Question? Just ask us!
Free Encyclopedia of Building & Environmental Inspection, Testing, Diagnosis, Repair
InspectAPedia ® Home
OIL STORAGE TANKS - home
ABANDONING OIL TANKS
ABOVE GROUND OIL TANK (AST) GUIDE
BURIED OIL TANK (UST) GUIDE
HEATING OIL TYPES & PROPERTIES - home
HOME BUYERS GUIDE TO OIL TANKS
OIL SPILL CLEANUP / PREVENTION
OIL TANK ABANDONING PROCEDURE
OIL TANK INSPECTION & TROUBLESHOOTING
OIL TANK LEAKS & SMELLS
OIL TANK PIPING & PIPING DEFECTS
OIL TANK REGULATIONS
OIL TANK REMOVAL COs
OIL TANK SPILL CLEANUP / PREVENTION
OIL TANK LEAK TEST METHODS
OIL TANK TESTING & REMOVAL COs
OIL TANK WATER CONTAMINATION
Heating oil storage tanks home page:
This oil tank information article series answers nearly all questions about above ground or buried oil storage tanks including oil tank inspection & testing, oil tank abandonment or removal, removal, oil storage tank & tank piping leak testing, leak prevention, and oil storage tank regulations.
We also provide details for heating oil storage tank installation, oil piping, oil piping gauges, controls, check valves, fire safety valves, and oil storage and piping system repairs.
Green links show where you are. © Copyright 2015 InspectApedia.com, All Rights Reserved.
Here we provide authoritative, extensive free un-biased oil storage tank inspection and testing advice for property buyers and owners.
Click to enlarge any image]
This document lets you know what to ask about oil storage tanks, what oil tank leak tests to order, how to interpret oil tank testing results, what to do if there is a buried fuel or petroleum storage tank at a property, what to do if there is or was a leaky oil storage tank or petroleum storage tank, and how to reduce the chances of an oil leak or oil spill in the future.
We include detailed information about underground (buried) oil storage tanks (USTs), aboveground oil storage tanks (ASTs), above ground fuel storage tanks, reporting and cleaning up oil tank leaks, and choosing among oil tank leak testing methods.
We discuss how to find buried oil tanks, how to remove or abandon oil tanks and how to recognize evidence that there was a previous oil tank at a property even if the oil tank may have been removed (or perhaps left buried in place). We discuss what to do if an oil tank has already been removed or abandoned.
We provide links to every U.S. state regulatory agency concerned with oil and other storage tanks and to regulatory agencies in Canada and other countries. Environmental damage from oil leaks, oil spill cleanup, are also discussed. We discuss oil spill cleanup, oil spill and odor remediation, and bio remediation, for fuel oil or heating oil.
LP Gas tanks are also addressed.
Home buyers and purchasers of other buildings using oil heating equipment should review the following oil storage tank articles
In-Depth Information on Oil Storage Tank & Piping Leaks & Odors
Does or Did Your Building Have an Oil Storage Tank?
What to do if an oil storage tank is or was installed at your property?
Buried oil tanks raise increasing environmental, safety, legal and economic concerns for home owners and home buyers because oil leaks underground or even within buildings can lead to both environmental damage and very costly cleanup operations.
Typical Cost to Abandon & Replace an Oil Storage Tank
Having to install a new above ground indoor oil storage tank involves significant expense, perhaps $2000. to $4000. to remove the old tank and install the new one.  Costs can be substantially higher in the event of extensive leakage and soil contamination.
Removing or abandoning a buried oil tank is more costly. If an oil tank has leaked the cost to clean up contaminated soils can be very significant, so much so that
a property buyer should not complete the purchase before questions about the condition of oil tanks, past or present at the property, and the chances of leaks from buried oil storage tanks have been answered satisfactorily.
Reporting Requirements for Heating Oil Storage Tanks
Home heating oil tanks are excluded from Federal Regulations about oil storage tank reporting and monitoring, but in almost every U.S. state or Canadian province, storage tanks are addressed by state or local DEP/DNR/DEC agencies and regulations. For example, in New York, even residential storage sites must be reported to the state DEC if more than 1100 gallons are stored at a single site. (A few U.S. states specifically exclude the regulation of storage tanks when used for home heating oil.)
In any case, should a home heating oil tank causes a release of oil into the environment, at that point the owner of the tank is not exempt from the other provisions of the State or Federal Regulations: the leak needs to be reported (often within two hours of observation), the source of leak/spill would have to be stopped, a site characterization would have to be completed, and appropriate corrective action (cleanup) would have to initiated, and the incident would have to be reported.
Who Checks for Leaky Oil Tanks?
Above ground oil tanks and clues for the presence of buried oil tanks are not usually examined during a pre-purchase home or building inspection unless specific prior test arrangements have been made.
