Question? Just ask us!
Free Encyclopedia of Building & Environmental Inspection, Testing, Diagnosis, Repair
InspectAPedia ® Home
OIL STORAGE TANKS
ABANDONING OIL TANKS
AGE of OIL TANK
ANODES & DIP TUBES on WATER HEATERS
BURIED OIL TANK ADVICE
BURIED OIL TANKS, FINDING
COMBUSTION PRODUCTS & IAQ
DEFINITION of Heating & Cooling Terms
DIAGNOSE & FIX HEATING PROBLEMS-BOILER
DIAGNOSE & FIX HEATING PROBLEMS-FURNACE
DIRECTORY of OIL TANK EXPERTS
FILTERS, OIL on HEATING EQUIPMENT
FIRE SAFETY CONTROLS
FLOATING UP OIL STORAGE or SEPTIC TANKS
FLOODED HEATING EQUIPMENT REPAIR
FLOODED WATER HEATER REPAIR
FUEL OIL TYPES & CHARACTERISTICS
FUEL UNIT, HEATING OIL PUMPS
GALVANIC SCALE & METAL CORROSION
GAUGES ON HEATING EQUIPMENT
HEAT TAPES, Heat, Insulation prevent Freeze-Up
HEATING COST FUEL & BTU Cost Table
HEATING COST SAVINGS METHODS
HEATING OIL CLOUD WAX GEL POINT
HEATING OIL EXPOSURE HAZARDS, LIMITS
HEATING OIL - OLD, USEABLE?
HEATING OIL PIPING TROUBLES
HEATING OIL SHELF LIFE
HEATING OIL SLUDGE
HEATING OIL TANKS
HEATING OIL TYPES & PROPERTIES
HEATING OIL USAGE RATE
HEATING SYSTEM NOISES
HOME BUYERS GUIDE TO OIL TANKS
NOISE CONTROL for HEATING SYSTEMS
NOISES COMING FROM WATER HEATER
ODORS & SMELLS DIAGNOSIS & CURE
ODORS FROM HEATING SYSTEMS
OIL FILTERS on HEATING EQUIPMENT
OIL FUEL TYPES & CHARACTERISTICS
OIL FILL PIPE LEAKS
OIL SPILL CLEANUP / PREVENTION
SOOT on OIL FIRED HEATING EQUIPMENT
STAIN DIAGNOSIS on BUILDING INTERIORS
THERMAL TRACKING & HEAT LOSS
VIDEO GUIDES: Heating System Videos
VIDEO GUIDES - InspectAPedia.com
WINTERIZE A BUILDING
This is a photo guide to visual clues spotted first outdoors and second indoors to help detect and locate abandoned or buried oil tanks or the detection of evidence that an underground (or even an above ground) oil tank is or was in use at a property. The article and photographs used to show the reader ways to find buried oil tanks include examples of clues leading to the discovery of "nearly hidden" buried or underground oil tanks which were found at residential properties and which avoided very costly surprises later for the new owner.
Underground oil storage tanks, or UST's, whether still present or previously removed, involve a risk of costly oil leaks and soil contamination which may need to be addressed. Here are some investigation methods that any home buyer, owner, or home inspector can apply to reduce these risks by looking for evidence that a buried oil tank is or was at a property. Also see Above Ground Oil Tanks: Visual Inspection.
Green links show where you are. © Copyright 2013 InspectAPedia.com, All Rights Reserved.
SIGNS OF BURIED OIL TANKS- A Photo Guide to Visual Clues for Finding Buried Oil Storage Tanks - Part 1, Outdoor Clues
How to find buried oil tanks: Evidence that a buried fuel storage tank exists at a property may be direct and visually obvious, or the evidence may be subtle. Mark Cramer's photo (left) shows a pair of painted-over copper pipes penetrating a building foundation wall close to ground level - a strong suggestion of a buried oil tank at this property.
Often a series of small observations, individually not apparently very important, can add up to an increased probability that a buried fuel storage tank is or was at a property.
While environmental investigators and oil tank test companies may use magnetic scanners or even ground scanning radar to locate buried steel tanks, an astute visual inspection can often discover the presence or probable presence of a buried fuel storage tank at a property, thus suggesting that further testing is definitely in order. Here are some clues to the possible current or past presence of a buried tank at a property.
Visible oil tank fill or vent pipes protruding from the ground or flush with the ground anywhere on a property.
Mark Cramer's photo (above right) shows an oil tank fill pipe cap (rust-colored round object closer to the building wall) and an oil tank vent pipe cap (silver colored object) . Placing the oil tank vent pipe cap at ground level was probably a cosmetic decision by the homeowner, but if that area of missing leaves marks a spill line from roof runoff, we're also asking for a problem with water in the oil tank at this home.
Frequently Asked Questions (FAQs)
No FAQs have been posted for this page. Try the search box below or CONTACT US by email if you cannot find the answer you need at InspectApedia.
Use the search box below to ask a question or to search the InspectApedia.com website.
Ask a Question or Enter Search Terms in the InspectApedia search box just below.
Technical Reviewers & References
Related Topics, found near the top of this page suggest articles closely related to this one.