Question? Just ask us!
Free Encyclopedia of Building & Environmental Inspection, Testing, Diagnosis, Repair
InspectAPedia ® Home
OIL STORAGE TANKS
ABANDONING OIL TANKS
AGE of OIL TANK
ANODES & DIP TUBES on WATER HEATERS
BURIED OIL TANK ADVICE
BURIED OIL TANKS, FINDING
COMBUSTION PRODUCTS & IAQ
DEFINITION of HEATING & COOLING TERMS
DIAGNOSE & FIX HEATING PROBLEMS-BOILER
DIAGNOSE & FIX HEATING PROBLEMS-FURNACE
DIRECTORY of OIL TANK EXPERTS
FILTERS, OIL on HEATING EQUIPMENT
FIRE SAFETY CONTROLS
FLOATING UP OIL STORAGE or SEPTIC TANKS
FLOODED HEATING EQUIPMENT REPAIR
FLOODED WATER HEATER REPAIR
FUEL OIL TYPES & CHARACTERISTICS
FUEL UNIT, HEATING OIL PUMPS
GALVANIC SCALE & METAL CORROSION
GAUGES ON HEATING EQUIPMENT
HEAT TAPES, Heat, Insulation prevent Freeze-Up
HEATING COST FUEL & BTU Cost Table
HEATING COST SAVINGS METHODS
HEATING OIL TYPES & PROPERTIES
HEATING SYSTEM NOISES
HOME BUYERS GUIDE TO OIL TANKS
NOISE CONTROL for HEATING SYSTEMS
NOISES COMING FROM WATER HEATER
ODORS GASES SMELLS, DIAGNOSIS & CURE
ODORS FROM HEATING SYSTEMS
OIL FILTERS on HEATING EQUIPMENT
OIL FUEL TYPES & CHARACTERISTICS
OIL FILL PIPE LEAKS
OIL SPILL CLEANUP / PREVENTION
SOOT on OIL FIRED HEATING EQUIPMENT
STAIN DIAGNOSIS on BUILDING INTERIORS
THERMAL TRACKING & HEAT LOSS
VIDEO GUIDES: Heating System Videos
VIDEO GUIDES - InspectAPedia.com
WINTERIZE A BUILDING
This document explains (and expands on) the US EPA detailed suggestions on how to properly "abandon" or close an underground petroleum storage tank in place, that is, without having to excavate and remove it. This procedure is permitted if tests show that the tank has not leaked, and it can save a significant amount of the cost of oil tank removal and site repair to fill in the hole left behind. We have made minor edits to the original document for clarity and we include links to additional and more detailed information about oil storage tanks and other environmental concerns.
Here are the U.S. EPA Recommendations for Temporary or Permanent Abandonment of Underground Oil Storage Tanks with additional text and illustrations by InspectAPedia.com.
Also see ABANDONING OIL TANKS. Proper oil storage tank abandonment requires the use of good engineering practices, including consideration of the future condition of the tank. While the original of this article focused on commercial oil storage tanks, the concerns and steps should be examined by those abandoning residential oil tanks as well.
Green links show where you are. © Copyright 2014 InspectApedia.com, All Rights Reserved.
You can close your UST [underground oil storage tank or other underground storage tanks such as for farm diesel fuel or other liquids]] temporarily or permanently. In either case, [oil or diesel storage] tanks must be closed properly.
Image at left provided courtesy Carson Dunlop Associates.
[Failure to properly close a storage tank risks:
How do you Close an Oil Storage Tank TemporarilyYou may temporarily close your UST for up to 12 months by following these requirements for temporary closure:
After 12 months of temporary closure of an oil storage tank, you have three options:
EPA's choices are:]
How do I Close an Oil Storage Tank PermanentlyIf you decide to close your UST permanently, follow these requirements for permanent closure:
Safe Closure Is A Must
People who do not follow standard safety practices are killed or injured every year while closing or removing tanks. For a safe closure, you need qualified professionals who will use standard safety practices.
[DF: in addition to EPA's serious safety warning just above we add this property resale and contamination warning: we also have encountered "do it yourself" oil tank removal cases which prevented the owner from selling their home due to either an actual oil leak contamination of soils or the inability to document a proper oil tank removal.]
For more information on standard safety practices, UST owners and closure contractors should refer to "Closure of Underground Petroleum Storage Tanks," API Recommended Practice 1604 (1996), which is available from the American Petroleum Institute, 1220 L Street, NW, Washington, DC 20005, or call (202) 682-8000 for assistance. You can also visit API's Web site.
The video and companion booklet called "Tank Closure Without Tears: An Inspector's Safety Guide" are available from the New England Interstate Environmental Training Center at (978) 323-7929. You can also visit NEIWPCC's Web site.
Regulations addressing reporting of oil tank leaks and oil tank abandonment of oil tanks written various state and federal authorities are discussed in more detail at OIL TANK REGULATIONS - "Buried Tank and Above Ground Oil Tank Leak Reporting & Tank Abandonment Regulations"
Be sure to review the details on oil tank abandonment procedures at
Be SURE that the tank filler and vent are totally removed lest you get an un-wanted oil delivery. Don't laugh, it happens.
Frequently Asked Questions (FAQs)
No FAQs have been posted for this page. Try the search box below or CONTACT US by email if you cannot find the answer you need at InspectApedia.
Check the FAQs just above, try the search box just below, or if you prefer, post a question or comment in the Comments box below and we will respond promptly.
Search the InspectApedia website
HTML Comment Box is loading comments...
Technical Reviewers & References
Related Topics, found near the top of this page suggest articles closely related to this one.
Contents of this individual web page are derived from the US EPA document cited at Technical Reviewers above.