Oil tank inspection, other than casual visual inspection for obvious leaks is not performed by such inspectors.
Oil tank tests for leaks, soil tests for oil contamination, soil tests for corrosivity, screening for evidence of prior or abandoned oil storage tanks, as well as oil storage tank removal or abandonment require that you use an appropriate expert.
However articles at this website outline easy on-site visual observations that any thoughtful observer can make to spot evidence of a present or previous buried tank and to spot evidence of leaks or other problems with above ground storage tanks.
From a previous use, a buried oil tank may be present or may have been present at a property now served by an indoor, above ground oil tank or even by LP or natural gas.
So don't assume that because you don't see a tank that none was ever used or present at a property.
If you just "scroll down" you'll miss some important articles.
Tank Removal Funding Assistance is available in some municipalities. See TANK REGULATIONS at page-left to find individual state or provincial agencies concerned with oil storage tanks.
Before completing purchase of a property that has or had a buried oil tank you need to have either had the tank removed, abandoned in place, or tested.
At end of the day, you need reliable documentation that shows that either there has been no leakage and a proper tank abandonment has been performed, or if there was leakage, that a proper cleanup has been performed.
If the oil storage tank is a newer buried model (perhaps a fiberglass or multi-walled oil storage tank) and if the oil tank is in good condition it may not need to be abandoned.
But if older oil storage tanks were used, were removed, or remain abandoned at the property you still need to satisfy the requirements of this paragraph. The discussion which follows explains the risks and gives detailed advice about what to do about buried or above ground oil tanks and tank leaks.
OIL TANK LIFE - Life Expectancy of Buried or Underground Oil Tanks
See OIL TANK LIFE for details about the life expectancy of oil tanks.
Also see OIL TANK FAILURE RATES
and see OIL TANK FAILURE CAUSES. Excerpts are below.
While we've found them lasting longer, a common life expectancy of buried oil tanks is 10-15 years. At about 20 years, the risk of leaks from buried steel oil tanks becomes significant. Leaks can occur earlier if a tank was damaged at installation or was not properly piped.
Even if you think the tank is ok, young, and not leaking, buried oil tanks, should be tested for water in the tank bottom. Water should be pumped out since it corrodes the tank and leads to leaks. Oil tank leaks can also be due to damage at time of installation, improper installation, corrosive soils, or piping defects. If the tank is to remain in use, ask your fuel supplier about using an additive or other methods to help remove water.
In New England for a two year period [1984-5] among customers who have buried heating oil tanks (16% of total customers) surveyors found an average of 1.7 tank leaks per thousand customers. They also found 2.5 fuel line leaks per 1000 customers. (Fuel Oil and Oil Heat magazine, August 1985 p.18.) We do not have similar data for buried gas tanks in residential application.
See OIL TANK LIFE for details about the life expectancy of oil tanks.
The rate or frequency of oil tank leaks or oil storage tank failures, focused on underground storage tanks or USTs,
is discussed in detail
TANK REGULATIONS outlines who, when, and how oil leaks and spills must be reported to environmental authorities.
Details about the causes of oil tank leaks can be read at OIL TANK LEAK CAUSES.
Below we present a summary of this topic. Sketch at left is provided courtesy of Carson Dunlop Associates.
Oil Tank Piping Leaks: Oil tank leaks may occur at buried piping connections as well. At least one study found that 82% of petroleum product storage tank leaks were not due to the tank itself but due to leaks in the piping system.
In-Tank corrosion of oil storage tanks: Underground fuel or heating oil storage tanks usually fail from rust perforation due to several effects of water inside the tank including, in the case of heating oil, combination of water with sulphur in the fuel, bacterial action, and other factors.
External rust on oil tanks, unless very heavy, isn't highly correlated with internal rust. Leaks can occur due to tank damage or at piping connections.
Oil Tanks in Corrosive Soils: Oil storage tank leaks are more likely if a steel tank has been buried in corrosive soil or if the tank was damaged during installation, such as gouging it or bouncing it off of a rock as it was placed into a hole for burying.
Delivery Oil Spills: occur around the tank fill pipe and range from trivial to more extensive requiring soil removal and cleaning. These leaks are usually obvious at the ground surface around the oil tank or tank filler.
Inadequate fill or vent pipe diameter is blamed by some for leaks at buried or above ground oil tanks, asserting that because oil tanks are filled under pressure from the oil delivery pumper-truck, a corroded, damaged, or poorly-plumbed oil storage tank, or one with a too-small vent opening, may not withstand the pressure of the filling process.
