Question? Just ask us!
Free Encyclopedia of Building & Environmental Inspection, Testing, Diagnosis, Repair
InspectAPedia ® Home
OIL STORAGE TANKS - home
ABANDONING OIL TANKS
ABOVE GROUND OIL TANK (AST) GUIDE
BURIED OIL TANK (UST) GUIDE
HEATING OIL TYPES & PROPERTIES - home
HOME BUYERS GUIDE TO OIL TANKS
OIL SPILL CLEANUP / PREVENTION
OIL TANK ABANDONING PROCEDURE
OIL TANK INSPECTION & TROUBLESHOOTING
OIL TANK LEAKS & SMELLS
OIL TANK PIPING & PIPING DEFECTS
OIL TANK REGULATIONS
OIL TANK REMOVAL COs
OIL TANK SPILL CLEANUP / PREVENTION
OIL TANK LEAK TEST METHODS
OIL TANK TESTING & REMOVAL COs
OIL TANK WATER CONTAMINATION
This article discusses inspection of oil tank support and piers.
The photo above shows an oil tank supporting leg (commonly made of iron pipe) that has been so exposed to flooding that it is badly rusted and about to split and collapse. If the pier or foot supporting an oil tank collapses, tips or slips and the oil tank falls over, a costly oil leak as well as possible damage from loss of heat to the building could be the result.
This is a section of our article on inspecting above ground oil tanks for defects. The article and photographs below give advice and example photos for the visual inspection of above ground oil tanks for leaks and damage including damaged or leaky oil storage tanks, improper oil tank piping, valves, and indoor-type oil tanks located outdoors. Page top photo is courtesy Arlene Puentes.
Green links show where you are. © Copyright 2015 InspectApedia.com, All Rights Reserved.
OIL TANK SUPPORT and Oil Tank Protection Inspection
Here are a some important indicators of tank condition that any home owner or home inspector can examine when an oil storage tank is visible and accessible inside or at a building.
[Click to enlarge any image]
Are the tank support legs sound and on firm footing? If required by local ordnance, is other tank support in place?
A standard 275-gallon tank with an average capacity of 260 gallons weighs about 2000 lbs. Placed on wood or dirt the tank is likely to tip and spill.
The photo shows a seriously tipping oil tank support pier, risking tipping of the tank, oil spillage, loss of heat (risking frozen pipes and water or mold damage) and environmental contamination.
Photo courtesy Arlene Puentes, Kingston NY
What about rusty oil tank feet? The rust shown in this photo is trivial in that it has not caused enough damage that we have any concern that the tank is going to tip over - at least not in the near future.
But rust on oil tank supporting feet for an indoor oil storage tank, especially on those back feet close to the wall, hard to reach, and hard to re-paint, are a great indicator of the history of water entry in a building.
What about just skipping oil tank feet entirely. Why can't we just sit the oil tank on the ground?
Steve Vermilye (photo at left) looked concerned for a reason. This oil storage tank had not much besides luck holding it up, and in addition, the tank was not designed for ground-contact.
This oil tank installation is inviting rust perforation of the oil tank or a tipped-over oil tank spill and loss of heat all at once.
Oil Tank Protection From Vehicles or from Tipping-over
Regardless of whether an oil tank is installed indoors or outdoors above ground, it must be properly supported. Some municipalities also require installation of special protection to assure that a tank cannot tip over, even if its feet are damaged.
A steel pipe may be installed in the floor next to the tank and extended vertically above the tank and then after making a 90 deg. bend, secured to the wall to "cage" the oil tank.
Our photo (left) shows steel piping installed to protect an outdoor oil tank from tipping over.
Where oil tanks are installed in garages, some jurisdictions require that the garage oil tank (and boiler or furnace if one is present) also be protected from being struck by a vehicle using similar iron pipe guards as just cited above.
Also see additional visibly detectable oil tank defects listed at Home Inspection Report Language Library: Visible Defects in Oil Tank Installations, Tanks, and Heating Oil Piping.
Reader comment: NFPA & Other Standards: requirements for support and anchoring of oil tanks
2 Feb 2015 NHFireBear said:
Thanks NHFireBear - we've added your note. Working together makes us smarter. - Ed.
Continue reading at OIL TANK INSPECTION & TROUBLESHOOTING or select a topic from the More Reading links shown below.
Suggested citation for this web page
Green link shows where you are in this article series.
Frequently Asked Questions (FAQs)
No FAQs have been posted for this page. Try the search box below or CONTACT US by email if you cannot find the answer you need at InspectApedia.
Use the "Click to Show or Hide FAQs" link just above to see recently-posted questions, comments, replies, try the search box just below, or if you prefer, post a question or comment in the Comments box below and we will respond promptly.
Search the InspectApedia website
HTML Comment Box is loading comments...
Technical Reviewers & References