Question? Just ask us!
Free Encyclopedia of Building & Environmental Inspection, Testing, Diagnosis, Repair
InspectAPedia ® Home
OIL STORAGE TANKS
ABANDONING OIL TANKS
AGE of OIL TANK
ANODES & DIP TUBES on WATER HEATERS
BURIED OIL TANK ADVICE
BURIED OIL TANKS, FINDING
COMBUSTION PRODUCTS & IAQ
DEFINITION of HEATING & COOLING TERMS
DIAGNOSE & FIX HEATING PROBLEMS-BOILER
DIAGNOSE & FIX HEATING PROBLEMS-FURNACE
DIRECTORY of OIL TANK EXPERTS
FILTERS, OIL on HEATING EQUIPMENT
FIRE SAFETY CONTROLS
FLOATING UP OIL STORAGE or SEPTIC TANKS
FLOODED HEATING EQUIPMENT REPAIR
FLOODED WATER HEATER REPAIR
FUEL OIL TYPES & CHARACTERISTICS
FUEL UNIT, HEATING OIL PUMPS
GALVANIC SCALE & METAL CORROSION
GAUGES ON HEATING EQUIPMENT
HEAT TAPES, Heat, Insulation prevent Freeze-Up
HEATING COST FUEL & BTU Cost Table
HEATING COST SAVINGS METHODS
HEATING OIL CLOUD WAX GEL POINT
HEATING OIL EXPOSURE HAZARDS, LIMITS
HEATING OIL - OLD, USEABLE?
HEATING OIL PIPING TROUBLES
HEATING OIL SHELF LIFE
HEATING OIL SLUDGE
HEATING OIL TANKS
HEATING OIL TYPES & PROPERTIES
HEATING OIL USAGE RATE
HEATING SYSTEM NOISES
HOME BUYERS GUIDE TO OIL TANKS
NOISE CONTROL for HEATING SYSTEMS
NOISES COMING FROM WATER HEATER
ODORS GASES SMELLS, DIAGNOSIS & CURE
ODORS FROM HEATING SYSTEMS
OIL FILTERS on HEATING EQUIPMENT
OIL FUEL TYPES & CHARACTERISTICS
OIL FILL PIPE LEAKS
OIL SPILL CLEANUP / PREVENTION
SOOT on OIL FIRED HEATING EQUIPMENT
STAIN DIAGNOSIS on BUILDING INTERIORS
THERMAL TRACKING & HEAT LOSS
VIDEO GUIDES: Heating System Videos
VIDEO GUIDES - InspectAPedia.com
WINTERIZE A BUILDING
Oil tank fill & vent piping guide: this heating oil piping article gives advice and example photos for the installation, inspection, & leak troubleshooting of oil tank fill & vent piping for both buried and above ground oil storage tanks .
Green links show where you are. © Copyright 2014 InspectApedia.com, All Rights Reserved.
See our complete list of heating oil piping topics beginning at OIL TANK PIPING & PIPING DEFECTS. Also see additional visibly detectable oil tank defects listed at ABOVE GROUND OIL TANK (AST) GUIDE and Heating Oil Piping. Sketch provided courtesy of Carson Dunlop Associates.
Here are a some important indicators of tank condition that any home owner or home inspector can examine when an oil storage tank is visible and accessible inside or at a building.
The oil company recommends going to 2", and most new installations use a two-inch diameter vent pipe; we've seen vent piping as small as one inch on oil tanks. During fill fuel is delivered at an average rate of 60 or even 70 gallons per minute.
Improper or blocked oil tank air exit venting can place excessive stress on tank seams and piping. See OIL TANK PRESSURE for a detailed explanation.
Fill and Vent Piping for Duplex Heating Oil Storage Tanks
At buildings where two heating oil storage tanks are installed, typically indoors, this Audel Oil Burner Guide sketch shows the proper arrangement of fill piping, vent piping, and oil line piping leaving the tanks.
We have seen an alternative arrangement that provides a fill line only to the first tank, with the second tank filled by a second pipe exiting the top of the first oil tank - not an arrangement we recommend as this forces the first oil tank to be fully pressurized at the oil delivery truck pressure during fill-up of the second tank.
The piping shown in this Audel sketch is better. Details about piping of fill and vent and oil supply lines for duplex oil tanks are at DUAL OIL TANKS - PIPING.
Thanks to Arlene Puentes for technical editing, March 2010.
Green link shows where you are in this article series.
Frequently Asked Questions (FAQs)
No FAQs have been posted for this page. Try the search box below or CONTACT US by email if you cannot find the answer you need at InspectApedia.
Use the "Click to Show or Hide FAQs" link just above to see recently-posted questions, comments, replies, try the search box just below, or if you prefer, post a question or comment in the Comments box below and we will respond promptly.
Search the InspectApedia website
HTML Comment Box is loading comments...
Technical Reviewers & References