Indoor oil spills during tank fill or later from a leaky oil tank range from trivial local cleanup and deodorizing efforts to very serious contamination problems if an oil tank bursts during oil delivery (which I suspect is rare) and on occasions when an indoor oil tank has been removed but someone (some fool) has left the oil filler pipe installed on the building, and when subsequently an oil delivery is mistakenly made through the filler pipe onto the empty basement or crawl space floor. This may sound crazy but it actually happens.
Also see OIL TANK LIFE their life expectancy and life factors
and TANK FAILURE CAUSES discusses the causes of oil storage tank leaks in more detail.
The rate or frequency of oil tank leaks or oil storage tank failures, focused on underground storage tanks or USTs, is discussed
in detail at TANK FAILURE RATES provides Oil Tank Failure Data - Oil Tank Failure Rates - Oil Tank Leak Probability as a Function of Tank Age, Location, Condition, Soil Conditions and Other Factors.
Details about oil tank testing procedures and choices can be read
In addition to oil tank inspection, oil piping inspection, and oil tank testing to "pass" or "fail" an oil storage tank, more sophisticated tests are available to assess the chances that an existing heating oil storage tank has leaked or is likely to have a serious leak soon.
These include a oil tank corrosion analysis which adds to the basic tank inspection and tests
an assessment of the level of corrosion of the tank walls and thus the chances of its leaking or failure,
and soil corrosion or soil corrosivity evaluation which includes an evaluation of soil samples
collected from around the tank in order to assess the degree to which the soil in which the oil
tank has been buried will contribute to the process of corrosion of the (presumably steel)
buried oil tank.
Details about handling water in oil tanks can be read at OIL TANK WATER CONTAMINATION. Below we present a summary of this topic.
Testing for water in an oil tank (above ground oil tanks whether inside or outdoors, or buried oil tanks) is simple and can be done by any service person or even a homeowner.
Tank testing methods vary in risk to the tank, cost, invasiveness, length of time to complete, and more.
Since water in a heating oil tank can lead to loss of heat and related building damage we want to know if in-tank water is a problem at a given property.
There are several steps and test methods for finding water in an oil tank and for determining how much of a problem it is.
Water can enter a heating oil storage tank by several means
Details about oil spill or oil tank leak, cleanup, remediation, prevention, training, and regulations are found
and at OIL TANK LEAK CLEANUP GUIDE. Excerpts are below.
Oil Storage Tank Testing Companies, Oil Storage Tank Removal Companies - Oil Tank Testing, Removal, Consulting Environmental Service Companies
For details on cleaning up residential oil spills see OIL TANK LEAK CLEANUP GUIDE.
Also see OIL TANK TESTING & REMOVAL COs
and OIL TANK REMOVAL FINANCIAL AID links to see our most current list of companies providing oil tank testing or oil tank removal/abandonment services.
Oil Tank Removal or Abandonment Methods
Details about oil storage tank removal or abandonment methods are at OIL TANK ABANDONING PROCEDURE. A brief summary is below.
There are also proper methods of "abandoning" old unused buried tanks without actually excavating and removing them (provided there is not evidence of leakage). If a tank is not to be used, can involve significant expense. A proper abandonment procedure involves pumping out remaining fuel, confirming that there has been no leakage, cleaning the tank, and filling the tank with an approved filler, or removing it entirely. These measures, if required, involve significant expense.
Buried tank removal is handled by environmental services companies.
Usually the specialist arranges testing, excavation, and disposal. Or tanks
can be abandoned in place.
Environmental Issues & Regulations for Oil Tanks
Details about oil storage tank rules, standards, guidelines, and regulations are aT OIL TANK REGULATIONS A brief summary is below.
Also see OIL TANK LEGAL ISSUES.
In the U.S. and many other countries state DEP/DEC/DNR (Departments of Environmental Conservation or similar agencies) have programs for registering buried tanks at any site storing (typically) more than 1100 gallons of heating oil. Requirements for gas (auto fuel), or other fuels may be different. Eventually this concern may spread to smaller residential tanks. The concern is for leaks which contaminate the environment. Tanks located where they may leak into a local waterway or into the water supply are a special environmental concerns. (C)trap DJ Friedman.
Thanks to Eagle Eye Arlene Puentes for proofreading this article. 4/3/2013.
More Reading for People Buying a Home with an Oil Storage Tank
Continue reading at OIL TANK INSPECTION & TROUBLESHOOTING or select a topic from the More Reading links shown below.
Suggested citation for this web page
Green link shows where you are in this article series.
Frequently Asked Questions (FAQs)
No FAQs have been posted for this page. Try the search box below or CONTACT US by email if you cannot find the answer you need at InspectApedia.
Use the "Click to Show or Hide FAQs" link just above to see recently-posted questions, comments, replies, try the search box just below, or if you prefer, post a question or comment in the Comments box below and we will respond promptly.
Search the InspectApedia website
HTML Comment Box is loading comments...
Technical Reviewers & References