVENTION
OIL TANK LEAK TEST METHODS
OIL TANK TESTING & REMOVAL COs
OIL TANK WATER CONTAMINATION
Above ground heating oil storage tank - AST inspections outdoors:
How to inspect above ground oil storage tanks (ASTs) when they are installed above ground outdoors: This article discusses the risks of heat loss or leaks when above-ground outdoor oil storage tanks are used outside. It explains how water gets into oil storage tanks no matter where they are located, above ground oil tanks, buried oil tanks, or even possibly indoor oil tanks. Photograph at page top courtesy of Arlene Puentes.
Green links show where you are. © Copyright 2015 InspectApedia.com, All Rights Reserved.
The article explains the problems caused by water in oil tanks and also the problems faced by owners of above ground oil storage tanks located in cold climates. This article is a sub-chapter of OIL TANK INSPECTIONS
[Click to enlarge any image]
This article, sketchs, and photographs give advice and example photos for the visual inspection of above ground oil tanks for leaks and damage including damaged or leaky oil storage tanks, improper oil tank piping, valves, and indoor-type oil tanks located outdoors.
Sketch of an above ground outdoor oil storage tank is courtesy of Carson Dunlop Associates.
Here are a some important indicators of tank condition that any home inspector can include when an oil storage tank is visible and accessible inside or at a building.
Oil Tank Size and Rating for indoor use but Used Outdoors: If you find a 250g or 275g oil storage tank above ground outside, check its label and UL rating to see if that location was permitted.
Similarly, if you learn that a buried oil tank is an older, small-capacity tank such as 250g or 275g, it is reasonable to assume that an "indoor use only" oil storage tank was buried outside, as we have not located a single instance of a 20 year old 250/275 gallon oil storage tank which was tested, UL-Labeled, and rated for outdoor use above ground nor underground.
Such oil tanks often need to be replaced. Unfortunately so many indoor oil tanks have been used outside, above ground or buried, that their use has been so popular that UL standards for labeling and controlling oil tank use are a bit more confusing.
Modern oil tank labels might no longer indicate if the tank is intended for outdoor use or not, and modern oil tank manufacturers may have rated tanks which were previously labeled "indoors" as now suitable for outdoor use or even buried-use.
Check with the manufacturer of your oil tank before moving it, using it outdoors, or burying it.
How Water Gets Into Oil Storage Tanks
Water can enter an oil storage tank by more than one means:
Problems Caused When Water Enters an Oil Storage Tank?
What happens when an oil tank is outdoors? Water can enter the oil storage tank where it causes possibly serious problems for the heating equipment.Water in the fuel oil or simple exposure of the oil to cold temperatures can lead to loss of heat and resultant damage to a building by several means:
The photo shows an oil tank which is half buried outdoors under a deck. Was this tank intended for outdoor use at all? If so, was it intended for use when in contact with the ground? Probably not. The risk is tank rusting, water entry, oil leaks, and related problems we've already listed.
Outdoor oil tanks in cold climates risk loss of heat from freezing water or jelling fuel as we just cited. In the photo shown here the oil lines are taken off of the top of the oil tank so as to avoid picking up water that may be present in the tank, avoiding the icing problem.
Note that no heat tapes are in use on the oil lines (good, that reduces a fire risk). It looks as if there has been some seepage around these oil lines, that the tank is old, and that one tank is being used to serve two oil-fired devices (two sets of oil lines leaving the tank).
Water in oil tanks also often leads to internal corrosion and leaks in the tank itself, regardless of the tank location, though buried tanks and indoor oil tanks are less prone to water accumulation due to in-tank condensation in response to temperature changes than a tank located above ground outside.
Oil storage tanks usually fail from rust perforation due to combination of water inside the tank with sulphur in the fuel oil. External rust, unless very heavy, isn't highly correlated with internal rust. A new tank, when required, may cost more $2000. installed, including removal of the old oil tank.
When an outdoor tank is exposed to these conditions and even for an indoor tank which we suspect has had a dose of water and sludge, we recommend regular use of a fuel oil additive such as 4 in 1 Hot(TM) to absorb water and to help break up sludge. The best solution is to locate the tank indoors or to build a heated shelter over the outdoor tank.
In cold climates, heating or fuel oil additives for above-ground outdoor oil tanks can help prevent loss of heat by adding a pour point depressant which lowers the temperature at which the heating oil will form waxes or jell, and by adding a chemical, typically an alcohol, to remove [small amounts] of water from the oil.
I've used a product called "4-in-One Hot" which
contains both a sludge break-up chemical and alcohol to help remove water from the heating oil. Such additives may indeed
help break up sludge which tends
to clog old heating oil lines.
Watch out: two warnings about using heating oil additives and chemicals for outdoor oil tanks:
Pour point depressants for heating oil tanks are about the same as similar products used by owners of diesel fuel powered automobiles and trucks in cold climates, but except in dire emergency I would not recommend substituting one for the other as there are some differences in these fuels and chemicals.
Note: these tips are not a complete oil tank installation guide. Proper installation must be done by trained service technicians and must comply with local building codes.
Readers whose heating system uses an above-ground outdoor oil storage tank should be sure to also
and OIL TANK SLUDGE.
Details about the various types of oil storage tank additives, treatments & chemicals and some warnings about their use are
Continue reading at OIL FILL & VENT PIPING or select a topic from the More Reading links shown below.
Suggested citation for this web page
Green link shows where you are in this article series.
Frequently Asked Questions (FAQs)
No FAQs have been posted for this page. Try the search box below or CONTACT US by email if you cannot find the answer you need at InspectApedia.
Use the "Click to Show or Hide FAQs" link just above to see recently-posted questions, comments, replies, try the search box just below, or if you prefer, post a question or comment in the Comments box below and we will respond promptly.
Search the InspectApedia website
HTML Comment Box is loading comments...
Technical Reviewers & References