Question? Just ask us!
Free Encyclopedia of Building & Environmental Inspection, Testing, Diagnosis, Repair
InspectAPedia ® Home
OIL STORAGE TANKS
ABANDONING OIL TANKS
AGE of OIL TANK
ANODES & DIP TUBES on WATER HEATERS
BURIED OIL TANK (UST) GUIDE
BURIED OIL TANKS, FINDING
COMBUSTION PRODUCTS & IAQ
DEFINITION of HEATING & COOLING TERMS
DIAGNOSE & FIX HEATING PROBLEMS-BOILER
DIAGNOSE & FIX HEATING PROBLEMS-FURNACE
DIRECTORY of OIL TANK EXPERTS
FILTERS, OIL on HEATING EQUIPMENT
FIRE SAFETY CONTROLS
FLOATING UP OIL STORAGE or SEPTIC TANKS
FLOODED HEATING EQUIPMENT REPAIR
FLOODED WATER HEATER REPAIR
FUEL OIL TYPES & CHARACTERISTICS
FUEL UNIT, HEATING OIL PUMPS
GALVANIC SCALE & METAL CORROSION
GAUGES ON HEATING EQUIPMENT
HEAT TAPES, Heat, Insulation prevent Freeze-Up
HEATING COST FUEL & BTU COST TABLES
HEATING COST SAVINGS METHODS
HEATING OIL CLOUD WAX GEL POINT
HEATING OIL EXPOSURE HAZARDS, LIMITS
HEATING OIL - OLD, USEABLE?
HEATING OIL PIPING TROUBLES
HEATING OIL SHELF LIFE
HEATING OIL SLUDGE
HEATING OIL TANKS
HEATING OIL TYPES & PROPERTIES
HEATING OIL USAGE RATE
HEATING SYSTEM NOISES
HOME BUYERS GUIDE TO OIL TANKS
NOISE CONTROL for HEATING SYSTEMS
NOISES COMING FROM WATER HEATER
ODORS GASES SMELLS, DIAGNOSIS & CURE
ODORS FROM HEATING SYSTEMS
OIL FILTERS on HEATING EQUIPMENT
OIL FUEL TYPES & CHARACTERISTICS
OIL FILL PIPE LEAKS
OIL SPILL CLEANUP / PREVENTION
SOOT on OIL FIRED HEATING EQUIPMENT
STAIN DIAGNOSIS on BUILDING INTERIORS
THERMAL TRACKING & HEAT LOSS
VIDEO GUIDES: HEATING SYSTEMS
VIDEO GUIDES - InspectAPedia.com
WINTERIZE A BUILDING
A checklist for visual inspection of oil storage tanks. This heating oil storage tank inspection checklist was provided by an experienced oil heat distributor who also offers oil heat service and other plumbing services in New York's Hudson Valley area. Oil companies who sell and deliver oil to commercial and private residential oil storage tanks issue warnings to their clients about possible oil tank leakage and offer some advice. This information is quoted from an information sheet and "checklist" provided by a New York heating oil contractor.
Green links show where you are. © Copyright 2014 InspectApedia.com, All Rights Reserved.
Oil company service employees are using this checklist to perform a field check of residential heating oil tanks. The item(s) which the inspector feels are pertinent to the homeowner are simply circled, and the sheet is provided (in carbon copy form) to the homeowner.
[Your attention is directed to item 5, in particular. It is possible that the chief function of this "inspection" is to attempt to reduce the liability of the oil company for future spills.
[Click to enlarge any image]
Note that at one installation, where two new oil tanks were installed and where there are no leaks, item 1 of the form below had *not* been marked.] Also see Visual Inspection of Above Ground Residential Heating Oil Storage Tanks - ASTs for photos and details of visibly detectable oil tank defects.
"In an effort to better serve our customers, we are telling you about the New York State Department of Environmental Law.
You, the customer, are legally responsible for your oil tank and connections.
An oil spill occurring because of an old and rotted tank, fill or vent pipes, could cause you a good deal of aggravation and possibly a great deal of money for a clean up.
Starting this year [ca 1995 or earlier-DJF.], in the course of our cleanings, we will inspect your fuel tank (for tanks which can be seen and gotten to) for any telltale signs of deterioration, and make our recommendation to you.
We highly suggest that you follow our recommendations!"
1. __ At this time the tank appears solid and leak free
2. __ Tank solid but showing signs of rust
3. __ Tank has extended rust and should be replaced
4. __ Tank is very rusted & pitted, metal getting thin. Should be replaced as soon as possible.
5.__ Tank is over 18 years, recommend replacement
6. __ You have an in ground tank between 10 and 18 years old, tank should be pressure tested. [Note: DJF disagrees. If you're going to test a tank, a soil test, which costs about the same as a pressure test, will be more definitive. A tank could have leaked previously, had piping repairs, and a leak could go undetected by pressure testing]
7. __ Your in ground tank has water in it. Tank should be pressure tested to find out why.
8. __ You have an in ground oil tank more than 18 years. Tank should be replaced with either an in ground fiberglass tank or a 275 gallon in house tank.
9. __ Pipe joint compound on fill or vent pipes dried out. Piping should be ���reworked.
10. __ Needs fill cap(s)
11. __ Fill piping pitched wrong way
12. __ Vent piping pitched wrong way
13. __ Vent too small
14. __ Vent plugged or improper venting
I _____________ have inspected the oil tank at this house and recommend the following
Age of tanks unknown __________________________________________
I __________________________(homeowner name) residing at __________________
have read the above tank inspection report. The mechanic has explained his findings to me and made his recommendations to me.
Tank size_________________� Date____________
(Thanks to Bob Juliano of Juliano Heating & Plumbing, Poughkeepsie, NY whose form is quoted.)
Continue reading at OIL TANK INSPECTION REPORT TEXTor select a topic from the More Reading links shown below.
Suggested citation for this web page
Green link shows where you are in this article series.
Frequently Asked Questions (FAQs)
No FAQs have been posted for this page. Try the search box below or CONTACT US by email if you cannot find the answer you need at InspectApedia.
Use the "Click to Show or Hide FAQs" link just above to see recently-posted questions, comments, replies, try the search box just below, or if you prefer, post a question or comment in the Comments box below and we will respond promptly.
Search the InspectApedia website
HTML Comment Box is loading comments...
Technical Reviewers & References